Textile Coal Steam Fire Tube Boiler Price
How to provide textile coal steam fire tube boiler price thermal efficiency thermal efficiency of the steam boiler has the following methods: low-pressure boiler at the factory has been designed considering the problem of thermal efficiency of the boiler, the flue gas from the device or change little aspects of energy-saving possibilities, it is best to start from the energy-saving operation (here talk recovered water vapor condensation method). The current design thermal efficiency of domestic low-pressure boiler is generally 70 to 90%, generally the actual operation of the thermal efficiency of about 60 to 80%, some even below 50%, a small low pressure industry as long as the operation, maintenance properly, can meet the design thermal efficiency of manufacturers. I think the management and operation should pay attention to the following points: First, the boiler flue gas temperature monitoring. Typically the maximum exhaust heat loss is loss, it is important to good control of exhaust gas temperature, exhaust gas temperature is generally low pressure coal-fired boiler of 150 ~ 180 ℃, fuel boiler exhaust gas temperature is 210 ~ 240 ℃, so when the boiler to find out why when the exhaust temperature is too high and promptly eliminated. Coal-fired boiler flue gas temperature is too high reasons are: high furnace pressure; shorting smoke; thick soot on the heat pipe; thick scale pot like. High temperature fuel exhaust reasons are: 1 air not adjusted oil, the oil is not completely burned in the chimney the secondary combustion occurs aft; 2 soot too, the need for timely cleaning; 3 shorting smoke; 4.... thick scale; Second, controlling blowdown rate. Without restricting the general rate of industrial sewage control in 5 to 10%, in the pot of water to ensure that qualified (mainly total alkalinity and pH value), the blowdown rate as low as possible, the sewage to adhere to the "ground row, row less, are ranked "the rules. Third, the maintenance of good furnace wall insulation. The heat loss is also a relatively large heat losses, now the manufacturers in the manufacturing and design has been well thought out, so we do not need to change, we just trying to be difficult to maintain. Outer surface temperature generally does not exceed 50 ℃, it will have to find out the reasons such as too high, and remove. Boiler insulation should always be kept dry, for coal, not a long positive run, or easy to damage the coal furnace wall and gate and so on. Fourth, adjust the ratio of fuel and air volume, complete combustion of the fuel as possible. Generally do not have a small amount of wind testing instruments, we can only go by experience adjustment. For oil, the normal combustion flame was yellow-white, non-glare, flame stability, no visible smoke chimney; For coal, the normal combustion flame pale, no visible smoke chimney, basic cinder burn coal particles as even as possible. Fifth, the need for a sound water treatment. Improve water treatment and water quality testing can maximize prevent fouling and correct guidance of the sewage, but it did not do a lot of small, companies usually do not pay attention.
Shandong Zhaoyuan Mining Group Co., Ltd. is a large state-owned local asset management companies, gold mining dressing and smelting for leading industries, operates in the area of tourism, services, precious metals, real estate, eco-agriculture, with total assets of 10.2 billion yuan, Shanghai gold Exchange is an international provider of standard gold bullion. July 2017, Shandong Mining Group and fast textile coal steam fire tube boiler price steam signed a 0.5-ton electric heating steam boiler which mainly produce steam for metallurgical mineral processing and other manufacturing processes, energy defeating small, strong ability to supply steam .
Henan combustion control and adjust fast textile coal steam fire tube boiler price boiler company to introduce small series with the boiler combustion control and adjustment. 1 steam boiler combustion process is the basis of all the work process of the boiler, from the safe operation of the economy, environmental protection point of view, how to properly regulate the burning furnace, saving coal consumption is the responsibility of each fireman. 2 hot water boiler combustion conditions primarily by uniformly supplying the fuel, and air distribution adjusting reasonable combustion equipment is achieved, the coordination of the three, to ensure stable combustion conditions, economy, safety. When coal and boiler load changes, will need to adjust the amount of coal feed and the amount of the wind, in order to obtain a normal combustion conditions. Indicator 3.1 normal combustion conditions 4.8.3 normal combustion means: timely fire burning strong, ash burnout. Specific requirements:. A fuel inlet from the anterior arch 0.1-0.15 m fire, gray ash ex chain at the 0.3-0.4 m burnout. B. fire bed smooth, dense and uniform flame, without flame or blown partial blackening phenomenon. C. Flame intermediate white light, two dark, the fire grate bed length representing more than 3/4 of the effective length. D. pale gray smoke or nearly colorless. In order to achieve good combustion conditions, must maintain a high furnace temperature, the temperature of the upper layer is generally burner combustion layer preferably 1100-1300 deg.] C, may be determined according to the color of the flame. Furnace temperature and flame color relationship in the following table. The outlet temperature of the furnace can also be used to determine, 29MW boiler design furnace outlet temperature of 1017 ℃, 58MW of 998 ℃. 3.3 In the case of normal combustion, the oxygen content in the flue gas is constant, the oximeter, fireman can understand the situation of excess air in the furnace, the furnace excess air is generally mechanical 1.2-1.4%, of excess air and oxygen table below. Ash 3.4 combustibles content is an important sign of good and bad conditions of the boiler combustion, which fuel, combustion equipment, and operations are closely linked, general mechanical furnace ash carbon content should be less than 10%. 3.5 water boiler operation should ensure that in the case of no condensation of the tail to minimize exhaust gas temperature, exhaust gas temperature is controlled at 110-160 ℃. Adjusting and controlling the amount of coal to a fireman who adapt to changes in load, the supply must be based on different types of coal and the various stages of the heating season, the weather trend, the thickness of the seam is determined, the general control of the thickness of 80-100mm low load, medium load control in 100-120mm, high load control in 120-160mm. 2 fireman in specifying a seam thickness, to be due to the furnace, because coal should comprehensive analysis, on balance, for the ash content, water large, large particles, high ash melting point of the coal, generally the appropriate tone thick seam, opposite seam is to tune thin. Small particles of coal or pulverized coal and a low ash melting point of the plurality coal i.e. strong bonding to a thin coal seam. Generally the 3 or the boiler when the load change is not too large, the method should not be used to adjust the thickness of the seam. Because coal seam thickness adjustment can not be effective immediately adjust the load only when a large load changes, and long-term stable operation of the boiler in the new load considering regulating coal seam thickness. 4 seam thickness can be achieved by adjusting the height of the coal and layered coal hopper shutter speed of the drum. Shutter elevation coal, coal may be added into the same hierarchical improved coal hopper drum speed may be increased into the amount of coal seam in order to obtain a proper height, the height of the shutter must coal, coal hopper drum speed stratified and chain speed adjustment of the three. Given the limited level editor, inevitable errors and inadequacies, please correct me! Henan fast Boiler Company is committed to a wide variety of gas-fired boiler, steam boiler manufacturing, product quality, reasonable prices and widespread customer industry praise, if you have any needs, please contact us!
6 tons gas steam textile coal steam fire tube boiler price steam pressure adjusting a boiler operation, must frequently monitor the pressure gauge indicated. To maintain stable steam pressure, boiler pressure must not exceed the design pressure. Second, increasing boiler load: Steam pressure decreased boiler load is increased, if the level is high at this time, the amount of water should be reduced to a water supply or suspend, the amount of coal and increase the air volume. Gradually increase the amount of water at the same time to strengthen the burning, keep the steam pressure and the water level is normal. Third, the boiler load reduction: the vapor pressure rises to reduce boiler load, if the level is high at this time, the amount of coal should be reduced and the air volume, reduced combustion. Then the appropriate water reduction or suspension of water supply to the water vapor pressure and stability in the nominal range. Then press the normal combustion and the amount of feed water 8 to adjust. If the actual water level within the boiler is low, to increase the amount of water should, until the water level returns to normal after the combustion and needs to be adjusted according to the water vapor pressure and load changes.