factory directly horizontal oil steam boiler
The szs series and wns series of oil and gas boilers produced by ZG boiler are the most widely used. In a big way, it can be widely used in heating, industrial steam and hot water supply, and the company has its own power station. Such as school heating, hotel bath hot water supply, food factory industrial steam supply. These two oil and gas boilers are all fast-assembling boilers with low capital investment and high degree of automation. Customers can choose according to their needs.
Combustion gas treatment unit and a fault, gas boiler burner ignition misfire rod reasons: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Measures following five: Clear, renewal, adjust the distance, change and switching transformer. Second, gas boiler, but spark ignition rods misfire reasons: 1, the cyclone disc space ventilation is blocked carbon, poor ventilation. 2, dirty oil nozzle clogging or wear. 3, the throttle angle is set too small. 4, the firing bar from the leading edge from the oil nozzle tip inappropriate (too protruding or retracted) 5, the first solenoid valve is an oil debris blocking gun (gun small kerosene). 6, oily or too viscous to flow easily clogged or the oil filtration system the valve is not opened, so that insufficient suction pump, oil pressure. 7, the filter pump itself blocked. 8, the oil more water (boiling abnormal noise within the heater). Measures are: Clear; first wash, such as not renewed; turndown test; adjusting the distance (in 3 ~ 4mm as well); Remove cleaning (cleaning the parts diesel); Check tubing and oil filters, insulation equipment ; remove peripheral screw pump, carefully remove the cover inside out oil network, with immersion oil; renewal of the test oil. Third, when the gas boiler and turn the fire a small fire normal, off, or flashing instability reasons: 1, the air volume damper setting fire too. 2, oil fires micro switch valve (damper outermost that group) inappropriate setting (set throttle air flow rate is greater than the fire). 3, oleaginous easy to spray viscosity is too high (heavy). 4, and the nozzle plate spacing cyclone inappropriate. 5, fire nozzle worn or dirty. 6, the preliminary fuel tank temperature is too high, so that the steam not smooth oil pump oil feed. 7, fuel oil boiler water. Action: Test gradually reduced; heating temperature; adjusting the distance (between 0 ~ 10mm); clean or replace; approximately set to about 50 deg.] C; or drain oil change. Fourth, the noise increases gas boiler burner reasons: 1, cut-off valve is closed or the passage into the fuel shortage, an oil filter blockage. 2, the oil inlet temperature is low, the oil viscosity is too high or the temperature is too high the pump inlet. 3, oil pump failure. 4, fan motor bearing damage. 5, dirty fan impeller. Processing methods: ① the oil line check valve is open, if the oil filter is working properly, the filter cleaning pump itself. ② heating oil or reduce the oil temperature. ③ Replace the oil pump. ④ replace motor or bearings. ⑤ cleaning fan wheel.
The essay serve a documented basis for joint project of erection and operation of biomass residue firing CHP (Combined Heat and Power) unit. 58 tons/hour of steam at 12 barg are generated in few heavy oil firing boilers and consumed in production process. The basic assumptions are that saw dust or/and wooden chips with LHV (Low Heating Value) 18,000 kJ/kg will be fired in a fluidized bed boiler producing about 30 ton/hour steam (about a half of needed process steam). The steam flow, passing through a back pressure turbine, will generate electricity corresponding to difference of enthalpies of fresh steam generated in the boiler and of one needed for process. From the turbine outlet the steam will be used, as today, for the technological process of the factory.
The use of central heating hot water boiler is the best choice for winter heating in northern China. Shanxi Province is located in Chang Darrow Heating Co., Ltd. mainly provides heating and post-service maintenance of heating equipment, heating clients involved in enterprises and institutions, office buildings, residential housing and a variety of commercial and other entertainment venues. With the wide blue sky covered Battle of the project, China's gradual increase in the proportion of heating for cleaning, heating, Ltd. Dalong Chang respond positively to the call of national policy, high pollution intensity wishing previously used, low thermal efficiency of coal-fired boiler to replace the traditional use hot water boiler clean fuel. After comparing many boiler manufacturers, choosing the optimal selection, determined and professional cooperation parties do fast boiler fuel boiler cleaning equipment. Providing a fast side 35 MW gas tube hot water boiler (SZS35-1.6-Y.Q) according to their actual needs.