steam boiler in thailand
4. Steam boiler working pressure
Rated working pressure on the nameplate of steam boiler should be greater than the sum of steam piping resistance and production need working pressure. Please do not ignore the steam pipe resistance, because the rated steam pressure higher, the saturated steam temperature will be also higher.
superheated steam heating Many boiler saturated steam heating. When using saturated steam heat, you need to set traps along the steam pipes. Traps because of the quality and regulation management issues, a large amount of leakage of steam, causing a great waste of energy. We take reconstruction measures will increase the steam boiler in thailand superheater, saturated steam superheater 20%. To use before the steam heating equipment for the micro superheated steam. Thereby eliminating the trap along the way, to eliminate the hydrophobic and run steam brings heat loss. This is closely related to the size of the heat loss and management level of the factory. Well managed, only hydrophobic heat loss, poor management, there are a lot of running steam losses. This loss is typically several percentage points.
(1) Low NOx combustion technology, which controls the combustion process in the generation of nitrogen oxides, mainly for large coal-fired boilers; low NOX combustion technology can reduce 30 ~ 50% NOX emission values, to further reduce NOX in emissions, flue gas denitrification technology must be used.
After use throughout the winter, the Central Conservatory of Music give us feedback, six V6-99 fully meet the heating needs of the school. And boiler fuel and water requirements are not high, urban water and low-pressure natural gas combustion can operate. The most important point is that nitrogen oxide emissions are very low and very happy to recommend it to others to do the brother of boiler units. --customer feedback