Rajasthan Industrial Coal Fired Steam Boiler Manufacturer
Main rajasthan industrial coal fired steam boiler manufacturer temperature abnormal phenomenon of how to do 1, main steam temperature anomalies alarm. 2, the rapid variation of the main steam temperature, a secondary damper frequently significantly reducing water operation. 3, starting superheat outlet steam separator above or below normal. 4, if the steam with water, the unit will water shock occurs. 1 reason, the fuel and water supply imbalance, the separator outlet temperature abnormality. 2, coal combustion conditions change or affect, such as excessive load lift; and pulverizing mill administration system abnormality stop; means automatically increase or decrease the failure rate is too large amount of wind and the like. 3, the central flame furnace changes, such as the bottom seal damage, W and inadequate flame downstroke. 4, the control failure by warm water, warm water flow rate reduction is abnormally reduced or increased. 5, feedwater temperature mutation. 6, does not match the wind coal. 7, the secondary combustion heating surface. 8, furnace coking or fouling seriously. 9, heating surface leakage squib. 10, flue gas damper opening degree is not normal. 11, coal sudden change occurred. 12, the uniformity of the powder feeding substantial change occurs. 1 process, failure caused by unit coordinated coal - water ratio should be immediately released coordinate offset, in accordance with the current load demand, with reference to the start of the steam superheat separator, and adjusting the amount of fuel corresponding to the amount of water, with one, two main desuperheating water rapidly steam temperature control in a normal range; when the coal - water ratio should avoid imbalance after coal and water while adjusting; when coal - water ratio is adjusted to further adjust the load after a relatively stable; contact maintenance processing timely. 2, when the water supply system fault condition occurs a significant disturbance furnace should pay attention and automatically coordinated working conditions, so as not to manual intervention, when not working properly coordinated and automated, should be manually adjusted, stable water flow, referring to separation according to the water flow steam superheat, the adjusted amount of fuel, with a secondary spray water rapidly controlling the main steam temperature within the normal range; contact maintenance processing timely. 3, due to rapid changes in load caused by the load change rate should be adjusted; load change caused due to protective operation or the like caused by heat load to be quickly adjusted to maintain the boiler pressure of the main steam stability. 4, by warm water automatic dysregulation, should be appropriate Save warm tone is switched to the manual may be an intermediate point of the feedwater control system be corrected for temperature if necessary, or the feedwater to switch control to manual control, due to lower lifting and lowering the load speed to prevent steam temperature, promptly contact a service process. 5, the boiler furnace cause severe fouling and coking of the main steam temperature anomalies can be corrected by an appropriate degree of superheat outlet steam separator start, adjust, and in a timely manner and the furnace heating surface sootblowing. When the platen superheater sootblowing or superheater outlet temperature is still above normal and a secondary reducing water damper fully open, to check the furnace and the combustion air distribution system is normal, the checking process to reduce still overtemperature unit load. 6, flue gas damper adjusted to an appropriate opening degree. 7, if the bottom seal after losing back to normal immediately. 8, to strengthen the turbine expansion, differential expansion, axial displacement of the shaft vibration and bearing temperature monitoring, if abnormal, the process according to the corresponding regulations. 9, after the above measures, if invalid, should immediately drop the load process. 10, in front of the main steam temperature main steam 50 ℃ drastically reduced within 10 minutes, should an emergency stop.
6 tons adjusting a combustion gas rajasthan industrial coal fired steam boiler manufacturer, normal combustion boiler three basic aspects of indicators include a uniform supply of the fuel, reasonable ventilation, adjustment the combustion. 1, to maintain the high temperature of the combustion chamber temperature of the upper layer is preferably in the 1100 ~ 1300 ℃, flame orange in color. Flame reddish color indicates that the amount is not enough to the wind, the color white indicates that excessive wind. It should be appropriately adjusted. 2, fuel ash to reduce ash content in the combustibles to be below 10%. 3, reducing the temperature of the boiler flue gas exhaust gas temperature should be controlled below 200 ℃. 4, holding furnace negative excess air boiler is 1.2 to 1.4, by adjusting the balance of the blowers to maintain the furnace pressure is -20 ~ -30Pa. 5, the thermal efficiency of the boiler to improve the thermal efficiency of the boiler should be kept above 60%. II. Combustion Adjustment 1, the amount of fuel to air required for combustion and the amount of a reasonable distribution. Ventilation should first increase the amount of fuel increases, it should first reduce the amount of fuel supply reduced ventilation. 2, the thickness of the seam and seam thickness configuration grate speed is 80 ~ 120mm grate speed at high, middle and low profile configuration of several commonly used methods:. 9a rapid combustion of thin seam b c thick seam in low combustion. 3 thick seam combustion speed, the segment with the wind blowing principle: burn promoting intermediate ends. That is, after the coal into the coal starts to warm up the shutter, fire line front arch, the primary combustion zone, the middle grate to burn the rear grate zone. Normal combustion conditions are: fuel from the coal at the beginning of the fire shutter 300mm, uniform flames, the fire bed formation, at the end of combustion from the end of the grate 300 ~ 500mm. 4. maintain proper furnace temperature to avoid coking. The fire bed to maintain the homogeneous combustion, to avoid burning fire bed obliquely. 6. The residence time of the fuel on the grate in less than 30 minutes.
Electric boiler with traditional coal boilers What are the advantages compared to? 1, environmental protection, health, the family does not appear the phenomenon of soot wander around the string, there will not be a black cinder material made everywhere. 2, and effort. L do not get up early every day fire, dig boilers, transport cinder, as long as you can plug in the power, if you want power, you can lower the temperature at night several. 3, security. In order to ensure the traditional boiler room, especially in northern areas, full, so there is often a phenomenon soot poisoning occurred at bedtime will certainly pressure of steam coal, and electric boilers do not worry about this, with leakage protection, water protection, ground fault protection, vapor overpressure protection, overcurrent protection, power protection, automatic protection boiler, antifouling functions. 4, electric boiler temperature can be provided, high precision. Want how high the temperature can be set.
Wuhan Port District Social Welfare Institute (apartments for the elderly) is invested by the government pension services, with a total construction area of 38,000 square meters, 532 beds, mainly adopt destitute persons, social support on behalf of the elderly. Hope to provide welfare to the elderly year-round 24-hour hot water, the original boiler equipment can not meet this demand, therefore, require additional purchase orphanage hot water boiler. After much investigation, in cooperation with the welfare determined fast boiler, provides three integrally condensing gas hot water boiler (WNS1.4-1.0 / 95/70-Y.Q) by a fast boiler.