energy saving atmospheric gas hot water boiler
4295, Henan reasons gas boiler chimney white smoke and some will Henan gas boiler chimney white smoke, some Henan gas boiler chimney does not smoke because of wet dust removal equipment used. Large water content of the flue gas. If the rear of the boiler flue temperature is too high, it will produce water vapor. Dry type cyclone. If the boiler air distribution adjustment is not the time. Excessive air excess factor. Short residence time in the furnace flue. The exhaust gas temperature is too high. Smoke density and air density difference is large. It may produce a visual image of white steam plume. The truth is like the summer heat flow on the same asphalt. Henan gas boiler includes a gas water boiler, gas energy saving atmospheric hot water boiler, gas steam boilers, gas hot water boiler which is also known as gas heating boilers and gas boilers bath, as the name suggests refers to the gas boiler fuel gas boiler, gas boilers and oil-fired boiler , compared to the most economical electric boiler, so most people have opted for a gas boiler as steam, heating, boiler equipment for bathing.
Our industry is a big country, provide power for industrial equipment giant multi-boiler. After investigation, the vast majority of our country's industrial boilers are in healthy condition, causing energy waste and pollution is very alarming. Moreover, the recent nationwide boiler accidents continue to occur, causing huge casualties and property losses, the adverse impact on society and the economy, how to effectively protect the safe operation of the boiler to be solved throughout the boiler industry event.
Vertical pressure steam boiler component damage cause an explosion in the explosion normal working pressure: the pressure receiving member defective or damaged vertical steam boiler, and gradually developed to a certain extent. There are heating and energy saving atmospheric hot water boiler bath for two purposes. Hot water boiler by circulating hot water circulation pump hot water holding tank, the tank hot water heating cycle can be achieved bath object; hot water boiler by circulating hot water circulation pump heating conduit, through the heat sink (radiator) people can achieve heating requirements; hot water boiler and hot water circulating pump with heat exchanger can be achieved bathing and heating dual function. Biomass boiler is a kind of boiler to biomass energy as a boiler fuel called biomass boilers, steam boilers into biomass, biomass hot water boiler, biomass stove, biomass thermal oil heaters, vertical raw biomass boilers, biomass boilers and other horizontal. The erosion of the steel sheet, equipment for manufacturing and testing of weld defects, vertical steam boiler accumulation of dirt poor heat transfer, rapid cooling apparatus taking water caused when vertical steam boiler water. Combustion furnace explosion: mainly vertical steam boiler explosion instantaneous deflagration of combustible gases in the furnace and the liquid concentration reaches a certain limit. Explosion in the furnace depends on the concentration and the heated mixed gas premise. Vertical steam boiler furnace if not cleared before starting or ignition failure is not required to operate, blind firing, furnace explosion is likely to occur. Operating pressure exceeds the design pressure: vertical steam boiler pressure gauge failure, the safety valve does not work after overpressure, boiler workers from work, supervision is not enough, the main steam valve is closed, the relief valve malfunction. Vertical steam boiler design is unreasonable, different manufacturing quality, the material does not meet the requirements, poor weld quality, maintenance is not timely, long downtime, resulting in corrosion vertical steam boiler, reducing the carrying capacity of the steam boiler explosion caused by overpressure.
You have to know the energy consumption of boiler problems (control measures exhaust gas temperature of the boiler) 1, operational measures (1) unit load changes, to adjust air flow and pulverizing system operation mode, keeping the excess air ratio most suitable furnace. (2) time to adjust the bottom seal tank inlet valve, suitable to ensure the seal tank water level. (3) changes in coal quality, timely adjustment of combustion, complete combustion and ensure proper furnace flame center. (4) heating surface periodic soot blowing and slag, maintaining heating surface clean. (5) maintaining a suitable gas velocity, the heated area ash reduced tail. (6) Check the class auxiliary burner throttle opening, to ensure there is sufficient oxygen in the combustion. (7) raise the water temperature. 2, boiler routine maintenance and testing (1) combustion optimization and adjustment tests, to determine the economic coal fineness different coal. (2) periodic testing coal fineness, abnormal timely adjustment process. (3) regular air preheater leakage test, and remove air preheater leakage. (4) Always check the furnace to see the fire hole, furnace wall, bottom seal, identify problems and timely closure, reducing boiler leakage. (5) Strengthen routine maintenance soot blowers to closely monitor motor current soot blowers, for soot blowers and often stuck in the barrel bending furnace and other defects timely treatment to ensure soot blowers investment rate above 95%. 3, repair, downtime (1) Check the burner damage, to replace or repair damaged nozzles, the nozzle and the bluff body. (2) heating surface, the flue fouling, slagging cleaning up. (3) adjusting the fuel to determine the secondary air and the opening degree position of the damper flap. (4) Health Check flue gas damper, the damper position adjusting checked. (5) roof sealing, see the fire hole, Manhole, bottom seal tank leakage inspection governance. (6) replacing air preheater wave plate, rinsing, the check processing sector plate, curved plate is deformed, and bearing wear off defects, defect inspection process automatic adjustment mechanism sealing gap. (7) Pulverizing System: Mill off the door, the hot air and the cool air shutter opening degree adjustment. Roller cover and bowl mill liner replacement, the spring biasing force and gap adjustment. Import a fan baffle opening adjustment. (8) the flue expansion joint leakage defect inspection process. (9) soot blowers and related equipment check process. 4, transformation (1) Burner deformation, wear process, replacement, and a bluff body concentrator ceramic sheet, and silicon carbide wear measures. (2) the heated area ash slagging comprehensive inspection process. (3) waterwall, economizer, reheater, superheater tube cutting test monitor segments corrosion and scaling inside the case. (4) boiler, air preheater Leakage leak plugging governance. (5) on the "four leak" taken by plugging repair. (6) backpass wear parts wear welding process and do. (7) heating surface (economizer, superheater, reheater) for transformation, reduce exhaust gas temperature. (8) to do a good job adjusting the air according to test results dynamic field. (9) boiler, the flue joints and other advanced seal plastic material, to reduce leakage.