Diesel or Natural Gas Fired Industrial Steam Boiler
The beverage plant needs steam in its beverage degassing ,sterilization, and packaging process. 3 ton steam requirement per hour came from beverage plant steam requirements in all process. Then, why there must be WNS series, any other choice here? WNS series steam capacity is from 2 ton to 10 ton, more suitable for lower capacity diesel or fired industrial steam boiler. Of course, we also have SZS series which capacity is from 4 ton to 30 ton. To larger steam requirements, industrial gas oil fired power plant boiler is also available. If you want to use other gas fuels like lpg gas, bio-gas or liquid fuels like diesel oil, heavy oil, light oil, our WNS series steam boiler also can burn them. But, like our advanced engineer said before, each boiler is specialized for one designated fuel, this WNS series 3 ton steam boiler is manufactured to burn natural gas. Although it can burn other fuels, it can reach highest thermal efficiency when burning designated fuel natural gas.
Now we have many types diesel or fired industrial steam boiler for chili sauce factory, there are gas fired steam boiler, oil fired steam boiler, coal fired steam boiler, biomass fired steam boiler, solid fuel steam boiler, straw steam boiler. The chili sauce plant can choose the suitable steam boiler according to the fuel cost in the local.
The reason the gas boiler burner noise analysis increases in the use of gas-fired boiler, found a small fire is normal, but when it becomes a fire goes out or flashing instability. First, because of excessive wind fire damper is provided; secondly, because of the fire valve microswitch (outermost damper group) is set incorrectly (fire damper is set larger than the amount of wind). Fuel circuit closing valve or port into the oil shortage, an oil filter plugging, increased gas burner boiler noise; Alternatively, since the oil inlet temperature is low, the viscosity is too high, the oil feed pump temperature, pump failure, fan motor bearing damage, and because the fan impeller dirty equipment, resulting in noisy equipment. Gas boiler in the course of the above failures, the viscosity is too high to spray the oil (heavy oil), and improper nozzle plate from the cyclone, and the like due to worn or dirty nozzles plus reasons. May be due to too high a heating temperature of the tank, leading to the steam delivery oil pump is not smooth; or because the fuel oil boiler caused by the water content. In use the gas boiler, the above failures should be gradually reduced, the heating temperature, to adjust the distance (0 ~ 10mm), cleaning or replacement should be about 50 ℃, the heating temperature should be raised. Oil change or drainage.
Recently, the district government Qingyang City, Gansu Province, deputy head of Xifeng Wang Chao organized a remediation coal-fired boilers will promote the work. By the township (street), the head of district straight relevant departments attended the meeting.
Written meeting issued atmospheric district office "notice Leading Group Office of Air Pollution Prevention
Wang Chao requires that all relevant units must concentrate efforts to promote coal-fired boiler renovation, remediation to the control list, in strict accordance with the "three three must" requirements, to promote catch, this area, this system is not in place of coal industry regulation boiler immediately carry out concentration and control, to ensure that the work complete, fully put in place. To collaborate actively cooperate with the township (street) mainly clear time limit for rectification and reform measures, solid progress. To strictly control inventory and remediation remediation standards of accountability and strengthen supervision of the ideological hesitation wait and see, action is delayed, focus on promoting renovation is not complete unit, accountability seriously investigated.