combined oil fired condensing hot water boiler supplier
Gas boiler burner failure how to do? Fault gas burning boiler opportunity arise, the most frequently occurring burner ignition rods gas boiler is not firing. The reason is concerned, it is because the ignition rods gap sandwiched carbon residue, oil phenomenon appeared, followed, that is because ignition rods chipping, moisture or leakage, furthermore, to stick ignition misfire, is because the distance between the ignition does not stick, too long or too short. Gas boiler burner ignition misfire rod, there may occur ignition due to the damage the insulation coating rod, ground short circuit; Then, since the ignition cable is transformer failure, including cable disconnection, connector damage caused by ignition when a short circuit; transformer disconnection or other failure occurs. When it comes to measures to deal with it is, it will include clearing, as well as new ones to adjust their distance, lane changing and changing transformers. Further, when we are faced with the ignition rod on the gas boiler burner spark reasons but misfiring, because the cyclone disc ventilation gap is blocked by carbon deposits, resulting in poor ventilation, or because the oil nozzle is dirty, clogged or is worn, it is because there is relatively small throttle angle setting. Gas boiler ignition spark rod misfiring but also may be due inappropriate firing rod tip from the leading edge of the oil from the nozzle (or protrude too retracted), moreover, the gun is because the first solenoid a valve clogging debris (small kerosene gun); if too viscous oily or not easily flow filtration system or re-clogging of the oil valve is not open, that the pump inlet is insufficient, low oil pressure. Finally, there is a spark ignition rods but misfire, because the pump itself or filter blockage in the oil because of its more water (boiling abnormal noise within the heater). For gas-fired boiler ignition spark stick but misfire, we must first be clear; the next, which is to be cleaned, such as not enough time to pay attention to new ones; furthermore, also is to pay attention to transfer a small test before they can .
How to maintain steam boiler 1, when maintaining boiler, must cut off the power supply, must release pressure. 2, burners should be removed from boiler body every two months, and other foreign bodies such as carbon deposit and dust should be removed seriously. The photo-electric tube is polished once a month. The fuel filter should always be cleaned and filtered. Carefully clean the inner filter screen of the oil pump and do not destroy the gasket. The burner shall not run without oil to prevent damage to the oil pump. 3, the water level gauge shall be kept clean at all times and rinsed once a day by opening the cleaning valve to ensure the water level is clear. 4. The safety valve shall be pulled once a day in case of rust failure. 5, When the steam boiler stops running for a long time The power supply should be cut off and the maintenance work should be done: (1) dry maintenance, discharging the furnace water after the furnace is stopped, rinsing away the dirt in the furnace, drying the pot with a small burner fire (the burning time should not be too long, so as not to damage the boiler), Then, after all the boiler gas has been discharged, all pipe valves will be closed and checked every three months. (2), wet maintenance shall be applied to boilers with a period not exceeding one month, and the boiler water will be discharged after the shutdown, and the clean and full water will be discharged. Cut off the power supply and close the valve.
Car accessories types of complex processing, such as the interior wall Peng, floor, seats, instrument panels, sound systems, many processes required in a high temperature environment, the temperature becomes optional metrics wind Visteon combined fired condensing hot water boiler supplier. It is reported that Dongfeng Visteon existing boiler equipment can not reach the growing production needs, the introduction of fast boiler production of two parties often piezoelectric hot water boiler (CWDR1.8-95 / 70-II) in 2017.
The oil gas power plant boiler has low NOx emissions in the flue gases. In the combustion zone of the boiler, the membrane wall is spiral wound, utilizing smooth-bore tubing. This inclined-tube arrangement reduces the number of parallel paths compared with a vertical-wall arrangement and therefore increases the mass flow of steam/water mixture through each smooth-bore tube. The development and realization of high efficiency methods for burning the oil and gas fuel in our power plant boilers make it possible to save fuel and reduce the emission of harmful substances while meeting rigorous safety requirements.