coal fired boiler water tube san fernando la union
Recently, Binzhou City, Shandong Province High-tech District Supervisor Bureau to carry out special rectification actions coal fired boiler water tube san fernando la unions within the region, mainly to effectively prevent and resolutely curb special equipment accidents from happening again, strengthen security principal responsibility.
Inspectors use of "without warning, went straight to the scene" way of checking for nine boiler units within the region conducted a comprehensive inspection, focusing on aspects of boiler operation, the operator of personal responsibility, troubleshooting, safety test accessories, etc. a comprehensive investigation. Long-term idle boiler, supervise the use of units in time for deactivation procedures; management is not in place, there are security risks of the use of units, ordered deadline to complete the hidden rectification. The campaigns, check out a total of more than 30 people, to identify risks at 8, at the completion of the rectification 8.
Next, Binzhou City High-tech Zone Market Authority will continue to strengthen law enforcement and inspection efforts, compacted layers of responsibility, and strengthen security consciousness, special equipment to protect the region's security situation continues to stabilize, escort for the economic development of high-tech zones.
58MW SZS series gas-fired hot water coal fired boiler water tube san fernando la union project for heating industryPeople cannot live a comfortable life without heating boilers in the winter, the normal and stable heat source is of great importance to human life. What is following is the increasingly serious problem of environmental pollution, implementing the policy of “coal to gas” is no time to delay, using gas-fired hot water boilers has been the general trend. Tianjin Jizhuangzi heat supply center is an enterprise specializing in city heat supply. In order to realize the “green heating”, the heat supply center decided to introduce a branch of gas-fired boilers to replace the old coal-fired boilers. ZOZEN successfully won the trust of Jizhuangzi heat supply center with its own strong comprehensive strength and rich experience in the heating industry. JIzhuangzi chose to cooperated with ZOZEN and ordered 3 sets of 58MW gas-fired hot water boilers (SZS58-1.6/130/70-Q) to provide heating source for citizens. This series of boilers adopts the design of " D " type membrane wall structure, the steam drum, the water drum and convection tube bundle form the convection heating surface to ensure the the boiler expands on both ends as a whole; at the same time, the combustion chamber is designed with the narrow distance tube membrane water cooling wall to reduce heat lost, in addition, the boiler is equipped with a big combustion chamber for the full combustion of fuel, effectively increasing the boiler thermal efficiency over 98% and reducing the NOx to 30mg, which are superior to the national level one energy efficiency standard.
Note the choice of industrial coal fired boiler water tube san fernando la unions from the first industrial revolution to develop microbial technology, and upgrading various products continue to emerge, led us to the development of human civilization from the original backward to technological civilization, to the boiler, for example, since the last century, there has been a cylinder since the boiler-shaped, with the needs of science and technology and production, from simple to complex, from single to serialization, boiler technology are developing rapidly, the good reputation of industrial boilers companies choose to share precautions industrial boilers; first, the coal use; the design of the cell structure based on coal boiler components as the design basis, select the boiler should pay attention to adjust to the type of coal in the region. It recommended new, high-efficiency, high-tech, high-quality, durable industrial boilers; second, parameter selection; industrial efficiency boiler work normally when approaching the highest efficiency rating, as the load decreases efficiency has declined. Boiler capacity is generally selected: it generates a large steam than the actual gas consumption, such as the required parameters and actual parameters difficult to match industrial boilers, high boilers in this case a gear selection parameter. Selection of auxiliary boiler should also refer to the above principles, to avoid the "big horse car"; third, the number of choices; normal maintenance of industrial boilers and boiler shutdown is a number of factors, but also pay attention to: the boiler room shall not exceed the number of boiler economizers work load, install boiler economizer device purpose is to avoid too much heat when the smoke away. Improve the thermal efficiency of the boiler, is provided in the back pass boiler economizer heating surfaces, the use of flue gas heating boiler feed water, to save energy, economizer after the installation, the boiler increases the thermal energy required for heating the feedwater, boiler water and so reducing the temperature difference between the water supply, reduce the burden of heating boiler feed water. Cause excessive number of boiler economizer can not play a role, resulting in waste of energy; These are high-quality industrial boiler company to share some notes selected industrial boilers; vast land of our country, many places are rich in coal, resulting in different types of coal , which has also become a basis for selection of parameters and select the number of boilers enable us to be more effective in energy conservation, to achieve a win-win.
Gas Steam Boiler non-normal stall, a phenomenon and treatment, flame reasons: 1, the operation of the auxiliary power supply or trip interruption. 2, coal fired boiler water tube san fernando la union combustion instability. 3, the load is too low, so that the load sharply mill automatic ignition energy loss or failure of combustion. 4, mutant coal, coal volatile or low calorific value. 5, the automatic combustion flame detector failure or failure caused by tripping mill. 6, or blast furnace wall tubes serious improper boiler soot-blowing operation, a large amount of water vapor into the combustion chamber. 7, coal pulverizing system, fuel system failure, resulting in a significant amount of fuel reduction or interruption. Or with a large amount of water in the fuel oil gun blocked too many impurities, low pressure steam or atomized. Second, the phenomenon: 1, a significant increase in furnace pressure, furnace flame monitoring flameless CRT display. See the fire no fire hole, BTG warning window MFT warning lights. 2, the unit load decrease, the steam flow drops rapidly, each segment working medium temperature, the vapor pressure decreases, the value of oxygen surge. Third, the method of treatment: 1, if the MFT tripping protection, should an emergency shutdown processing, stop the supply of fuel. 2, identify the cause flameout, and try to eliminate, to conduct a comprehensive inspection of the boiler, after confirming the device properly, can restart. How early circulating fluidized bed boiler ignition achieve the protection of reheaters? Fire causes of valve failure chemical industry regulation and Countermeasures bearing parts heat treated high boiler common defects due to low bypass the security gate and reheaters failure phenomenon and treatment of condensate pump turbine worm gear failure cause analysis and improvement measures in the pneumatic valve powder operating system instructions on how to implement.