dzl packaeged chain grate coal steam boiler
What part of the body including the boiler? What role have? It comprises a crucible and the furnace: a body: refers to a soda boiler system, which is superheated by the reheater water preheating system and a vaporization system composed of dry steam. The role of the high-pressure boiler feedwater heater through the further heating evaporation, for the purpose of blowing rpm turbine to do work. System configuration: economizer, the drum, the downcomer, water wall, superheater, reheater, economizer high pressure heater outlet feedwater is introduced into the economizer, economizer tube within an outer absorber tube gas and fly ash heat, water temperature increases to about 300 ℃ drum water out from the economizer line into the bubble along the top of the boiler disposed outside. Drum lower half of the water, the upper half steam. Unsaturated high pressure drop along the water reaches the bottom of the bubble tube at the bottom of the lower header outside the boiler, a number of pipes mounted in parallel on the bottom of the boiler around the lower header, the furnace by the upward flow of the absorbent in the central flame of the inner tube wall pipe convective heat radiation heat transfer and high temperature flue gas. Since the heat absorption is much less than the water vapor, the water wall within a predetermined vaporization rate can not be greater than 40%, because the working fluid will easily melt late Wall water absorbing tube rupture occurred. Downcomer role is water vapor to the bag waterwall lower header, to establish a water circulation. Wall water in the tank through the second line and then returned to the boiler water wall, the water in the drum is completed, the downcomer, the circulation between the superheater waterwall separated in the steam drum is withdrawn from the top of the drum, laying into the first top ceiling superheater, then through the cladding wall superheater, low temperature superheater, platen superheater, to a high temperature superheater, after reaching the rated temperature of the heating steam turbine into work. After the reheater boiler is also provided with a large reheat means that steam from the high pressure cylinder acting, temperature and pressure of the exhaust gas is reduced, the exhaust gas is heated to a reheater, and then returned to the steam turbine, a low pressure cylinder continues to work. Furnace body: it refers to a boiler furnace combustion system and its role is to heat the fuel combustion in the furnace as much as possible and transfer heat to the working fluid, and the completion of the water wall and economizer water water heated in the tubes, heated in the dry steam superheater and reheater tubes, the air in the air preheater tube heated. The system consists of: a combustor, furnace, air preheater. Production process: raw coal from the coal by the belt conveyor to the higher field position of the coal bin, the bottom of the coal from the coal bin out through the stoker evenly into the ground to a coal mill. Nature of the atmosphere via the air inlet of the blower is arranged in the vertical flue to the boiler air preheater, subjected to heat of the flue gas, flue gas waste heat recovery. About 250 degrees out of hot air into two air preheater from: one directly introduced into the burners of the boiler as secondary combustion air into the furnace; the other can be introduced into the mill inlet for drying, transporting coal, which said primary air portion of hot air. Excellent flow of drying gas and pulverized coal mixture powder consisting of primary air, conveyed via line separator to be coarse coarse separator, the separated coarse powder inlet sending back regrind mill, and eligible powder and primary air mixture into pulverized powder separator, gas separation, the separated coal fines into storage to save it from the powder according to the magnitude of the thermal load of the boiler, the control of coal flow discharged coal warehouse bottom while separated from the fines separator as the primary air pulverized coal power delivery, after the pressing of mill powder mixture with the gas mixture into a fine powder fed again by a burner into the combustion furnace.
Many model biomass fired boilers in Malaysia can be choose,Suitable for burning a wide range of biomass fuels such as palm shells/fibres/empty fruit bunches, wood waste, coconut fibres etc as well as coal, and make it suitable for sugar mill and wood related industry. Popular steam capacity range from 2tons/hr to 50 tons/hr.
Shunde main business of special sea oil production and processing, etc., in the course of special oil refining, a large amount of steam required for oil and gas extraction, distillation and extraction technology and other aspects, therefore, the boiler is supplied special sea oil processing technology company Shunde indispensable less equipment. As environmental policy progresses, the chemical industry as more polluting industries are highly valued the various departments of quality supervision, sea Shunde companies to follow the development of the State Environmental Protection pace, choose clean the boiler industry-leading fast Boiler cooperation with the parties by quickly assess the specific needs on-site estimates and sea Shunde, to provide a SZS series of 25 tons of steam water tube dzl packaeged chain grate coal steam boiler (SZS25-2.0-YQ).
The heat loss of exhaust smoke is the largest of all kinds of heat loss in boiler. Generally, the heat loss of exhaust smoke is 6% of the heat fed into the furnace, and the heat loss of exhaust gas increases 0.5% when the temperature of exhaust gas increases by 12 ℃ and 15 ℃. So the exhaust temperature is one of the most important indicators of boiler operation. The following are several possible causes of increased flue gas temperature in the furnace: (1) slagging and ash accumulation on the heated surface. No matter it is the slag accumulation in the water-cooled wall of the furnace, or the ash deposition in the superheater, convection tube bundle, economizer and preheater, the thermal resistance of the flue gas measurement will increase, the cooling effect of the flue gas will become worse due to the deterioration of the heat transfer, and the exhaust temperature will rise. (2) excess air coefficient Big. Under normal conditions, the exhaust temperature increases with the increase of excess air coefficient at furnace outlet. After the increase of excess air coefficient, although the amount of smoke increased, the rate of smoke increased, and the convection heat increased, the increase of heat transfer was not as much as that of the increase of flue gas. It can be understood that after the increase of smoke speed, the flue gas leaves the heating surface without time to transfer heat to the working fluid. (3) the air leakage coefficient is too large. The flue gas leakage in the furnace and rear shaft of a negative pressure boiler is inevitable and the leakage coefficient allowed by a certain heating surface is specified. When the air leakage coefficient increases, the effect on the exhaust temperature is similar to that of the superheated air coefficient. And the air leaks away. The closer the furnace is, the greater the influence on the rise in exhaust temperature. (4) Water supply temperature. When the steam turbine load is too low or the high pressure heater is out of line, the feed water temperature of the boiler will be lowered. Generally speaking, if the fuel quantity is kept constant, the heat transfer temperature difference of the economizer decreases and the heat absorption of the economizer decreases when the feed water temperature is increased, which makes the exhaust temperature increase. (5) moisture in the fuel. The increase of moisture in the fuel increases the amount of smoke, thus increasing the exhaust temperature. (6) Boiler load. Although the boiler load increases proportionally, the amount of smoke, the amount of steam, the amount of water supplied, and the volume of air increase proportionally, however, the flue gas temperature at the furnace outlet increases proportionally. Increase, so that the exhaust temperature increased. After increasing the load, the outlet temperature of the furnace increases, the heat transfer temperature difference of the convection heating surface increases and the heat absorption increases. Therefore, the more the convection heating surface is, the less the influence of the boiler load on the exhaust gas temperature is. (7) fuel varieties. When the low calorific value gas is fired, the radiative heat transfer in the furnace decreases due to the decrease of furnace temperature, and the non-combustible components in low calorific value gas, mainly N _ 2, CO _ 2 and H _ 2O, increase the amount of flue gas, so the exhaust temperature increases. Although the excess air coefficient of furnace outlet is lower than that of coal burning, the ash content in the fuel oil is very low after the pulverized coal furnace is changed to burn oil, although the excess air coefficient at the furnace outlet is lower when burning oil. There is no larger ash particle in flue gas, and there is no cleaning effect of larger ash particle on the heating surface, and the convection heating surface is polluted more seriously. Therefore, combustion is not good, often smoke-emitting boiler smoke temperature rise. When there is a steel ball dust removal device at the tail, the exhaust temperature is slightly lower than that of burning coal because the tail is cleaner. (8) the operation mode of pulverizing system. For a closed pulverizing system with a silo, when the pulverizing system is in operation, as a part of the water in the fuel enters the furnace, the furnace temperature decreases and the flue gas increases, and the cold air leaking into the pulverizing system enters the furnace as a primary air during the operation of the pulverizing system. Reduction of air flow through air preheater To raise the exhaust temperature. On the contrary, when the pulverizing system is shut down, the exhaust temperature decreases.