fire tube 9 ton gas steam boiler prices
Boiler Association party leaders to come soon Group: innovation and development has won high praise, Secretary General of China Association for boiler water treatment boiler and arrogance Ling Wang, Assistant Secretary Guo Hua, chief engineer Tongyou Wu and his party three people come fast Boiler Group inspections visits, Luhai Gang president accompanied by full enthusiasm.
Matters needing attention in installation of Gas-fired BoilerGas-fired boiler also says that gas-fired heating boiler is a kind of boiler which uses gas combustion to heat water to satisfy people's heating. It belongs to the category of domestic boiler. By gas-fired heating boiler we usually refer to gas-fired atmospheric hot water boiler, gas including natural gas, liquefied gas, city gas, coke oven gas, biogas and so on. There are explosion-proof doors on the rear of the fuel-fired boiler or on the smoke pipe, and the position of the explosion-proof doors should be conducive to the discharge of the explosion. In cases where explosive gas may endanger the safety of operators, a pressure relief guide tube shall be installed on the explosion-proof door. The installation of boilers, auxiliary machines and water treatment equipment shall be in accordance with the technical requirements of the equipment manufacturing plant. . The equipment foundation must wait until the equipment arrives and checks correctly with the design drawing before construction. 3. When installing the equipment, avoid the equipment, and the installation material should be stacked on the floor. When using building column, beam lifting equipment, the bearing capacity of beam and column must be verified in advance. 4. After installation of oil, gas, hot water and steam pipes, the pressure test acceptance shall be carried out according to the Code for Construction and acceptance of Industrial Metal Piping Engineering GB 50235 / 1997.
Water wall boiler tube leak or burst phenomenon how to do 1, the normal water flow is not greater than the steam flow. 2, the furnace pressure transient and unstable prejudiced. 3, tube leak detection alarm device. 4, the furnace may not tight at the outward discharge gas and water vapor, and a significant leakage sound. 5, the main steam pressure drop. 6, boiler combustion dark flame instability caused by severe boiler fire. 7, when the induced draft fan is automatically cast, abnormal static vane opening is increased, the current increases. 1 reason, the presence of water wall tube material defects or post-production, the installation of the damaged pipe, poor welding quality. 2, the inner tube fouling overtemperature. 3, the inner tube corrosion. 4, water wall wear. 5, the long-term high load operation, furnace coking, coal sulfur corrosion caused by high temperature water wall. 6, improper combustion, flame deflection. 7, in the possession of bad foreign body, the water cycle. 8, the wall of the long-term over-temperature operation. 9, the temperature difference between waterwall tubes, mechanical stress crack. 10, the normal exit or drain sootblower steam punctured tube. 11, smashed chunks of coke furnace water wall tube or serious explosion occurred, resulting in water wall tube suffered external damage. 12, boiler overpressure long run. 13, the boiler starts to heat up, step-up too fast. 1 process, the leakage should try waterwall tubes outage. The leakage is not serious, while still capable of maintaining operation, note that each of the automatic operation when the device, if not normal, it is cut immediately to the manual, if necessary, may be down, down-load operation. Closely monitor the development trend of damaged parts, good accident anticipation, application shutdown as soon as possible. 2, if the leak is serious, the bursting point temperature after a sharp rise in quality work, leading to serious over-temperature wall, unable to maintain the normal operation of the boiler or threaten the safety equipment, emergency shutdown provision should be processed, when the steam temperature to protect the action value, the protection does not move, should immediately hand MFT. 3, note that the operation of the electrostatic precipitator, to strengthen the inspection checks, to prevent fouling, and the electrodes ESP hopper, pipes and the like plugging air preheater ash. 4, after the shutdown, should retain ID fan, the furnace pressure is maintained constant, there is no discharge to be stopped after soda ID fan.
After the gas hot water boiler hot water boiler vaporization emergency 1. Vaporization handler circulating pump stops abnormally pump failure caused by: ① blower stops running immediately. ② immediately open the door, take measures to pressure the fire, lift the chute gate, cutting off the supply of coal grate. ③ In the case of boiler pressure not greater than 0.6MPa (600KPa), the exhaust valve to follow, only a sharp rise in pressure in the boiler deflated, used only relief exceeds 0.9MPa, and the exhaust process to be carried out slowly, prevention boiler due to loss of pressure and more violently again vaporized. ④ close the boiler water, water main gas valve. ⑤ open stop valve recirculation line, to ensure that the water supply pipe velocity convection heating surface (economizer) to prevent re-vaporization of the economizer. ⑥ The operation of the above operation, at the same time to pay the boiler to reduce the boiler water temperature and the furnace pressure. ⑦ After the boiler pressure is normal, i.e., opening the standby circulating pump, into the normal combustion. 2. Treatment failure or sudden loss of power boiler vaporization of power: ① immediately open the door, lift the coal chute slide gate to take pressure fire measures to reduce the oven temperature. ② Grate with the fastest speed in order in the shortest time to fire onto the slag tap. ③ the degree of treatment in the first case. Once a short time can not supply heating network system, antifreeze should take emergency measures. 3. Due to excessive heat boiler boiler vaporization process: ① the immediate closure of the drum, induced draft fan. ② immediately open the door, take measures to pressure the fire, lift the supply of coal chute slide gate, off of coal, while the grate into fast gear. ③ In the case confirmed the presence of water, the boiler can supply water to the boiler body, boiler out of the water while closing the main valve. ④ Open line stop valve recirculation pump to ensure water velocity convection heating surface of the pipe, to prevent the economizer again vaporized. ⑤ Open circulating pump with jog mode, jog each time less than 30 seconds, again less than one minute jog interval. Jog purpose is to reduce the boiler water temperature, while preventing a large amount of steam into the pipeline system. ⑥ back into place after the safety valve, circulating pump running, and then the normal burning stove. 4. Water boiler system run vaporization process due to water loss, loss of pressure caused by: ① immediately closed drum, induced draft fan. ② out of the water while closing the main valve and the boiler circulating pump. ③ take the same measures to cool the furnace tube described above. ④ Open stop valve recirculation line. ⑤ rely exhaust valve until the safety valve back into place. ⑥ until the boiler water temperature drops below 50 ℃, when the temperature of the furnace temperature less number 200 ℃, again within the boiler feed water, water course to be carried out slowly, to prevent harm to the boiler when the temperature is too large. ⑦ After processing leakage fault, the system time to the replenishment, and out of the water boiler always open the valve, and the circulating pump, and then normal combustion.