wns fire tube low pressure gas fired steam boiler
Depending on the operating characteristics of electric wns fire tube low pressure fired steam boilers, mainly to properly regulate the drum and induced draft fan. The chamber negative pressure is guaranteed ± (5-10) premise mm water column (water column ≈9.8Pa 1mm) to minimize the amount of the wind, to extend the residence time of the flue gas temperature in the furnace, reduce exhaust gas temperature.
Industrial gas boilers small volume itself, and these need not be equipped with auxiliary equipment, simply set up between a host and auxiliary room, set on more messy, covering economy. Industrial gas boiler city gas source is generally taken from the intermediate pressure gas supply line, the gas pipeline laying gas sampling point to the boiler room, then according to quell's brand, type and caliber regulating device applications, scheduling outlet pressure range, by metering the put into use. Establish a set fee just gas network tariffs, pipeline fees, hot walks pipeline fee. Gas pipeline network overall cost of capital is the sum of the gas company funds charged to the user, can be determined depending on the circumstances around the gas company. Usually adopted buried gas pipeline type, buried depth is generally about 0.8m ~ 1.0m, seamless steel pipe can be selected or PE pipes, pipe surrounding sand 15cm ~ 20cm plating, hot water pipe laying relatively simple, somewhat messy steam pipe walks . 3, industrial gas boiler room planning results in the presence of 3.1. Selection of the size of the heat load of the boiler and its expansion tend to choose the boiler capacity, the number of great links. The larger heat load, single boiler capacity should be large. The near future can be greatly increased thermal load, is also relatively large capacity boiler can choose, it will expand the load thought. The only thought to increase the long-term thermal load, the expansion device may leave the boiler placeholder deployment end in the boiler room, or space left on the total FIG. However, in the practice of project planning, often there is a lack of expansion heat load estimates, constitute improper boiler selection, pre-operation to cause unnecessary trouble. 3.2. Gas boiler gas regulator trivial results generally used in high-pressure (less than 5kPa) and medium voltage (5 ~ 150kPa) trivial. Gas usually before entering the boiler room will arrive this requirement. Now the gas hot water boiler is equipped with a high level of automation subsided, a calm requires the gas pressure is lower, so before further demand into a calm pace pressure boiler manufacturers themselves generally equipped. Gas pressure regulating trivial demands reliable equipment, but on the size of the gas pipeline valve is open due to the gas pressure when scheduling the gas pressure is high or low, and tempering will cause off, start and stop frequently subsided's configuration, thereby affecting the boiler work. 3.3. Gas boiler quality results planning standard gauge, the quality can not be ensured when the gas, should be provided or dust, oil and water, respectively, and a total closed drain valve before the gas main pipe before the regulator device. Most of the oil production plant in the use of oil with anger, it is often said of moisture in the summer cold weather, moisture and light hydrocarbons and other substances containing moisture, condensation will constitute a line blockage, an initiative to quell the flame, impact Heating. 3.4. Chimney condensate results because of the high thermal efficiency of industrial gas boiler, a low exhaust gas temperature, typically 180 degrees, the boiler room planning criteria (GB50041-2008) rules industrial gas boiler room chimney should be reinforced concrete or steel chimneys chimney. Chimney will appear directly in the outdoor summer steel chimney condensate freezing results, constitute icing light rusty steel chimney, would constitute a temporary corrosion, freezing severe affect chimney smoke. 3.5. The amount of air to quell the outcome's when quell Industrial gas boiler is in the boiler room, the air between the boiler must be satisfied the requirements apply to quell the device, otherwise there will be no abundant natural gas to quell working carbon monoxide poisoning.
Pressure boilers Products of the non-pressure hot water boiler, also called pressure boilers, boiler usually refers to the top does not bear the water column static pressure of the heating system. That is quite an open hot water tank. Meaning pressure boiler: boiler body opening to the atmosphere. In any conditions, the boiler at the water line are zero gauge pressure boiler. Pressure boilers Model consists of three parts, connected by a hyphen between the parts. Categories: pressure hot water boiler is mainly classified by fuel can be divided into CLDR (CWDR) often piezoelectric hot water boiler, CLHS-YQ (CWNS-YQ) pressure fuel (gas) hot water boilers, pressure coal-fired hot water boilers. Model: The first part of the model by atmospheric pressure boiler code, pot-type code, combustion equipment code, the rated thermal power four sections. Boiler pressure is represented by C code example: CLSG0.35; 95/70; W12 represents a vertical pipe fixed grate boiler pressure, the rated thermal power of 0.35 mW, rated outlet water temperature was 95 deg.] C, the nominal temperature of the water inlet. 70 ℃, burning anthracite class I, a second design of the boiler. Product Structure: The overall structure of pressure boilers and boiler auxiliary equipment including two parts. Boiler furnace, drum, burner, water wall superheater, economizer, air preheater, and the furnace wall, etc. The main frame member constituting the core part of the steam production, called boiler. Boiler body is in two main parts and drum furnace. Also known as the furnace combustion chamber, fuel combustion for space. The solid fuel on to the grate, referred to as a fire bed combustion furnace Stoker, also known as fire bed furnace; solid fuel furnace liquid, gas or pulverized, is injected into the combustion chamber is called the fire chamber burner, also known as the furnace fire chamber; air coal particles burn hold it was boiling, and the furnace is inferior fuel suitable for combustion is called fluidized bed furnace, also called fluidized bed furnace; coal particles so that an air flow rotated at high speed, and strongly called fire cylindrical cyclone furnace hearth. Furnace design needs to fully consider the characteristics of the fuel used. Each boiler should be fueled with the original design of the fuel. Boilers running economy and reliability are likely to vary greatly reduced when using the characteristics of fuel combustion. And the natural circulation drum is repeatedly forced circulation boiler receiving feedwater to the economizer, the coupling cycle and supplying saturated steam superheater cylindrical vessel. Simplified drum made from high quality steel plate, is one of the heaviest components of the boiler. Safety knowledge; boiler is a high-temperature, high-pressure thermal equipment, is one of special equipment, widely used in government agencies, public companies and all walks of life, are dangerous and special equipment. Event of an accident involving public safety, it will cause huge losses to the state and people's lives and property. For public safety, people's lives and property safety, according to the State Council, "Regulations on Safety Supervision of Special Equipment", the boiler should use full attention the following matters: 1, should be accompanied by safety technical specifications of the factory boiler design documents, product quality certification, safety and the use and maintenance instructions, supervision and inspection certificate (safety supervision, inspection and performance certificate). 2, boiler installation, maintenance, alteration. Engaged in the installation of the boiler, maintenance, renovation of the unit shall obtain special equipment installation and maintenance certificates issued by the Provincial Quality and Technical Supervision, before engaging in the boiler installation, maintenance, alteration. Construction unit before construction will be prepared for installation, maintenance, alteration in writing inform the special equipment safety supervision and management department of the municipality or district, and will start informing sent to the local county level Quality and Technical Supervision for the record, told immediately after construction. 3, inspection of boiler installation, maintenance, transformation. After construction, the construction unit To State Quality and Technical Supervision of Special Equipment Inspection and hydrostatic testing of the boiler installation supervisory inspection declaration. After passing by the State Quality and Technical Supervision, State Special Equipment Inspection, County of Quality and Technical Supervision involved in overall acceptance. 4, registration boiler. After the boiler inspection, the use of units must be in accordance with the "special equipment registration and use of management rules", fill "boiler (census) Registration Form", the State Quality and Technical Supervision to register and obtain a "registration certificate to use special equipment safety . " 5, operation of the boiler. Boiler operation must be performed by trained and qualified to obtain "special equipment operator certificate" certified personnel to operate, must strictly abide by the rules and eight systems, six record. 6, check the boiler. Periodic inspection of boiler once a year, not be used without safety periodic inspection of boilers. Safety accessories safety valve of the boiler regular inspection once a year, pressure gauge biannually verified, may not be used without the periodic inspection of the safety accessories. 7, non-pressure boilers will be installed for the boiler pressure. Do not use water level gauge, safety valve, pressure gauge three safety accessories insufficiency boiler. Daily operation and maintenance: ⒈ chemical contact, turbine attendant prepare enough desalinated water, oxygen, water passing temperature no higher than the drum wall temperature 50 ℃; Sheung during hot water temperature should not be to the drum wall metal temperature difference greater than 40 ℃ .⒉ new installation or after recording before overhaul boiler Feed expansion departments indicated .⒊ Sheung summer time less than 2 hours, at least 4 hours in winter, when the temperature and Sheung drum wall temperature difference of less than 40 ℃ how reheater be preserved? ⒈ turbine after playing brakes, boilers ensure a blower, an induced draft fan is running the best cross reserved two oil gun .⒉ open reheaters to the empty exhaust steam reheater hydrophobic doors and air doors corrosion, anti-corrosion of the reheater steam temperature is lower than a predetermined deg.] C for 400 .⒊ control drum water level within the permissible range .⒋ preservation time less than 20 minutes after stopping two oil gun operation guaranteed .⒌ when the furnace pressure 50--100Pa, each of the flaps open, baffle for ventilation less than 5 minutes, stop sending, fan, each of the flaps closed tailgate may be appropriate to accelerate Sheung speed.
Anyang City Minshan Nonferrous Metal Co., Ltd. is a collection of urban mining, renewable resources, energy as one of the economic wisdom of cleaning companies, mainly non-ferrous metal extraction and processing work. Company to conserve energy, cleaner production for the purpose of this concept coincides with the fast boiler. Thus, when the company in the purchase of the product boiler, and fast boiler almost hit it off, by the party to provide a fast 6 tons of steam integrally condensing gas wns fire tube low pressure fired steam boiler (WNS6-1.25.Y.Q).