Coal Fired Steam Boiler Used In Textile Sugar Factory
Blue Sky Battle horn started, our country constantly walking on the green road. Reduce atmospheric emissions of nitrogen oxides, improve air quality, but also the people a blue sky, the industry has invested in the construction of environmental protection go, Guizhou Baiyun Quan Lake Hotel is no exception. As we all know, fast boiler R & D in the field of clean fuel boiler never stopped, through market research and screening, Guizhou Baiyun Quan Lake Hotel in October 2017 signed a low-nitrogen Thalia T5 series vacuum hot water and fast boiler boiler for hot water supply and heating the hotel.
Gas-fired coal fired steam boiler used in textile sugar factory steam boiler gas to become the market trend is for countries to protect the environment, to control environmental deterioration and promote the steam boiler, gas steam boiler reconstruction is an arduous and urgent major project. Why the high price of coal to gas has changed, serious pollution of coal, especially in the past two years haze is particularly serious, mainly from coal to gas deal with environmental pollution, but the operating cost is much higher than gas. But the long-term development, economic development and should not expense of the environment, protecting the environment is everyone's responsibility. After gas steam boiler into a gas steam boilers, gas consumption is how much? Do not control coal, substantially in accordance with your boiler power to calculate, but one thing you need to think clearly, with the efficiency of gas-fired boiler efficiency gas boilers were quite different. So when you change 4 tons of coal boiler gas boiler, you can consider using a smaller gas-fired boiler. Coal to gas is a national policy not to install all right? Not installed, then it is possible, but now the country for gas-fired boilers is gradually ban, not to use, and if you do not choose coal to gas, then you need to select the coal to electricity, coal to heat pump etc., the gas must be slipping, these types of coal to the way you can compare each to see which is more suitable for their own gas steam boiler steam boiler gas into the benefits of what. Gas steam boiler includes a central water heater, new energy-saving, high efficiency stainless steel burner, electronic ignition pulse, a stainless steel coil heat exchanger, a strong discharge blower, intelligent control assembly elements, security devices and the like, the use of liquefied petroleum gas, natural gas, gas and other gaseous fuels, using the latest combustion technology design and manufacture of the heat exchanger, the thermal efficiency up to 95% water fast heating speed, high flow, with energy saving, easy to scale, automatic control without staff on duty, easy maintenance and so on. Economic and environmental performance far superior to the conventional type boiler modules may be stand-alone or in combination of line. Gas-fired steam boiler to save land resources, the same will not cause pollution like soot gas boiler. Gas boiler need to go through dust, slag process, complicated process, where the same water, gas boiler more environmentally friendly.
Fire fighting methods inventory boiler in the boiler use, if a fire phenomenon, you know how to deal with it? Today, Xiao Bian teach you the recipe. When coal is poor or low load, it may be administered less number, to maintain a high pulverized coal concentration, but can not chipping operation or asymmetric operation. Load is less than 170MW, should remain A, B powder layer to stable operation, when any failure to a powder, should be administered stable combustion, the failure to the powder to be put into operation, combustion stability, and then exit the gun run . Adjustment of the amount of the low-load air supply, to maintain the oxygen 4-5%, and adjust the opening degree of the auxiliary windshield. If it is a bad case of fire, may be appropriate to increase the primary air temperature, wind speed reduces time, but not overshoot the spark plugs burned once or blocked ducts. When the job should be strictly periodic system and to reduce powder powder switching system, dust bunker normal position at least 2.5 meters, so that a stable working state bunker, at each adjusting shutter powder to powder, the powder as far as possible amount consistent and stable, no spark plugs to prevent dust and to dust gravity caused by combustion fluctuations. Should maintain acceptable fineness of pulverized coal, according to chemical analysis, after adjusting the test plate to open Classifier, coal is poor or low load, it may be appropriate to increase the fineness of pulverized coal, in order to facilitate combustion. Maintain normal milling system, powder separator shall not clogging the tertiary air pinkish large deterioration in combustion. Furnace can eliminate air leakage and air leakage milling system, all view of the fire without plugging holes, play Giocondo, etc. should be tightly closed. Value of the long should keep abreast of the situation of coal and coal quality fuel, combustion instability occurs when, such as when a fault powder, coal mutation, the differential signal changes drum is too large, the oil should immediately cast coal combustion stability and taking samples for analysis. High load, the premise of ensuring steam temperature, combustion can be appropriately adjusted to prevent the shift of the center of the flame, so that the furnace exit gas temperature rise, caused by coking. Operator adjusting the main steam temperature may be employed with positive pagoda wind run, the central flame stabilizer. Should be a bellows pressure control as a basis for wind speed, in time to observe the duct pressure and temperature, the premise of ensuring primary air duct is not blocked, a bellows pressure should not exceed 4000Pa.
Main coal fired steam boiler used in textile sugar factory temperature abnormal phenomenon of how to do 1, main steam temperature anomalies alarm. 2, the rapid variation of the main steam temperature, a secondary damper frequently significantly reducing water operation. 3, starting superheat outlet steam separator above or below normal. 4, if the steam with water, the unit will water shock occurs. 1 reason, the fuel and water supply imbalance, the separator outlet temperature abnormality. 2, coal combustion conditions change or affect, such as excessive load lift; and pulverizing mill administration system abnormality stop; means automatically increase or decrease the failure rate is too large amount of wind and the like. 3, the central flame furnace changes, such as the bottom seal damage, W and inadequate flame downstroke. 4, the control failure by warm water, warm water flow rate reduction is abnormally reduced or increased. 5, feedwater temperature mutation. 6, does not match the wind coal. 7, the secondary combustion heating surface. 8, furnace coking or fouling seriously. 9, heating surface leakage squib. 10, flue gas damper opening degree is not normal. 11, coal sudden change occurred. 12, the uniformity of the powder feeding substantial change occurs. 1 process, failure caused by unit coordinated coal - water ratio should be immediately released coordinate offset, in accordance with the current load demand, with reference to the start of the steam superheat separator, and adjusting the amount of fuel corresponding to the amount of water, with one, two main desuperheating water rapidly steam temperature control in a normal range; when the coal - water ratio should avoid imbalance after coal and water while adjusting; when coal - water ratio is adjusted to further adjust the load after a relatively stable; contact maintenance processing timely. 2, when the water supply system fault condition occurs a significant disturbance furnace should pay attention and automatically coordinated working conditions, so as not to manual intervention, when not working properly coordinated and automated, should be manually adjusted, stable water flow, referring to separation according to the water flow steam superheat, the adjusted amount of fuel, with a secondary spray water rapidly controlling the main steam temperature within the normal range; contact maintenance processing timely. 3, due to rapid changes in load caused by the load change rate should be adjusted; load change caused due to protective operation or the like caused by heat load to be quickly adjusted to maintain the boiler pressure of the main steam stability. 4, by warm water automatic dysregulation, should be appropriate Save warm tone is switched to the manual may be an intermediate point of the feedwater control system be corrected for temperature if necessary, or the feedwater to switch control to manual control, due to lower lifting and lowering the load speed to prevent steam temperature, promptly contact a service process. 5, the boiler furnace cause severe fouling and coking of the main steam temperature anomalies can be corrected by an appropriate degree of superheat outlet steam separator start, adjust, and in a timely manner and the furnace heating surface sootblowing. When the platen superheater sootblowing or superheater outlet temperature is still above normal and a secondary reducing water damper fully open, to check the furnace and the combustion air distribution system is normal, the checking process to reduce still overtemperature unit load. 6, flue gas damper adjusted to an appropriate opening degree. 7, if the bottom seal after losing back to normal immediately. 8, to strengthen the turbine expansion, differential expansion, axial displacement of the shaft vibration and bearing temperature monitoring, if abnormal, the process according to the corresponding regulations. 9, after the above measures, if invalid, should immediately drop the load process. 10, in front of the main steam temperature main steam 50 ℃ drastically reduced within 10 minutes, should an emergency stop.