Vertical gas fired steam boiler used in textile mills in Jakarta
Vertical projection which features good vertical fired steam boiler used in textile mills in jakarta boiler having a vertical steam energy conversion device, the input of thermal energy by chemical, electrical, and high temperature flue gas to the furnace, thereby converted into electrical energy, and to provide the desired life for people heat, on the safety and convenience of all with excellent product qualities, then what good salient features vertical steam boiler has it? 1, reliable safety performance vertical steam boiler in terms of product safety has a lot of protection, by ground fault protection, overvoltage protection and power protection and other measures to make operation of the boiler can always be in a safe state, when the pressure is too low or there is leakage, the boiler will cut off its own power button, so to ensure the life and personal safety of the boiler. 2, the portable vertical steam boiler operation which is preferably used, which have to see ease of operation and convenient operation of the boiler does not require user intervention excessive production process, just to the introduction of the electric power source control box start button to enter the automatic operation state, and when the job if the amount of water in the furnace suddenly reduced, the vertical steam boiler control system is also used to automatically replenish the water in the water tank to fill the pump through the apparatus in order to achieve high efficiency of production operations process. 3, small size and yield stability compared with the conventional boiler products, the type and volume of the vertical steam boilers are an advantage, not only a wide range, and the volume of the boiler is very small, but it has a large steam room to make product productivity and quality are the most significant upgrade in order to obtain a more stable production company that won the biggest profits. The above is a brief introduction which has a prominent characteristic of a good vertical steam boiler, not difficult to find, the boiler reliability in terms of safety and convenience of operation have notable features, but also in the volume and yield stability also has a prominent feature , production efficiency and product quality to make the most significant upgrade, but also to ensure personal safety as well as the effect of the use of the boiler.
2 t 2 t introduce gas boiler gas boiler burner arranged good technical performance, the use of automatic combustion ratio adjustment, automatically adjust the water supply, the program start and stop, automatic operation and other advanced technology, and having a low water level and low level alarm, high . steam pressure, turn off automatic protection function of the boiler has a compact, safe, reliable, simple, rapid installation, low pollution, low noise, high efficiency features: 2 tons of gas vertical fired steam boiler used in textile mills in jakarta with a leading domestic level, and industry compared to the same parameters of the boiler, with a compact, power, fast boosting, high thermal efficiency. Advantages: use all wet back shell type pyrotechnic tube structure. This structure because of its compact structure, small footprint, originally applied in the marine boiler. This architecture uses three return, the oil mixed with air or gas well through the atomizing burner, complete combustion in the furnace in a corrugated, folded from the rear chamber into the first tobacco smoke return pipe to the front smoke box to the second return pipe tobacco, cigarette box, is discharged after the last to enter the chimney.
Exhaust gas has been plagued by sewage paper industry, paper industry pollution problems of the country very seriously. Fujian Heng paper packaging company has been committed to the use of clean-type boiler paper processing. October 22, 2016, David Carse, the paper with my company, signed a 6 tons of steam an integral condensing vertical fired steam boiler used in textile mills in jakarta for the production of corrugated cardboard and other paper products. I provided the boiler greatly solve the problem of sewage wastewater Heng paper. After the boiler operation, both to meet local environmental requirements, but also reduce operating costs for the constant boiler paper products.
The main reason gas vertical fired steam boiler used in textile mills in jakarta produces smoke which fuel gas steam boiler main cause of smoke. A fuel gas steam boiler: oil, gas oil quality is not good when the gas contains more water, reduce the heat value of the fuel, while producing steam, the furnace temperature tends to decrease, making it difficult to burn, easy to produce smoke. Water and more oil, mainly when unloading rain water into the oil during heating the oil in water vapor penetration. When the oil contains impurities, the impurities unburned produce fine coke, the coke into fine smoke, dust becomes large, and the formation of soot. Impurities contained in the oil and gas, but also affect the pure oil and pure combustion gas generated soot. Oil impurities, mainly due to inappropriate choice of filters or filter difference impurity removal effect. Second, the failure of the fuel atomizing nozzle member main burner fuel oil atomizing nozzle. Atomizing oil burner nozzle fails, affecting the quality of the atomization, easy to poor combustion. 1, the adhesiveness between the bonding surface of the oil and the consequences of failure oil atomizers swirl atomizers and the splitter plate well, leakage will occur, atomized large oil particles, increasing the amount of fuel injection and the like. In this case serious deterioration of the quality of the combustion, the oil droplets have landed on the water wall, stacking up oil coke, partially unburned black smoke into droplets. The tangential swirl chip groove clogging mist causes uneven density distribution in the dense side of the oil mist, combustion air be insufficient. In the more dilute side of the oil mist, combustion air causes severe local excess. Mixed with oil, wind conditions deteriorated significantly, combustion conditions deteriorate, resulting in black smoke. 2, spray atomization slice failure and the consequences of failure to clogging and wear. Nozzle clogging, resulting in blockage of the fuel injection quantity is not glib increase, oil particle size thicker, the effect of fuel poor and black smoke. Wear injection port, a large hole diameter, increasing the amount of fuel injection, increasing the particle size of oil affect combustion efficiency, produce black smoke. The use of artificial gas burner, naphthalene and tar and other impurities will block the nozzles, the influence of gas distribution, resulting in black smoke. Should therefore be cleaned regularly, or clogging of the selected burner. 3, the partition partitioning poor poor, insufficient supply of air into and excess. The amount of air can not meet the requirements of the fuel combustion, so that combustion of fuel can not be sufficiently black smoke. The amount of air, will result in lower combustion temperature, black smoke and fuel difficult to burn. 4, the furnace temperature is too low when starting the furnace, fuel oil steam boiler furnace temperature is too low due to easy black smoke. 5, the furnace hearth product oil is sometimes caused by internal combustion nozzle oil accumulated inside the chamber, the oil reservoir coke black smoke at high temperature. Causes dripping of fuel combustion nozzle: ① The drip just work, just at the operating pressure is too low, the oil will flow from the nozzle, instead of the discharge. The reason for low oil pressure is a solenoid valve, the valve is clogged filter or the like or failure caused by contamination. ② In the dripping process work, probably because the relative position of burner nozzle mounting head too far, improper ignition electrode position, the oil into the atomizer, the nozzle holder is mounted is not tight, nozzle dirty, low oil pressure caused. ③ When the dripping stopped, because the line between the pump and the air nozzle, electromagnetic valve or a hydraulic valve or dirty failure. 6, the furnace flue purged countless consequences when the furnace flue remnants of oil and gas, when gas purging endless, high temperatures encountered in the explosion and black smoke. 7, the furnace smoke, sparks, the furnace pressure is too ①; ② inappropriate choice of the burner, the burner flame is too long or too much power; ③ improper combustion ratio, there are more to produce products of incomplete combustion; ④ atomization quality is not good nozzle or improper installation location, or affect the combustion flame into the furnace off port; ⑤ flue is blocked, poor smoke; ⑥ a secondary air mismatches; irrational ⑦ furnace structure; ⑧ oil spray angle is selected from with improper.