98 thermal efficiency gas fired hot water boiler
Using Ultraten wings condensation boiler technology has greatly enhanced heat the heating rate; silicon alloy material design to achieve the depth of the condensing heat exchanger, high efficiency, high heat transfer speed. "APH the T7" ready to use the factory mode, the system design is simple and clear, i.e. security that is used, the best burner performance debugging the factory, the user can simply set up at the installation site, connected to gas, water, to a flue , it covers an area of greatly reduced.
The method of adjusting the temperature of the superheated steam heating stove have? The method of adjusting the temperature of the superheated steam heating stove have? DC boiler steam temperature is mainly adjusted by adjusting the quantity of fuel to water. In actual operation, because the efficiency of boiler feed water and fuel heat enthalpy (depends on the water temperature) and the like will change, so the actual boiler operation to ensure the water-fuel ratio of the exact value is not easy. Coal-fired furnace will fluctuate because of the amount of coal and the amount of fuel due to the steam temperature. So, except DC boiler fuel to water ratio as the coarse adjustment means, but also must be used as a method of spray desuperheater means of fine-tuning adjustment. There is also some boiler flue gas recirculation, dampers and methods of the swing center of the flame as an auxiliary adjusting device.
2. Oxygen corrosion
For the biomass fuel boiler pressure parts,the water side is mainly electro chemical corrosion,the fire side (or flue gas side) is mainly chemical corrosion.The oxygen corrosion belongs to electrochemical corrosion, it is mainly caused by the dissolved oxygen in water.At room temperature,the dissolved oxygen concentration is about 9.1mg / L,according to the GB1576-2001 “industrial boiler water quality” requirement ,the rated steam pressure should not be more than 1.0MPa,the dissolved oxygen concentration should not be more than 0.1mg / L,otherwise,it is likely to lead to metal corrosion.
Commissioning of Boiler gas boiler commissioning must be carried out after the hydrostatic test. Before commissioning, should be a comprehensive inspection of each furnace parts, electronic control devices, wiring, etc. are normal, water supply, oil furnace if opened, electrical contacts are in the set position. 1, depending on the size of the fuel consumption, the initial damper, the hydraulic pressure. 2, the power is turned on, the power switch to open the cabinet, the water pump starts furnace, (if the pump is rotated into the anhydrous, pump purge valve is opened, the air exhaust pump). 3, control checks whether the normal water level electrode. 4, check the burner operation is normal. Starter burner starts combustion when the water level rose to a predetermined level, the start of combustion is normal to observe: Start no vibration noise, stable combustion, no smoke, orange yellow flame, burning bright clear. Otherwise, to make the appropriate adjustment (refer to burner instructions). Note: The oil pressure between 0.8 ~ 1.0Mpa, after a good tune, do not easily change, oil pressure is too high or too low have an effect on burner performance life. 5, check the pressure gauge pointer swing is smooth, with or without loosening stuck. 6, whether the discharge check valve is set at the set pressure steam: Pressure controller first maximum working pressure, a safety valve is adjusted to the set pressure higher than 0.05MPa, when the furnace pressure was raised to whether the exhaust pressure setting, if exhaust , pulling the safety valve a few times, and try again, if not enough to deal with safety valve to adjust. Pressure relief valve setting: boiler rated pressure + 0.03MPa. 7, check the electrical contacts of the operation: When the pressure is raised to the maximum working pressure (not exceed the rated working pressure), should stop burning, open the safety valve blowing off steam, the pressure to a minimum operating pressure (maximum operating pressure is generally lowest set to 0.10MPa), combustion burner should be restarted. Note: When the adjustment screw should slow, especially when the pointer approaches the end, otherwise, damage the screw off the wire.