chain grate boiler for plastic plant
Horizontal WNS gas steam chain grate boiler for plastic plant for heating
ZG Boiler is a leading designer, manufacturer and marketer of horizontal gas and oil-fired hot water and steam boilers for space heating in residential, commercial and institutional buildings.
Since more than six months since the chain grate boiler for plastic plant equipment, heating and hot water supply well, our technical staff also view real-time remote monitoring and control through the use of the boiler to the scene, Baiyun Quan Lake hotel management staff related to our technical staff gave very great encouragement and affirmation. --customer feedback
Why chain grate boiler for plastic plant always pay? Phenomenon: the pressure gauge shows the value of frequent falling, falling. Normal water pressure of the boiler must be greater than 0.8bar, replenishment cycle in 3-6 months or more. The boiler is connected to the cooling system in the room together to form the heating system. Pressure gauge is displayed on the boiler pressure value of the entire heating system, so that the replenishment is the replenishment of the entire heating system. Therefore, in most cases often pay a heating system problems that may arise, not the problem of the boiler. One reason: in the pre-commissioning of the new system heating system commissioning new air heating system more automatic exhaust valve release system results in reduced pressure, requiring multiple replenishment. Two reasons: heating system for leaks out pipe heating system or ground heat sealing leakage may occur at the interface and the leaks little leakage, since the heating boiler is in the state of the whole system is hot, so the leakage the rapid evaporation of the water is difficult to find the leak by the naked eye. If the pressure off the boiler and can not appear to find the leak, we recommend that you check the boiler leaks. Inspection method: After stopping the boiler operation, close the bottom of the heating boiler supply and return valves (the valve can ensure shutting), disconnected from the system directly to the boiler, the boiler supply water to an integer value, a period of observation to see if there are fluctuations in pressure gauge . This method may be simply determined to be a problem after the boiler or heating system piping valve leakage problem. Reason Three: The expansion tank expansion tank failures would result in failure of the boiler heating system pressure exceeds 3bar the boiler drain valve protection. Contact your dealer for a replacement. Four reasons: replenishment valve closed lax if replenishment valve closed lax and low pressure water pipe network, the system will fall in pressure when using hot water. Solution: If frequent replenishment of the situation, need to contact the service provider, check the heating system as soon as possible to avoid long-term damage to the boiler caused by replenishment.
As the market demand continues to increase, the number of manufacturing enterprises increased rapidly, the industry is expanding. Throughout the development of the industrial chain grate boiler for plastic plant industry, although impressive, but still hidden. First, the technology industry as a whole needs to be improved. At present there are still too many industry manufacturer, producing scattered, most enterprises Shengchannengli relatively low, uneven development between enterprises, the production concentration is not high. After investigation, although most enterprises change their operational mechanism, to effectively enhance the vitality of enterprises, the market reaction was markedly increased, but some companies still lack long-term development strategy, resulting in independent development and innovation ability, lack of investment, resulting in product development and grade level is still not high, product quality did not significantly improve performance. The obvious question is that competition in the market of low-level, industry overall technological level, economic efficiency unhappy. Second, serious waste of energy.