oil or gas fired wet back hot water boiler
8 ton per hour steam boiler with gas fuel is one of our hot sales products. SZS new designs boilers is more energy-saving and eco-friendly than others. SZL Boiler is with D type and horizontal structure. This Water Tube Boiler’s Capacity is among 4 to 35ton per hour. And its steam pressure is between 1 to 2.5Mpa. We can control its steam temperature between 193 to 300℃ with consumers’ requirements. SZS boiler also has wide fuel avaibility such as Heavy oil, Light Oil, Natural gas, Coke oven gas, etc.
How to ensure the normal operation of the gas steam boiler steam boiler gas used in the process in order to ensure the proper and safe use, in the design of on improving the allocation of system protection, common protection system has five steam boilers are: water protection , pressure protection, temperature protection, flame protection, power protection self-locking, followed boiler Co., Ltd. for your details each steam boiler protection system. Gas steam boiler water level to protect the five common protection systems: steam boiler is equipped with two sets of pumps, operation and use. Boiler water level gauge plate supporting one to two, should always be compared with each other, findings indicate inconsistency shall be corrected immediately. Class water level should be flushed, to determine their true level. And also has balanced water level electrode cartridge point can accurately collect to alarm level signal or to control the pump. Common pressure protection systems protect the five gas steam boiler: steam pressure protection: When the boiler pressure exceeds the rated value, the need for chain protection: is shutdown, the system stops the combustion; fire mouth can also be varied, single-stage or two-stage combustion You can also adjust the amount of oil, so the buck, to ensure the safe operation of the boiler. Steam boilers and pressure protection as the water level, the use of multiple protection: safety valve pressure controller. Temperature protection gas steam boiler five common protection systems: temperature protection is an important procedure in the safe operation of the boiler, is particularly important for the regulation and protection of the boiler temperature steam; at the same time to regulate protective role in over-temperature oil or fired wet back hot water boilers. Prevent explosion of the furnace, the fuel (gas) boiler flame protection means must be provided, is a function of combustion (including ignition, combustion or misfires when halfway off, typically within five seconds re-ignition furnace in the monitoring, within 1 second running off into the oil (gas) solenoid valve, and turns on and audible alarm signal, when the blower continues to operate, the residual gas was purged of combustible furnace, after 20 to 30 seconds purge, automatically cut off the blower and various auxiliary power boiler stop running.) by the flame monitoring and control device component.
10 tons of horizontal gas oil or fired wet back hot water boiler safety features Henan party nearly 10 tons of gas hot water boiler can be divided according to the type of gas hot water boiler WNS and SZS gas hot water boiler, meaning both what is it? WNS means is a horizontal-type combustion chamber burner, meaning that double drum SZS vertical type burning furnace chamber, although the two different processes of different structures, but the fuel and the safety device are the same. This chapter focuses to introduce safety protection system of the two kinds of boiler: 1, interlock protection system ① As the two kinds of dual-use oil and gas boilers are in this together computing, once the fuel or air pressure below the minimum set when the standard, it will automatically cut off the fuel supply ② cold water delivery device event of a failure, will automatically cut off the fuel supply ③ water temperature is higher than the highest temperature setting, will automatically cut off the fuel supply 2, the most dangerous place is the ignition system boiler system , because many of these conditions could not be controlled once the ignition, so the first firing of the furnace should be purged to avoid residual combustible gas combustion furnace, after the purge, ignite pilot fuel (oil or gas) flame monitor reflects the flame existence, and it continues to burn about 10s. After 10s, the main fuel valve (oil or gas) driven i.e., ignite the main burner. If the normal main burner combustion, the ignition system is automatically shut down. 3, turn off the boiler system we know if it is to continue to provide fuel to the furnace in the flame will cause serious consequences of an explosion, this one so fast Henan party made a special detection device, or burn when the ignition fails halfway flameout, general in the 5S (ignition) or the 10s (runtime) off oil, gas solenoid valve, with sound and light alarm signal. 4, via the feedwater system to a steam cycle water injection drum seat, gall direct flame furnace, the flame furnace heat absorption, the heat absorption of smoke tube furnace high temperature flue gas discharged water, boiler water becomes progressively heated steam, by after separation water separation means leads from the main steam valve. Henan party fast as a professional gas boiler manufacturer, has 70 years of design and manufacturing experience, customers throughout the country, the most recent of several large cooperative enterprises and 10 tons of gas hot water boiler, Zhengzhou University, Zhengzhou Yutong Bus with 10 tons of gas hot water boiler, Gongyi aluminum plant with 10 tons of gas steam boiler, your trust is fast Henan party's power in the service of idealism Henan party fast, quality-oriented principle never live up to your commitment to your trust!
Inner Mongolia Autonomous Region Development and Reform Commission issued a notice publicity Inner Mongolia clean heating in winter embodiment (hereinafter referred to as "Notice"), "notice" mentioned that in 2019 the region to achieve clean heating rate of 50% in 2021 to reach 705; urban built New forbidden zone 35 tons of steam / hour and below the coal-fired boilers, which Hohhot, Baotou, Wuhai city urban area will phase out 35 tons of steam / hour and below the coal-fired boilers, all new buildings to achieve clean heating.
The region's total heating area of about one billion square meters of urban heating an area of about 750 million square meters, of which: decentralized heating an area of about 090 million square meters; central heating an area of about 660 million square meters, heating rural area of about 250 million square meters, of which central heating an area of about 027 million square meters, the rest are dispersed heating.
Urban areas mainly in the CHP and district heating central heating boiler room mainly to gas, industrial waste heat, wind power, solar and other energy sources to supplement heating. Rural areas with decentralized heating the main heating source mainly scattered coal-fired boilers, conventional coal-fired furnace or straw.
Urban district heating cogeneration accounted for 51.5%, the proportion of area of 43.6% heating boiler, gas heating accounted for 4.5%, the proportion of the heat pump in other ways, electric heating and the like about 0.4%.
To clean as the goal, in ensuring the safety of people's livelihood heating premise, overall thermodynamic equilibrium between supply and demand, either alone or using a combination of various cleaning heating mode, alternative urban area and would like to keep burning coal for heating casual, less warm air pollutants areas emission. Adhere to safety bottom line, build a reasonable size, safety and reliability of heat supply systems.
2, according to local conditions, the residents can afford. Based on natural resources, economic strength, infrastructure around such as regulation and install air pollution control requirements, scientific assessment, depending on the region to its own characteristics, full old people's consumption capacity, adhere to both energy security and clean development, should power the electricity, should be coal is coal, the gas should be air, clean heating strategy adopted XI, to promote its low cost and low pollutant emission cleaning combination heating under the same conditions.
Considering the urgency of the air pollution control, affordability, work to promote the difficulty and other factors, co-ordinate the work of promoting cleaner heating city, county and urban-rural.