oil fired industrial condensing steam boiler
What are the precautions in the loading and installation of gas-fired fired industrial condensing steam boilers?
Gas-fired steam boilers are a very wide range of special equipments, widely used in food, chemical, paper, textile, construction and other industries. In the process of loading and installing a gas steam boiler, some problems must be paid attention, otherwise it may cause a certain degree of economic loss.
1. Pay attention to the following matters during the loading and unloading and handling of gas-fired boilers: the lifting capacity of the lifting equipment should match the weight of the lifting boiler. The lifting lug on the boiler with the lifting lugs that cannot be used for lifting can not be used for lifting. The length of the steel cord should be reasonably selected to avoid the scratching of the furnace due to the improper length of the steel cord. The boiler must be protected from any damage during handling and handling.
2. Reserves for maintenance space When installing boilers, ensure that there is sufficient maintenance space around the boiler.
3. Setting and precautions for the base and base of the gas steam boiler The boiler body must be installed on the basis of 100-150mm above the floor of the boiler room. It must be confirmed with the technical personnel of the boiler manufacturing company in advance and constructed according to the basic drawings. The anchor bolts must be reserved on the foundation. The foundation shall be capable of withstanding the maximum weight of the boiler and the amount of water it holds. When installing the base, you must first position it. After positioning, adjust to the same length of the two diagonals of the base, and then tighten all the fixing bolts. The installation of the base is carried out with reference to the reference line.
4, general precautions Be careful not to tilt and impact the boiler and accessories too much. No combustibles can be placed around the boiler. Do not use oil and water to smother the boiler. The boiler should normally be installed in a separate boiler room. The new gas-fired boiler room should not be connected to the house. The boiler room shall not be connected to Class A, Class B and Category C fire hazard rooms using flammable liquids. If connected to other production plants, the application firewall is separated.
5. The fire resistance grade and fire protection requirements of the boiler house building shall comply with the requirements of the Code for Fire Protection of Building Design and the Code for Fire Protection Design of High-rise Civil Buildings. The ground of the gas steam boiler room should be flat, non-flammable, no water accumulation, and the foundation load should meet the requirements. The power supply voltage of the gas steam boiler room should be stable to avoid causing the electrical components to burn out. If the voltage is unstable, it is recommended to install a voltage regulator. Ventilation equipment should be installed in the boiler room, and the boiler should be kept at room temperature below 50 °.
Water Tube Oil Gas Fired Boiler is D Type in which water circulates in tubes heated externally by the fire. Fuel is burned inside the furnace, creating hot gas which heats water in the steam-generating tubes. D Type Water Tube Oil Gas Fired Boiler in ZBG is designed with a large steam drum at the top, vertically connected to a smaller water drum (or “mud drum”) at the bottom, via multiple steam-generating tubes which carry feed water (providing the main heat transfer surfaces for the production of steam). These are surrounded by walls made up of larger water-filled tubes, named membrane water wall, and all of them form the boiler.
Gas Fired Steam Boilers are not covered by the rule:
Gas fired boilers (a boiler that primarily burns gas is still considered a gas-fired boiler even if it also burns oil or other liquid fuel during periods of gas curtailment, gas supply interruption, startups, or for periodic testing not to exceed 48 hours during any calendar year)
The use of central heating hot water boiler is the best choice for winter heating in northern China. Shanxi Province is located in Chang Darrow Heating Co., Ltd. mainly provides heating and post-service maintenance of heating equipment, heating clients involved in enterprises and institutions, office buildings, residential housing and a variety of commercial and other entertainment venues. With the wide blue sky covered Battle of the project, China's gradual increase in the proportion of heating for cleaning, heating, Ltd. Dalong Chang respond positively to the call of national policy, high pollution intensity wishing previously used, low thermal efficiency of coal-fired boiler to replace the traditional use hot water boiler clean fuel. After comparing many boiler manufacturers, choosing the optimal selection, determined and professional cooperation parties do fast boiler fuel boiler cleaning equipment. Providing a fast side 35 MW gas tube hot water boiler (SZS35-1.6-Y.Q) according to their actual needs.