5th coal fired steam boiler for brewing
6 tons gas 5th coal fired steam boiler for brewing steam pressure adjusting a boiler operation, must frequently monitor the pressure gauge indicated. To maintain stable steam pressure, boiler pressure must not exceed the design pressure. Second, increasing boiler load: Steam pressure decreased boiler load is increased, if the level is high at this time, the amount of water should be reduced to a water supply or suspend, the amount of coal and increase the air volume. Gradually increase the amount of water at the same time to strengthen the burning, keep the steam pressure and the water level is normal. Third, the boiler load reduction: the vapor pressure rises to reduce boiler load, if the level is high at this time, the amount of coal should be reduced and the air volume, reduced combustion. Then the appropriate water reduction or suspension of water supply to the water vapor pressure and stability in the nominal range. Then press the normal combustion and the amount of feed water 8 to adjust. If the actual water level within the boiler is low, to increase the amount of water should, until the water level returns to normal after the combustion and needs to be adjusted according to the water vapor pressure and load changes.
Shutdown four tons of gas boiler 5th coal fired steam boiler for brewing shutdown and maintenance of fire into pressure shutdown, normal shutdown, emergency shutdown. A pressure fire fire shutdown shutdown pressure applied to temporarily stop the supply of steam, the boiler is shutdown pressure hot standby state. 1, before the pressure reduction appropriately to fire the boiler load, and according to the length of the seam thicker shutdown time, (up to 200mm) to accelerate the speed of the grate, the grate is stopped when rotated about 1.5 meters from the coal seam to the shutter. 2, stop blowers, blower suitably adjusted flap subsections, relying on a lean-burn natural ventilation is maintained. 3, the sewage, to allow the water level in the boiler water level. 4, Yang fire regularly, to prevent rotation of the furnace grate extinguish the fire bed. Young fire first before sewage water, then rinse water level gauge. II. Normal shutdown Normal shutdown for heating period ends, boiler pour fire into the buck repair or maintenance. 1, make a record before shutdown problems in operation, so that after the shutdown process. 2, the coal bucket coal memory runs out, the amount of toner to reduce the wind. 3. Stop the blower, draft fan stop and then the opened door grate ash. 4, after the steam supply is stopped out, the boiler to the boiler water to maintain a high level. 5, close the main steam valve, if the pressure rises to open the air exhaust valve suitable pressure relief. 6, stop the water supply to the boiler and economizer attention to monitoring changes in water temperature, open return pipe if necessary. 7, 4 to 6 hours after the furnace fire bed down exhausted, continued rotation of the cooling grate. Throughout the boiler throttle, the door should be kept closed. Allowed to naturally cool. 8, appropriate to open the pump, the boiler water and sewage. When the pressure drops to zero, open the air valve. 9, when the boiler water temperature is below 70 ℃, boiler water can be exhausted. Shutdown is complete. 10, less than 24 hours during shutdown. Avoid Shutdown cooling process, step-down too fast. Third, emergency shutdown emergency shutdown applies to the boiler accident, g combustion equipment damage, furnace or boiler structure collapsed wall is red-hot, a serious threat to the safe operation of the boiler when; h boiler pressure parts found serious distortion, leakage. when i found flue gas explosion or secondary combustion, boiler and seriously endanger the safety of operating personnel;; when endanger the safety of operation.. the safe operation of the boiler j endanger other unusual circumstances when. 2, the emergency shutdown procedures to immediately stop a blowing coal and reduce the wind; B rotates quickly grate, the pour slag pit coal or sand, wet ash coal burning fire to extinguish. , but not to the firebox water;. c boiler air valve, the relief valve opens quickly exhaust the steam pressure is reduced;. d after the fire goes out, stopping fan, opening the ash door and door, promote air circulation accelerated cooling; 3, emergency shutdown Notes a. when an accident and emergency shutdown due to lack of water, boiler feed water is strictly prohibited to, and shall not be such as to open the air valve or exhaust valve work on preventing boiler from sudden changes in temperature or pressure to expand accidents;. b when filled with water due to an accident and emergency shutdown, should immediately stop the water supply, reduce combustion, open the drain valve and drain, due to lower the water level, while opening the main steam pipe, the sub-cylinder and steam traps mother tube, water and prevent steam pipe with a large number of water hammer occurs. c. emergency shutdown operation to ensure the safety of the main event of an accident to calmly deal with, timely reporting, and make relevant records in the "log table boiler." d. Whether shutdown any case, we must maintain timely contact with steam departments.
ZG Boiler can supply oil & gas fired 5th coal fired steam boiler for brewing, coal fired steam boiler, biomass fired steam boiler, CFB steam boiler, waste heat steam boiler to paper mill. However, biomass fired steam boiler is the most suitable one for paper mill.
New R & D building fast-party group, is a technology demonstration, research and development as an integrated office building. On the first floor exhibition hall design is simple and modern technology, integration of human-computer interaction, virtual reality, projection, graphic panels, simulation models and other advanced means of interactive multimedia display a variety of boiler technology, creating a precedent for the domestic boiler industry technology show. 360 holographic ---- wing tube interactive rejection screen technology - condensing technology Slide TV - premix --FGR intelligent human-computer interaction technology modeling techniques - Remote monitoring