2 ton steam gas fired low nitrogen condensing boiler for sugar mill
Water wall 2 ton steam fired low nitrogen condensing boiler for sugar mill tube leak or burst phenomenon how to do 1, the normal water flow is not greater than the steam flow. 2, the furnace pressure transient and unstable prejudiced. 3, tube leak detection alarm device. 4, the furnace may not tight at the outward discharge gas and water vapor, and a significant leakage sound. 5, the main steam pressure drop. 6, boiler combustion dark flame instability caused by severe boiler fire. 7, when the induced draft fan is automatically cast, abnormal static vane opening is increased, the current increases. 1 reason, the presence of water wall tube material defects or post-production, the installation of the damaged pipe, poor welding quality. 2, the inner tube fouling overtemperature. 3, the inner tube corrosion. 4, water wall wear. 5, the long-term high load operation, furnace coking, coal sulfur corrosion caused by high temperature water wall. 6, improper combustion, flame deflection. 7, in the possession of bad foreign body, the water cycle. 8, the wall of the long-term over-temperature operation. 9, the temperature difference between waterwall tubes, mechanical stress crack. 10, the normal exit or drain sootblower steam punctured tube. 11, smashed chunks of coke furnace water wall tube or serious explosion occurred, resulting in water wall tube suffered external damage. 12, boiler overpressure long run. 13, the boiler starts to heat up, step-up too fast. 1 process, the leakage should try waterwall tubes outage. The leakage is not serious, while still capable of maintaining operation, note that each of the automatic operation when the device, if not normal, it is cut immediately to the manual, if necessary, may be down, down-load operation. Closely monitor the development trend of damaged parts, good accident anticipation, application shutdown as soon as possible. 2, if the leak is serious, the bursting point temperature after a sharp rise in quality work, leading to serious over-temperature wall, unable to maintain the normal operation of the boiler or threaten the safety equipment, emergency shutdown provision should be processed, when the steam temperature to protect the action value, the protection does not move, should immediately hand MFT. 3, note that the operation of the electrostatic precipitator, to strengthen the inspection checks, to prevent fouling, and the electrodes ESP hopper, pipes and the like plugging air preheater ash. 4, after the shutdown, should retain ID fan, the furnace pressure is maintained constant, there is no discharge to be stopped after soda ID fan.
Our other fast 2 ton steam fired low nitrogen condensing boiler for sugar mill in the boiler industry strength already heard, through cooperation proves that our choice is correct. This water-tube boilers installed very quickly, basically no delay our production process, bring benefits to the enterprise. --customer feedback
How to use gas-fired 2 ton steam fired low nitrogen condensing boiler for sugar mill gas boiler includes a gas water boiler, gas hot water boiler, gas steam boilers, gas hot water boiler which is also known as gas heating boilers and gas boilers bath, as the name suggests refers to the gas boiler fuel gas boiler, gas boiler and oil-fired boiler, electric boiler comparison economy, so most people have opted for a steam boiler equipment gas-fired boiler, heating, bath with. 1, boiler water, softening the first, but also to clean the water quality can not be an impurity. 2, gas boiler before the fire, you want to view the valve pipes, steam pipes, water gauge, pressure gauge and drain valve and so on, whether it is intact, whether the normal use. 3 and can not be conditioned to avoid rendering problems. If the gauge to reach the promised 80% working pressure, to avoid excessive pressure. 4, the water table in a glass tube, which should consolidate outer shield, but also to clean and tidy. How should the functioning of the water table at any time of the investigation, if any anomalies should be handled immediately. 5, when the gas boiler shutdown urgency, you want to cancel burning, then closed throttle, then open the door and release valve, the order can not be inverted. 6, when the pressure rises quickly, when and beyond promised to work pressure or boiler annex presents the phenomenon of failure, or a furnace, ducts appear deformed, when leaking air leakage, urgency should be shutdown immediately.
Combustion characteristics and operation of steam 2 ton steam fired low nitrogen condensing boiler for sugar mill steam for steam boilers everyone know how much will the following to let everyone have a preliminary understanding of the steam boiler by two aspects, but also hope to give a friend wanted to buy a steam boiler of some help. Chain-type layer is generally fixed combustible fuel steam boiler chain grate or a grate (the traveling), it is fixed only for small coal-fired boilers. The most commonly used medium-sized coal-fired boilers or for chain grate, as the chain travels will gradually sent to the tail of the coal grate in the process of moving complete fuel combustion tube from the inlet to the lower part of the grate grate internal supplemental air required for combustion, ignition top-down, no ventilation grate uneven seam and around the relative movement, through non-flammable. After heating area of the heating flue gas temperature of the working fluid designed to flow through the same furnace hot flue gas and heating surface arranged in the other exhaust flue boiler. Incidental chain grate type, scale type, beams, and other means, the current domestic applications mainly for small and medium-sized joint type and scale type chain grate, generally large chain grate beam type. Former steam boiler steam boiler system to start all waterproof steam cylinder valve open, let go condensate. The inlet steam valve slightly open, to warm up the cylinder, drain cocks to be out after closing the steam, drain cocks. The steam valve was then opened progressively larger until drainage tank vent cock and water out there, and closed vent cock drain cocks. Turn on the water supply valve to the boiler feed water. Steam boiler in operation if there is gas in timely attention tank, water tank periodically open the air discharge valve, in order to avoid air resistance tank, the influent. Pump flow regulator bypass should be adjusted to achieve the degree of opening of the valve, and not with a method of adjusting the outlet valve is adjusted. At the rated discharge pressure of the pump, which inlet pressure should not exceed a predetermined value. Inlet and exhaust pressure difference should be maintained within a predetermined range. Steam boiler steam valve should be shut down first, then turn off the water valve and turn on the water valve is open, then turn on the water faucet open the lower part of the tank and cylinder, the cylinder water drain. Of steam cylinder reciprocating pump, which cylinder two stroke difference should not exceed 5% of rated travel.