Food industrial gas fired 2 ton per hour steam boiler
Electric boiler supplying domestic matters need to pay attention what? 1, electric boiler carefully check each system before opening oven parts electric boiler, focused on checking the three security controls pressure gauge, safety valve, gas pipe fittings, water level is normal, everything is correct, put on compliance clothing to continue to work. Electric food industrial fired 2 ton per hour steam boiler 2, please do one-handed operation when the water in the electric boiler, water regulatory action is single-handedly opened the door in one hand and a water injector steam valve, when the water column to a predetermined level, the first valving (valving time face not being on the water, to prevent splash injuries face) and then turn off the water gate, electric boilers provide domestic water to be alert order can not be reversed. When electric boiler work, surrounding someone must guard the moment the water level and pressure gauges, there can be no neglect of duty, to adjust work schedules when working at night, night shift work, be sure to have a good rest during the day, not at night when this work I would doze off, because if there is any carelessness, accidents will happen. Points to note what? 4, electric boilers night to the boiler daily sewage treatment, water table should clean up once every night. For motor and other mechanical equipment have always been its inspection, if any abnormal findings, the investigation must be immediate. Weekly safety valve should be checked whether it is safe.
What is the reason for food industrial fired 2 ton per hour steam boiler explosion? Boiler itself is flawed: the pressure component aging, strength weakened, or leakage, corrosion, deformation, scaling and other defects can not be timely maintenance and eliminate hidden dangers, but let the disease run with the boiler and so on. Fuel gas boiler is not only fuel but also refers to the gas boiler. Previously no such dual-fuel boiler, burner because either fuel or gas, no dual fuel burners. With the rapid development of the world energy equipment, some European countries begin production and sales of fuel gas burner, dual fuel burner and boiler combination of organic birth of a new breed of boiler - fuel gas-fired boiler. Therefore, we must carry out regular inspection of boilers in accordance with national requirements. 3. poor management, furnace workers irresponsible or low levels, lead to misuse. Therefore, furnace workers must obtain a certificate as required. None of the above is the main reason for the actual boiler explosion. In actual operation, the most common situation is that the boiler add cold water and drying, which is very dangerous. Biomass boiler is a kind of boiler to biomass energy as a boiler fuel called biomass boilers, steam boilers into biomass, biomass hot water boiler, biomass stove, biomass thermal oil heaters, vertical raw biomass boilers, biomass boilers and other horizontal. This is also the operators need the most important thing vigilance. There may be debris blocking the pressure cooker vent, causing the pot to continue to increase pressure, excess pressure can not be discharged to reach the pot of strength, can withstand the pressure will naturally explode, of course, does not rule out the cause of pan itself. Substandard quality, tank leaks, inadequate exhaust usually cause an explosion. Therefore, before use, carefully check the vent is smooth, not to violate the specification and taboos, without any danger.
Gas boiler installation and preparation requirements of (a) the preparatory work before the installation of a boiler installation must be installed by the unit has installed a license .. The installer must be familiar with "Boiler Safety Technology Supervision", and carefully read the installation instructions and other random technical documents. 2, a mounting position: 1) as close as possible to install a boiler steam, hot site, to facilitate shortening the hot water and steam pipes, reducing capital costs, reducing the pipeline heat loss. The installation site should be water supply, sewage convenience. Burning light diesel oil, heavy oil residue and the boiler must be closer to the oil reservoir; burning natural gas, town gas boiler must be easy to close the gas source. 2) boiler room layout should follow the "Boiler Safety Technology Supervision" relevant provisions "boiler room", to be well-lit, well-ventilated, no ground water, ease of operation and maintenance, boiler room must be equipped with at least two fire extinguishers 1211. 3) Check the boiler foundation, prepare the boiler in place. 3, equipment acceptance: acceptance by conduct an inventory purchase contract or supply list. 4, lifting large boiler: not less than 1.1 times the lifting equipment of large weight of the boiler, two lugs for the lifting jack top or at the bottom edge away slowly, not to any other parts of the lifting or addendum to avoid damage to the boiler. (Ii) installation requirements: 1, the main steam line installation requires the main steam lead pipe height is generally greater than 0.5 m, the bending radius should be greater than or equal to 5 times the diameter of the pipe, the pipe should be installed at the lowest trap, preventing water pipe, It should be a main steam pipe insulation. 2, a main return pipe installation requirements should the main return pipe elbow minimize installation, to facilitate the mounting operation of the valve, piping should be insulated. 3, the hydrostatic testing relief valve, the safety valve should be installed in the exhaust pipe, the exhaust pipe connected to the straight pipe outdoor safety. 4, should be connected to a sewage outfall tank or other security, the pipe should be secured to prevent shifting or counter scald accidents blowdown. 5, railings, stairs (with large oven) after the positioning by drawing the boiler installation. 6, water table must be installed to the lighting device, easy to install or inspection.
In the transformation process, side by rapid technical engineers FGR advanced combustion technologies, the use of flue gas recirculation and the outer loop is provided, withdrawing part of flue mixed with the combustion air, and then into the furnace through a burner, not directly part in the combustion, by reducing the effect of the combustion flame temperature to reduce the temperature and oxygen concentration, to achieve the purpose of reducing NOx generation. For now, for a large volume of gas boilers, low compared to the overall transformation of nitrogen to replace the boiler equipment will save a lot of costs. Fast boiler has a boiler in research and technology low nitrogen aspects of considerable industry experience, successful completion of the reconstruction project Dingzhou low nitrogen Erie boiler, significant cost savings for businesses.