automatic oil steam boiler
Fast boiler is a very trustworthy business, whether it is the beginning of cooperation or boiler put into operation, such as a party soon have maintained cooperative attitude, patience, careful. To ensure long-term stability of the latter part of the boiler operation, fast boiler technician fireman's gave us a free people to do the training, precautions and reduce the accident rate method full guidance boiler operation. --customer feedback
ZG Boiler is the automatic steam boiler manufacturer and we can design and manufacture all types boilers to meet customers’ demand. We can supply customers oil fired steam boiler, gas fired steam boiler, biomass fired steam boiler, coal fired steam boiler, CFB steam boiler for textile industry. Textile industry is suffering from energy crisis specially gas, low pressure and high demand among residence in winter causes complete breakdown. So, it’s high requirement to shift on alternate energy resources e.g. Coal.
Combustion gas treatment unit and a fault, gas boiler burner ignition misfire rod reasons: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Measures following five: Clear, renewal, adjust the distance, change and switching transformer. Second, gas boiler, but spark ignition rods misfire reasons: 1, the cyclone disc space ventilation is blocked carbon, poor ventilation. 2, dirty oil nozzle clogging or wear. 3, the throttle angle is set too small. 4, the firing bar from the leading edge from the oil nozzle tip inappropriate (too protruding or retracted) 5, the first solenoid valve is an oil debris blocking gun (gun small kerosene). 6, oily or too viscous to flow easily clogged or the oil filtration system the valve is not opened, so that insufficient suction pump, oil pressure. 7, the filter pump itself blocked. 8, the oil more water (boiling abnormal noise within the heater). Measures are: Clear; first wash, such as not renewed; turndown test; adjusting the distance (in 3 ~ 4mm as well); Remove cleaning (cleaning the parts diesel); Check tubing and oil filters, insulation equipment ; remove peripheral screw pump, carefully remove the cover inside out oil network, with immersion oil; renewal of the test oil. Third, when the gas boiler and turn the fire a small fire normal, off, or flashing instability reasons: 1, the air volume damper setting fire too. 2, oil fires micro switch valve (damper outermost that group) inappropriate setting (set throttle air flow rate is greater than the fire). 3, oleaginous easy to spray viscosity is too high (heavy). 4, and the nozzle plate spacing cyclone inappropriate. 5, fire nozzle worn or dirty. 6, the preliminary fuel tank temperature is too high, so that the steam not smooth oil pump oil feed. 7, fuel oil boiler water. Action: Test gradually reduced; heating temperature; adjusting the distance (between 0 ~ 10mm); clean or replace; approximately set to about 50 deg.] C; or drain oil change. Fourth, the noise increases gas boiler burner reasons: 1, cut-off valve is closed or the passage into the fuel shortage, an oil filter blockage. 2, the oil inlet temperature is low, the oil viscosity is too high or the temperature is too high the pump inlet. 3, oil pump failure. 4, fan motor bearing damage. 5, dirty fan impeller. Processing methods: ① the oil line check valve is open, if the oil filter is working properly, the filter cleaning pump itself. ② heating oil or reduce the oil temperature. ③ Replace the oil pump. ④ replace motor or bearings. ⑤ cleaning fan wheel.
Our boiler is mainly about horizontal automatic steam boiler and industrial hot water boiler, according to different fuel, the suitable boiler have biomass boiler, coal boiler, gas boiler, oil boiler. In most plant and factory, 1-35 ton steam boilers and hot water boilers is enough.