8 Tonh Chain Grate Biomass Coal Fired Steam Boiler
Steam boiler accident type and processing method, and use common sense safety boiler 8 tonh chain grate biomass coal fired steam boiler accident type and processing method, overpressure accident 1 boiler, boiler overpressure phenomenon of (1) a sharp rise in steam pressure, exceeds the allowable working pressure gauge pointer over " red line "safety valve after the pressure is still elevated. (2) the operation of the device is the interlock overpressure protection, should send overpressure alarm signal, stops the air blowing, the wind, coal. (3) steam temperature and steam flow rate reduction increases. 2, to treat boiler overpressure (1) weakened rapidly burning, manually open the valve or bleed valve. (2) increase the water supply, while the lower reinforcing blowdown drum (It should be noted at this time to maintain the normal water level of the boiler), in order to reduce the temperature of the boiler water, thereby reducing the pressure in the boiler drum. (3) as a safety valve malfunction or all of the pressure gauge damage, emergency shutdown, safety valves and pressure gauges are to be repaired after the boost operation. When endanger the safe operation of (4) Boiler excessive pressure, blood pressure should take measures, but too fast buck is strictly prohibited. (5) boiler overpressure eliminate serious, to the shutdown of the boiler internal and external inspection, to eliminate the overpressure caused by deformation, leakage and other safety accessories and maintenance unqualified. Second, an accident boiler water, boiler water shortage (1) below the minimum safe water level line, or can not see the water level, the water level gauge glass (plate) as a white. (2) as a full-color water level gauge vapor instruction color. Low water level alarm signal (3) water level alarm occurs. (4) low water interlocking means, the water level should be below a prescribed value blower, Fan, grate reduction motor stops running. (5) a sharp rise in the superheater steam temperature, higher than the outlet steam temperature. (6) boiler exhaust gas temperature rises. (7) the water flow is less than the steam flow, causing Should the water tube due to tube cracking or economizer, an opposite phenomenon occurs. (8) When a serious water shortage, can smell the burnt smell. (9) When a serious shortage, the door can be seen from the red-hot waterwall tubes. (10) a serious water shortage, the furnace tube may rupture, then can hear the explosions, smoke and steam from the door, watching spray the fire door. 2, boiler water treatment (1) through the "waters", sentenced to severe water shortages, emergency shutdown must be prohibited blind to the boiler feed water. (2) through the "waters" sentenced to a slight lack of water, it should reduce fuel blast, the wind, and slowly feed water. Third, full water boiler 1 accident phenomenon (1) above the maximum allowable water level line, or can not see the water level, the water level gauge glass (plate) dark color boiler filled with water. (2) all of the water phase as a color level gauge indication color. High-water alarm signal (3) water level alarm occurs. (4) decreased superheated steam temperature. (5) water flow is not normally greater than the steam flow. (6) water in a large number of sub-cylinder, severe trap operation. (7) with a large amount of water steam severe, increased salinity, water hammer occurs in the sound of the steam pipe, the steam connection flange outwardly dripping take place. 2, boiler full of water treatment rinse water table, determined to be minor or serious full of water full of water. Method: Close water table, the water pipe connected cock, then open drain cocks As can be seen from the decreased water level, indicating a slight full of water, the water supply is stopped, the drain valve open, put to the normal water level. Such as severe filled with water due to take emergency shutdown measures.
The reason gas 8 tonh chain grate biomass coal fired steam boiler flame of abnormal phenomena and processing method. Flameout for the following reasons: 1. Auxiliary trip or power interruption. 2. boiler combustion instability. 3. When the load is too low, due to the sudden drop in load, ignition energy mill will be lost or the combustion is automatically stopped. 4. mutation coal, low volatile or low calorific value. Fuel gas boiler is not only fuel but also refers to the gas boiler. Previously no such dual-fuel boiler, burner because either fuel or gas, no dual fuel burners. With the rapid development of the world energy equipment, some European countries begin production and sales of fuel gas burner, dual fuel burner and boiler combination of organic birth of a new breed of boiler - fuel gas-fired boiler. 5, the automatic combustion flame detectors or failure resulting in failure to trip mill. 6. The furnace wall or squib serious improper boiler soot-blowing operation, a large amount of steam into the combustion chamber. 7, coal pulverizing system, fuel system failure, resulting in a substantial amount of fuel reduction or interruption. A large amount of water or impurities in the fuel oil gun clogging, or atomized vapor pressure is too low. Second, the phenomenon: 1, furnace pressure was significantly higher, flameless furnace flame monitoring CRT display. Pit of fire no fire. BTG MFT alarm window alarm indicator lights. 2. The unit load is reduced, steam flow drops rapidly, and the temperature of each section of the working medium vapor pressure decrease, a sharp increase in oxygen index. Steam boiler is an energy conversion device, the energy input to the boiler fuel chemical energy, electrical energy, thermal energy and other forms of high temperature flue gas, and after converting the boiler, the steam output having a certain outside thermal energy, high-temperature hot water or an organic carrier. 3. Treatment: 1. If you refuse to run MFT protection, emergency stop should be handled according to the situation and stop the supply of fuel. 2.2. Identify the cause of stalling, and try to eliminate it. Conduct a comprehensive inspection of the boiler, and to confirm proper before the device is restarted.
As a leader in the fast side condensing gas boiler, in recent years, provide a clean boiler to Beijing multiple office units, was well received. I units through the preliminary investigation and contrast, select fast boiler, it turns out, party fast product does have quite a good cleaning environmental performance, in line with the Beijing municipal government requirements for air pollution emissions, the use of very at ease. --customer feedback
Steam boiler wear and electric test pump DSY Henan fast boiler's 8 tonh chain grate biomass coal fired steam boiler small series with you about wear and DSY electric test pump wear is one common steam boiler heating surface defects, boiler heating surface is arranged in the boiler the furnace and the flue, in particular a heating surface in the steam boiler flue vertical tail, by the long brush smoke, soot in the flue gas so that the wall heating surface wear thinned, so that heat from the flue gas scouring wall ironed a phenomenon known as wear and tear. Flow rate, the concentration of soot in the flue gas and the hardness of the tube bundle arrangement such factors as the wear rate of the heating surface of the steam boiler and the flue gas is related to the flow rate of flue gas wherein the greatest impact on the wear of the heating surface. Experimentally measured, proportional to the cube of the wear rate of the heating surface tubes and the flue gas velocity, it is necessary to effectively control the flow rate of flue gas. Leakage of the furnace wall, a partial wall flue ash, convection heating surface partially severe slagging will cause a partial flue gas velocity is too large, so that the heating surface tubes local wear increased, further, when the soot blowers work failure, high pressure steam steam heating surface tube will blow erosion, so that the wall thinning. Heating surface tubes often wear area is: cool ash, burner, bullnose, and close to Manhole sootblowing waterwall tube aperture; a lower portion of the flue gas before the steering tube heating surface vertical chamber; vertical tail horizontal heating surface portion of the second row of three tubes of the flue, the lower portion of the second three tubes, tube support edge portion of the clip, close to the furnace wall side of the rows of tubes and the individual tubes and the like projecting tube rows. Heating surface wear reduction methods are: to reduce boiler load, reducing flue gas velocity; burning coal quality, reducing the content of fly ash in the boiler flue gas steam; change bundle arrangement, a staggered arrangement to the line arrangement; Clear slagging and blocking flue ash, flue gas flow area increases; leakage reduction furnace wall; the installation of a shoe or the spoiler like. Abrasion test on the electric pump plunger hole set DSY electric test checking pump plunger sleeve (1) Check the DSY type. If the pump DSY electric test has passed the test on sealing ST-990 or the tester 3,375,375, the plunger sleeve is available. If the leakage is large, it is necessary to replace the plunger and plunger sleeve. (2) using the burr, coke, and high-expansion magnifying glass to check the amount of deformation of the bore. When the metering orifice is damaged, DSY i.e. electric test pump is not working properly. Do not attempt to clean with a wire, plug, etc., should be cleaned with a solvent. (3) Check the fuel oil channel as well as choking loose plunger sleeve for cracks. (4) Check DSY electric test pump plunger sleeve surface endless belt black area and Degree how damage flatness. Some electric test pump head end of the barrel nozzle sump has been canceled. Henan is committed to fast boiler steam boiler manufacturing, product quality, reasonable prices and widespread industry praise, if you have any needs, please contact us!