hot water boiler with gas or oil
Furnace pulverized coal fired boiler is smaller than you: Today saw a piece of content, said: with the same capacity, oil-fired boiler furnace is smaller than pulverized coal. why? The following reasons: the size of the furnace volume, in the boiler capacity is determined, depending on the size of the volume of heat load. Volumetric heat load size is mainly determined by the type of fuel. After the fuel into the furnace, it will take some time to burn. Typically all the required fuel burn before leaving the furnace, the pulverized coal burnout is obviously longer than oil, i.e. coal flame longer than oil. To ensure long-term safe operation of the boiler, not only to prevent the boiler slag, and flue gas at the furnace exit is low to make the temperature at the start of the deformation ratio of ash flue gas temperature 50 ~ 100 ℃, at the outlet of the furnace and to prevent subsequent convection slagging heating surface. In many coal ash content, coal-fired furnace to control the furnace exit gas temperature typically of 1050 ~ 1100 ℃. The fuel oil furnace because very little ash, furnace slag is not dangerous, do not consider the problem of slagging furnace slag discharge outlet pipe, so the furnace exit gas temperature can be higher. For the above two reasons, the volume of the thermal load is higher than Pulverized fuel boiler. Pulverized volumetric heat load is about 145 ~ 185kw / m3, and the volumetric fuel burner heat load of up to 255 ~ 350kw / m3, so the same volume of the furnace fuel burner furnace capacity is relatively small pulverized coal fired. Rinse water gauge oil-fired boiler
Beijing SL Pharmaceutical Co., Ltd. as China's key high-tech enterprises, has great influence in the pharmaceutical industry. In early 2017, two-Heron relevant person in charge to get in touch fast boiler, double-Heron Pharmaceutical according to demand, our company to provide a 1-ton split steam condensing steam boiler, and is responsible for subsequent transportation, installation and commissioning work .
11.Steam exiting the high pressure steam turbine is called cold reheat.
It is reheated in the re-heater and sent back to the second steam turbine. By the time the flue gas exits the boiler most of the energy in the coal will be transferred to the water in the boiler. The hot gases are cleaned up before they are sent to a stack. Feed water is generally supplied by condensed steam from the low pressure steam turbine. Large amounts of cooling water are used to condense this steam into liquid water in the condenser.
When we use the boiler, it is unavoidable to have faults or abnormal phenomena, but in order not to affect the normal use, when the boiler appears problems should be dealt with in a timely manner, then in the face of all kinds of circumstances, how should we deal with it? Share with you some ways to handle exceptions. If only the boiler circulating pump abnormal, such as its current reduced, outlet pump pressure return to zero, which means that the pump is idling non-oil, may be caused by vaporization of oil. Therefore, first of all, Yang should take measures to identify the cause of vaporization; if the filter blockage causes the circulating pump to empty, the by-pass cleaning filter should be opened immediately; such as the new heat transfer fluid containing water or Water-decomposing gas is not excluded in the system, then the open valve should be opened immediately. If the circulating pump pressure is constant, the current increases and the flow rate decreases, the heat transfer fluid is metamorphic and the viscosity is increased, so it should be replaced or regenerated in time. If the gas containing water or decomposing is not excluded from the system due to the new heat conduction fluid, the gas should be discharged immediately by opening the valve. When the current of the circulating pump is lower than the normal value, it shows that the efficiency of the circulating pump is lower and the flow rate is decreased, which may be the fouling blockage of the heating pipeline, and the stainless steel chain should be cleaned. If the pressure difference between the front and back of the filter in the boiler increases and the pressure of the pump inlet drops, the filter may be blocked. The bypass should be opened and the filter should be turned on. Remove cleaning. In addition, the low outlet temperature of the liquid-phase heat carrier furnace and the lack of heat supply are mainly due to the problem of ash accumulation, so soot-blowing should be carried out in time. A more common problem with the boiler's grate is that it is stuck because it is broken or loose after the pin has fallen off; metal inclusions in the coal trap the grate; the grate is arched; and the tip of the slag stopper sinks to jam the grate. In view of this phenomenon, it is necessary to clean up the debris with the plate hand-down converter row, replace the broken furnace platoon and start again, if it is stuck again after the start-up, then check the causes after stopping the rotation and solve the problem in detail. At the same time, it is necessary to adjust the screws on both sides and tighten the grate, if it is still not correct. Often, you need to change the sprocket.