Horizontal Type Gas Fired Steam Boiler for Food Industry
After the gas hot water boiler hot water boiler vaporization emergency 1. Vaporization handler circulating pump stops abnormally pump failure caused by: ① blower stops running immediately. ② immediately open the door, take measures to pressure the fire, lift the chute gate, cutting off the supply of coal grate. ③ In the case of boiler pressure not greater than 0.6MPa (600KPa), the exhaust valve to follow, only a sharp rise in pressure in the boiler deflated, used only relief exceeds 0.9MPa, and the exhaust process to be carried out slowly, prevention boiler due to loss of pressure and more violently again vaporized. ④ close the boiler water, water main gas valve. ⑤ open stop valve recirculation line, to ensure that the water supply pipe velocity convection heating surface (economizer) to prevent re-vaporization of the economizer. ⑥ The operation of the above operation, at the same time to pay the boiler to reduce the boiler water temperature and the furnace pressure. ⑦ After the boiler pressure is normal, i.e., opening the standby circulating pump, into the normal combustion. 2. Treatment failure or sudden loss of power boiler vaporization of power: ① immediately open the door, lift the coal chute slide gate to take pressure fire measures to reduce the oven temperature. ② Grate with the fastest speed in order in the shortest time to fire onto the slag tap. ③ the degree of treatment in the first case. Once a short time can not supply heating network system, antifreeze should take emergency measures. 3. Due to excessive heat boiler boiler vaporization process: ① the immediate closure of the drum, induced draft fan. ② immediately open the door, take measures to pressure the fire, lift the supply of coal chute slide gate, off of coal, while the grate into fast gear. ③ In the case confirmed the presence of water, the boiler can supply water to the boiler body, boiler out of the water while closing the main valve. ④ Open line stop valve recirculation pump to ensure water velocity convection heating surface of the pipe, to prevent the economizer again vaporized. ⑤ Open circulating pump with jog mode, jog each time less than 30 seconds, again less than one minute jog interval. Jog purpose is to reduce the boiler water temperature, while preventing a large amount of steam into the pipeline system. ⑥ back into place after the safety valve, circulating pump running, and then the normal burning stove. 4. Water boiler system run vaporization process due to water loss, loss of pressure caused by: ① immediately closed drum, induced draft fan. ② out of the water while closing the main valve and the boiler circulating pump. ③ take the same measures to cool the furnace tube described above. ④ Open stop valve recirculation line. ⑤ rely exhaust valve until the safety valve back into place. ⑥ until the boiler water temperature drops below 50 ℃, when the temperature of the furnace temperature less number 200 ℃, again within the boiler feed water, water course to be carried out slowly, to prevent harm to the boiler when the temperature is too large. ⑦ After processing leakage fault, the system time to the replenishment, and out of the water boiler always open the valve, and the circulating pump, and then normal combustion.
It is understood that, recently, the ecological environment Department of Henan Province issued the "Henan electricity in 2019 non-standard governance program industry" and six special programs, mainly to further promote the campaign of air pollution control, to ensure that the province's ambient air quality continues to improve. Meanwhile, the "plan" also made clear this year Henan Province industrial air pollution control in key tasks.
The province meet the conditions of steel, coke, cement, carbon (including graphite), flat glass (including electronic glass), aluminum and other six major industries and enterprises, the requirements before the end of this year to complete the mentioned standard treatment, the required limits for reducing pollutant emissions. Carry closed down or banned brick kiln, lime kiln, tunnel kiln, firing kiln and a variety of smelting furnace, roaster and so on nine categories of Kiln, upgrading, restructuring and integration work. Before the end of October this year, all kinds of industrial furnaces to achieve discharge standards.
Before the end of June this year, the province's petrochemical, oil refining, industrial coating, packaging, printing, chemicals, pharmaceuticals and other industrial enterprises, the full completion of volatile organic compounds pollution control; before the end of August, the province's petrochemical, oil refining companies to complete volatile organic compounds depth governance and leak detection and repair of governance; before the end of December, the provincial cities of built-up areas phasing out the open dry-cleaning machine.
Before the end of October this year, in addition to undertaking tasks and will not have the alternative livelihood conditions, the province completed 35 steam tons / h coal-fired boilers and the removal or clean energy transformation, provincial cities and county (city) district built 4 tons of steam and above gas-fired boiler, fuel (including alcohol-based fuel) boiler low nitrogen transformation complete, the provincial municipality to build a biomass boiler area (including biomass power plants) completed the first ultra-low emissions transformation. Before the end of June this year, the completion of the provincial cities to build coal-fired facilities Chaigai all industrial areas.
Water tube boiler for cocoa factory
A 15-ton oil and gas water tube boiler produced by ZG boiler provides steam for cocoa processing. The plant is located in Côte d'Ivoire and requires a steam boiler for production due to the expansion of production.
Gas-fired horizontal type fired steam boiler for food industry equipment maintenance equipment maintenance points 1: 1, or twice a day to clean up slag. 2, washed once or twice a heater dust (ash door with the appliance design) weekly. 3, once or twice a month, or butter oil feeding helical gears and bearings induced draft fan. 4, a monthly injection of butter or oil to the fan motor bearings once or twice. 5, a boiler must be 2-4 times the annual emissions (emissions must promptly after filling water). 6, poor water quality, in use. 2. Before, must soften water. Gas hot water boiler with environmental protection, energy conservation, safety, salient features fully automatic operation, and ease of use. In addition, due to the operation of the economy, government policies to encourage, gas hot water boiler more and more people of all ages. Daily inspection equipment: 1, the fan regularly checks whether there is a feed screw loosening device, whether there is abnormal noise. 2, regular inspection trip tank float valve is normal replenishment, water pressure is normal. Biomass boiler categories: biomass boilers Horizontal, vertical biomass boilers. Biomass gas thermal oil heaters, biomass steam boiler, biomass hot water boiler, biomass oil furnace. 3, if equipped with a pump, replace circulation pump on a regular basis, and check whether the pump is working properly. Function gas boiler the ignition system that ignites the mixture of air and fuel, its main components are: the ignition transformer, the ignition electrode, a high voltage electrical cable fire. A more secure electronic ignition system called ignition pulse, is widely used Zhuoyi energy saving gas boiler manufacturers. Which facilitate saving, can simply press a finger, and safe, does not occur due to unexpected accidents occur flame, once the stall state occurs, the control system can close the solenoid valve, off the gas passage. 4, regular inspection equipment grounding cable is connected correctly. 5, to ensure the normal supply of fuel in the hopper, so as to avoid non-fuel flameout downtime. 6, it should be observed regularly combustion of the fuel in the combustion chamber. Incomplete combustion of fuel, smoke or large block to form sulfur, the sulfur should be promptly removed block and the governor to adjust the feed flow rate ratio of the fan, to achieve the desired combustion.