Burning Coal Steam Boiler
Check Item item hot water boiler hot water boiler comprising a boiler inspection and checking internal use preparations, checking in the furnace and the flue, the boiler attachment check, check automatic control system, the secondary device, check the combustion device, the auxiliary heat check the surface of the hot water boiler must be done before running some tests, these tests are quite a lot of us, it is possible because of our neglect and causing very serious consequences. Therefore, we must forestall, be sure to carefully check the following before the hot water boiler operation. 1, including the use of internal inspection and boiler ready. 2, inspection, and furnace fouling and debris inside the flue in the furnace and flue should be cleaned. Flue duct and damper, the shutter must be complete and compact, flexible switch, opening and closing accurately indicated. 3, check the boiler accessories, check the safety accessory is intact; cock is rotating flexible, easy to use; all kinds of instruments and controls should be complete, good, clean. After passing the examination, should the gauge cocks in working condition. 4, check the automatic control system. 5. Check the accessory device. 6, inspection of the combustion apparatus, the combustion apparatus is intact inspection; mechanical transmission system, coal handling system, the ballast system test switch normally; spring-loaded safety level of a gearbox should be appropriate, well lubricated; coal shutter indicate the correct scale. iron eagle neat, well, turn the ballast plates full, flexible movement. 7, the auxiliary heating surface of the inspection, check the auxiliary device (fan, blower, pump, etc.) are firmly connected coupling; proper belt tension triangle; oil should be good enough; cooling water flow. After passing the examination, installed security guard, respectively, commissioning, and note the current when idling. It is fed out of the hot water boiler heat equivalent to a mass per hour (usually expressed in tons) in water was heated from 20 ℃ and heat output of all vaporized into a burning coal steam boiler water absorbed three expressions, in tons) water from 20 ℃ heated and vaporized into all heat absorbed by the steam boiler it is fed out of the hot water heat equivalent to a mass per hour (i.e. typically kcal / hr (kcal / h), tonnes / hour (t / h ), megawatt (MW). (1) kcal / h is in metric units of expression, which represents the heat of hot water boiler fed out per hour. (2) t t borrowed steamed steam boiler popular argument, ( 3) megawatts (MW) is the international system of units unit of power, the basic unit is W (1MW = 106W). this expression formal documents should be used.
The third reason is that the amount of nitrogen oxide released during operation is very small. Most heating equipment such as ordinary boilers need to use coal materials as raw materials when they are in operation. Materials such as coal generally release a large amount of hazardous air-quality substances when burned. The condensing boiler uses the steam produced by natural gas combustion as the raw material when it is in operation, so the nitrogen oxide content released during the operation is much lower than the prescribed standard. The analysis of the reason for the year-by-year increase in the sales of condensing boilers has come to an end for the time being.
Beijing New Energy Automobile Co., Ltd. is China's first to operate independently and gain new energy automobile production qualification of new energy auto companies, mainly engaged in new energy vehicles and key parts and components research and development, production, sales and service business segments, and the layout intelligent manufacturing, energy management, smart travel, Internet +, and other strategic emerging industries. In the new energy automobile manufacturing process, and a series of paint drying processes can not do without the help of hot water boiler. Due to the company before the device has reached less than the growing production needs, the introduction of the 2017 mid-tail electric company producing heating pressure hot water boiler (CEDR0.7--95 / 70-Ⅱ).
Learning materials heat boiler 1, the boiler is three safety accessories: water gauge, pressure gauge, safety valve. 2, the normal operation of the boiler water level is 0 ± 40mmH2O, the maximum does not exceed 0 ± 80mmH2O, the normal water pressure of 5.5MPa, to allow the fluctuation range of 4.5-6.0MPa, normal pressure boiler feed water temperature should be 105 degrees Celsius. 3, steam flow is not larger than the normal water boiler feedwater flow reasons, the measuring device instrument to do so. 4, the steam flow rate is less than the abnormal overheating damage reasons of water flow, water wall damage, damage to the economizer, the boiler is full of water, measuring device instrument to do so. 5, points on the furnace process CCP washed three times water gauge, pressures of 0.05-0.1MPa, 1.0MPa, 2.8MPa. 6, it is determined whether the normal water table and put into operation to see if the water level fluctuates slightly exemplar. 7, the boiler water pressure test and the test is divided into P overpressure test of two, when the water pressure P test, the boosting speed of not more than 0.35MPa 0.5MPa down rate does not exceed per minute. To the boiler water blowdown 8, the pressure in the boiler shutdown boiler water temperature drops below 80 degrees Celsius. 9, the position of each ordinary pressure test is hydrophobic doors: a door opening, the second door is closed. 10, the boiler-burner with a swirling-type and DC type two. 11, elemental analysis of coal with a composition: C, H, O, N, S, moisture, ash. 12, the main component of the blast furnace gas is: CO.'S time, nitrogen gas, blast furnace gas pressure is lower than 1500Pa, the user must reduce the amount of gas. Fire stop its pressure 1000Pa, working pressure 4000-8000Pa, the upper limit for the dangerous pressure 10000Pa, the lower limit is 2000Pa. 13, the main component of the coke oven gas: CO, nitrogen gas, coke oven gas pressure is lower than 1500Pa, must reduce the amount of gas, which pressure is 500Pa fire stop, working pressure 5000-7000Pa, the upper limit is 8000 Pa pressure the risk, the lower limit is 1500Pa . 14, the high, the main features of coke oven gas is flammable, explosive, toxic. 15, proximate analysis of coal with a volatile content, fixed carbon, ash and moisture. 16, boiler water circulation loop fault has stagnated, cycling back down the tube vaporization, soft drinks stratification. 17, the pulverized coal burning furnace radiation heat from a heat source of flame, high temperature flue gas convection heat. 18, the pulverized coal ignition and quick combustion conditions are sufficiently high temperature furnace, a sufficient amount of air mixed well, pulverized coal and air. Enough burn time. 19, ignition of pulverized coal into the combustion stage, the combustion stage, burning ember stage. 20, boiler mechanical rolling bearing does not exceed a predetermined temperature 80 degrees Celsius, the slide bearing does not exceed 40 degrees Celsius. 21, with factors affecting the steam load boiler water, boiler water salinity, pressure change, the vapor space of the drum height. 22, the principle of the steam separator drum gravity separation, inertial separation, centrifugal separation, separation of the water film. 23, the first ignition of the pulverized coal volatiles, fixed carbon is the latest ignition, the combustion of carbon is the longest. 24, steam soluble salt contaminated steam quality reasons, mechanical carryover. 25, the normal operation of the boiler drum water level in the glass tube than the water level high 50MM, when the water level in the steam table overall door leak, the water level high water table, the total gate leakage when the water level is low. 26, a method for enhancing heat transfer with a heat transfer coefficient is increased, raising the average temperature difference between the heat transfer, the heat transfer area is increased. 27, into the boiler furnace wall refractory layer, three-layer insulating layer and the sealing layer. 28, light blue flame blast furnace gas, as a bright golden yellow flame co-firing light yellow flame, coal, coke oven gas when the combustion gas as a combustion time. 29, the boiler by the "pot" and "furnace" composition, "pan" refers to a soft drink system is mainly composed of the drum, the downcomer, the header, waterwall, economizer, superheater composition; "oven" refers to a combustion system, a furnace, a burner, an air preheater composition. Calorific value 3.27GJ 30,1 tons of steam.