1000KG natural gas boiler
Factors affecting 1000kg boiler gas consumption SZS20 tons of gas vapors which gas consumption is influenced by three factors: 1. Calorific value of the fuel; 2. Boiler thermal efficiency; 3. Operating level fireman. So, if you want to consume as little fuel boiler over a period of time, there are several options: 1. Select efficiency gas furnace. A gas boiler type on the market a lot, have a variety, the price is different. Thermal efficiency between 85% to 95%, the heat efficiency is different from different manufacturers. Small boiler factory price is relatively low, but poor results. A price is true, so when the time to buy, do not look cheap, money is to buy a truly efficient boilers in the price. 2, select high calorific value gas. Different heating values of different fuels, different fuel heating value different origin. Just like oil, it is oil, but at a different price, per kilogram a few kilometers of oil is different. Of course, high calorific value, the price is relatively high. At the time of purchase, a good trade-off affecting the relationship between the price of both. 3, find an experienced operator. Regardless of the industry, when recruiting is like looking for the same experience, because experience is a treasure, you can do more things for the enterprise to save a lot of energy. Boiler workers, too, they save more money than those without experience. An experienced operator on a gas steam boiler can save 10 tons in addition to the cost of about 100,000 yuan, the user is also very worried about another problem: 10 tons of natural gas steam boilers. Specific cost depends on the manufacturing process, brand, product quality and other manufacturers.
The low-nitrogen gas 1000kg boiler adopts the international leading condensing combustion technology, and the nitrogen oxide emission is as low as 30mg/m3, which not only fully meets the requirements of Beijing's low nitrogen emission standards, but also reaches the world leading level of low-nitrogen emission combustion technology. Coupled with the high safety of ZBG oil and gas boilers and up to 95% thermal efficiency, ZBG oil and gas boilers have achieved low nitrogen emissions and greatly saved energy, making them the first choice for self-service heating for domestic and foreign customers.
School education is the foundation for development of our country, to provide environmental and healthy living environment for students is our top priority school. Winter is fast approaching, fast 1000kg boiler heating and for us to solve the problem of the coexistence of environmental protection, give us tremendous help provide heating in winter. --customer feedback
Fuel gas control step and the blowing process air volume of the total fuel gas steam 1000kg boiler steam boiler is achieved by adjusting a liquid coupling scoop blower. Organization fuel gas steam boiler combustion, is to make a, air pressure, air flow of secondary air with the good. Adjusting the amount of primary air should meet it carries the fuel into the furnace ignition of volatile oxygen required, and to maintain a certain speed, and without clogging the fuel discharge pipe of the jet having a certain rigidity. Primary air volume is too large and too small, the wind speed is too high and too low, should be avoided. In addition to adjusting the secondary air of combustion of the fuel should ensure that the oxygen demand, but must maintain a certain wind speed and primary air is mixed with the master time should have a strong stirring and mixing coke penetrate "the Gray" kinetic , which requires the case may be, each layer of the secondary air flow rate, in order to achieve stable combustion and flue gas excess oxygen appropriate destination. Fuel gas steam boiler, secondary air with what is better? Primary air volume air volume of the total share is called the primary air rate. A small air fraction, pulverized coal is heated to at least the heat required for the ignition point, fire faster, but the amount of primary air to satisfy the principle of combustion of volatiles. Secondary air mixed with the primary air time to the right. If it is mixed before ignition, means an increase in the amount of primary air, so that the ignition delay; hypoxia combustion secondary air if mixed will make late after ignition; if secondary air is mixed all at one position, since the secondary air temperature well below flame temperature, the flame temperature decreases, the combustion slows down, causing the fire. Therefore, the secondary air mixed with fuel should be based on the nature of the combustion zone as required timely sent, so that the combustion of oxygen, and will not reduce the flame temperature to ensure complete combustion and ignition stability. One or two wind speed with what is better? Fuel gas steam boiler once the wind speed is high, the fuel gas stream will catch fire in places far away from the burner, the ignition point postponed; once the wind speed is too low, it will cause a blocked ducts, and ignition point is too far forward, the burner will burn , but also easy to coke near the burner.