1 Ton Industrial Fire Tube Intelligent Control Diesel Oil Fired Steam Boiler
How pressure hot water boiler the security work in Year 6 at night, is located opposite the old 1 ton industrial fire tube intelligent control diesel fired steam boiler certain aquaculture farm town of Rudong Ju Wang Tan explosion cause of the accident is operating a boiler operator improper. Such as shrimp farms in the South East of whitening, the use of the boiler is very extensive, mainly used for farming shrimp shed warming. Before many farms use steam boilers, higher risk, many farms put on a higher level of security pressure hot water boiler. Pressure hot water boiler is no risk, but it does not mean you can neglect of duty fireman. To regularly observe the water level to avoid low water level, the situation appears dry, otherwise there will be a certain risk, but will seriously reduce the life of the boiler using pressure hot water boiler. Boiler operator should note the following: 1, strict implementation of rules and regulations, seriously concerned to learn boiler expertise, and constantly improve the level, to ensure safe and economic operation of the boiler. 2, the pressure hot water boiler in use, organizations and individuals will be allowed to change the structure of the boiler, valves and piping system 3, before the predetermined succession visits to check a variety of devices, comprising: a water tank (hot water tank, expansion tank) , the amount of energy (boiler gas meter), a thermometer (temperature of hot water tank, the boiler water temperature of heat medium) and the like operation, when the shift operation to check the recorded inventory tool, and to learn more about the operation of the boiler. 4, take over staff as required, shift and provisions ahead of time to take over the boiler room to do the preparatory work, and to understand the operation of the boiler. 5, shift work were prepared in advance, be careful and comprehensive inspections and investigations, to keep the boiler running. 6, shift workers should take over personnel issues related to equipment operation, water quality and boiler blowdown, etc., without handing, transfer of personnel shall not leave their jobs. 7, keep the boiler running when the boiler clean, no dirt, no leakage, no rust and corrosion, carefully fill out detailed equipment maintenance records. 8, using the boiler room is one of the vital sectors of the boiler unit, in addition to the boiler room workers, leaders and security, defense, department managers, other unauthorized persons do not access inside. 9, prohibits storage of flammable boiler room and other debris and the like, loaded with a small amount of lubricant required, cleaning the oil drums, oiler, to be stored in designated locations, and pay attention to check whether the explosives combustion. 10, boiler room to be equipped with fire fighting equipment, carefully managed, it should not be moved or used for other purposes. 11, boiler room floors, walls, doors and windows keep clean. 12, competent leadership regularly, irregularly running records, sanitation inspection, identify problems and timely solutions. 13, at the stipulated time to work on time, do well shift recording, not just leave their jobs, leave something. 14, alcohol is strictly prohibited in the boiler room, drowsiness, gambling, fighting once found seriously. After 15, equipment failure and accidents timely reporting (timely reporting on duty the night the person in charge), realistic write a written accident report, to be thoroughly investigated, after clarifying the responsibility, resulting in losses to the accident negligence, be held accountable process.
Increase productivity boiler system must first be optimized for verification, including the entire steam system for a complete analysis, and focus on some of the energy waste places. Via check can often find opportunities to save energy, increase productivity, and environmental protection have a positive contribution of. Check includes a steam generation, distribution, use and condensate recovery. The main steam waste requiring special attention place: exhaust gas boiler: boiler efficiency emissions system the most important indicators, the loss of energy is the most important place. Combustion air: general air enters the combustion furnace of the genus room temperature, require a lot of heating energy, i.e., the most commonly used power saving mode using a high temperature exhaust gas to preheat the combustion air of boiler, boiler efficiency can be significantly improved. The fuel / air ratio: Proper oil / gas mixture can only complete combustion, if the lack of air, combustion is incomplete, not only smoky pollution, environmental protests caused nearby residents, and easy carbonized grease gun and boiler heating tubes affect performance. If excess air is formed wasted energy, reducing boiler efficiency. Via the oxygen content of the tail gas can appropriately adjust the oil / gas ratio. Oil-fired boiler exhaust gas which content 3%, i.e., the excess air of about 15%, as the standard combustion control.
13th of this month, Jiangsu Province, held a working meeting air pollution control, meeting the main objectives and tasks around the year, and plan the next phase of priorities, from morning to promote strict air pollution control this year's tight.
First, in-depth treatment of industrial pollution, dehumidification start off white along the Yangtze River coal-fired power project to promote the electricity, steel, cement, coke, glass, carbon, boilers, furnaces and other key industries the full implementation of the transformation of ultra-low emissions, the province basically completed iron and steel enterprises sintering machine ultra-low emission transformation, cement, coke, glass, carbon industry to achieve the emission limits set provincial requirements.
After the gas-steam circulation pump approach failed for some time to use gas steam oven, it will produce a precipitate. At this point, we need to clean heat transfer oil furnace, but before cleaning, we need to know what kind of sediment, and then cleaned the right way, if the heat transfer oil, grease appears very easy to make the wall thermal resistance increases, will increase the production of energy, gas steam liquidity will deteriorate, production will be reduced, the operating cycle will shorten the life of the device will be. Shorten, which in turn affect production. Some of the more common gas 1 ton industrial fire tube intelligent control diesel fired steam boiler deposits are: sulfate, carbonate, silicon and iron. Acid sulfate does not bubbling, since relatively hard sulfates, carbonates decompose at high temperatures, the bicarbonate will dissolve, but the release of carbon dioxide will form an insoluble carbonate salt. When the temperature reaches 300 ~ 400 ℃, hot oil furnace thermally cracking occurs. It will produce carbon deposits on the inner wall and an inner wall, it affects the heat transfer efficiency. Easy to produce oil furnace heat transfer in high temperature environments. Thermal cracking, thermal polycondensation, and its kinematic viscosity increases, the fluidity deteriorates internal oxidation of the oil pipeline, oil conductive accelerated failure, the machine will be damaged, endanger human will be high. Steam oven gas processing cycle pump failure: (1) When the current is below the normal circulating pump, the circulating pump efficiency is lowered, the flow rate is reduced, the fouling of the heating pipe may be blocked, it should be cleaned. (2) circulating pump pressure constant, the current increases, flow decreases. Bad heat transfer fluid, the viscosity increased, should be replaced or regenerated. If the system does not remove water or aqueous decomposition newly heated conductive liquid should be immediately opened exhaust valve to the exhaust gas. (3) circulating pump current is reduced, the pump outlet pressure back to zero, indicating that the pump is not idle. It may be vaporized oil, gas and steam oven measures to find the cause vaporization; if the filter is clogged, the circulation pump should be evacuated and cleaned immediately opens the bypass filter; if the heating fluid contained in the new water or heated water, the system does not exclude the decomposition gas, the exhaust valves should be opened immediately exhausted.