Automatic Coal Hot Water Boiler Manufacturer
Henan difference fast boiler steam boiler steam boiler is a steam boiler with ordinary steam production machinery and equipment, generally used gas, or coal gas as a fuel, there are an electric steam boiler. Henan fast boiler for the inspection of the steam boiler is a steam boiler gas, fuel oil, gas, and it is common conventional steam boiler with the following differences: "steam boiler supervision norms" and the forthcoming introduction in June next year the new pot rules " boiler safety technology to monitor the specifications "are clearly defined steam boiler needs to be regulated by the state. In other words, users looking to buy a steam boiler plant boiler installation and can not be used directly. Before installation To pot seized by the approval and registration required for installation, and the need for inspection on a regular basis, usually one year during the annual inspection. But there are some of the steam boiler does not require registration and annual inspection, the old rules and the new pan pot regulations stipulate a water capacity less than 30L steam boiler is not within the scope of the surveillance. Because the water capacity of 30L water capacity than at home with a water heater are also small, so there is no risk of explosion, we do not need supervision. Henan water capacity fast boiler steam boiler 26L, belongs steam boiler does not require supervision. Steam boiler explosion hazards generated is amazing. In many steam boiler explosion in the boiler room were razed to the ground, the annual explosion of a steam boiler will be the first to cause casualties and significant economic losses. Henan fast boiler steam boiler is to achieve the ultimate, the boiler body through the scientific design, water capacity is very low, only 26L, itself, there is no risk of explosion on security. The thermal efficiency of conventional steam boiler is only 80%, while the party Henan boiler thermal efficiency of fast gas steam boiler can reach more than 93%. Henan plus energy-saving system fast boiler control systems, the actual energy savings up to 30%, running down a year could save hundreds of thousands of operating costs. The Henan fast boiler steam boiler without boiler room, an area itself is small, you can put in the basement or roof, it can also be placed directly next to the device requires the use of steam. Saving the cost of laying pipe network construction costs and the boiler room, a significant reduction in the use of the initial investment.
Hot water boiler in the school dormitory and classroom building are generally used for central heating, drinking water and bathing water aspects of teachers and students and so on. Shanxi Linxian County high school is an important educational school personnel training for the community. 2017, the school responded positively to national coal to gas and other environmental policies, but also to provide students with a more favorable living and learning environment, the school decided to phase out conventional coal-fired boilers, clean and environmentally friendly replacement for the gas boiler. After getting to know and choose the boiler industry, major companies, determined cooperation with professional production of clean fuel boiler fast boiler-by-side to provide a fast 4.2MW integrated condensing gas automatic coal hot water boiler manufacturer (WNS4.2-1.0 / 115 / 70-YQ).
Steam boiler accident type and processing method, and use common sense safety boiler steam boiler accident type and processing method, overpressure accident 1 boiler, boiler overpressure phenomenon of (1) a sharp rise in steam pressure, exceeds the allowable working pressure gauge pointer over " red line "safety valve after the pressure is still elevated. (2) the operation of the device is the interlock overpressure protection, should send overpressure alarm signal, stops the air blowing, the wind, coal. (3) steam temperature and steam flow rate reduction increases. 2, to treat boiler overpressure (1) weakened rapidly burning, manually open the valve or bleed valve. (2) increase the water supply, while the lower reinforcing blowdown drum (It should be noted at this time to maintain the normal water level of the boiler), in order to reduce the temperature of the boiler water, thereby reducing the pressure in the boiler drum. (3) as a safety valve malfunction or all of the pressure gauge damage, emergency shutdown, safety valves and pressure gauges are to be repaired after the boost operation. When endanger the safe operation of (4) Boiler excessive pressure, blood pressure should take measures, but too fast buck is strictly prohibited. (5) boiler overpressure eliminate serious, to the shutdown of the boiler internal and external inspection, to eliminate the overpressure caused by deformation, leakage and other safety accessories and maintenance unqualified. Second, an accident boiler water, boiler water shortage (1) below the minimum safe water level line, or can not see the water level, the water level gauge glass (plate) as a white. (2) as a full-color water level gauge vapor instruction color. Low water level alarm signal (3) water level alarm occurs. (4) low water interlocking means, the water level should be below a prescribed value blower, Fan, grate reduction motor stops running. (5) a sharp rise in the superheater steam temperature, higher than the outlet steam temperature. (6) boiler exhaust gas temperature rises. (7) the water flow is less than the steam flow, causing Should the water tube due to tube cracking or economizer, an opposite phenomenon occurs. (8) When a serious water shortage, can smell the burnt smell. (9) When a serious shortage, the door can be seen from the red-hot waterwall tubes. (10) a serious water shortage, the furnace tube may rupture, then can hear the explosions, smoke and steam from the door, watching spray the fire door. 2, boiler water treatment (1) through the "waters", sentenced to severe water shortages, emergency shutdown must be prohibited blind to the boiler feed water. (2) through the "waters" sentenced to a slight lack of water, it should reduce fuel blast, the wind, and slowly feed water. Third, full water boiler 1 accident phenomenon (1) above the maximum allowable water level line, or can not see the water level, the water level gauge glass (plate) dark color boiler filled with water. (2) all of the water phase as a color level gauge indication color. High-water alarm signal (3) water level alarm occurs. (4) decreased superheated steam temperature. (5) water flow is not normally greater than the steam flow. (6) water in a large number of sub-cylinder, severe trap operation. (7) with a large amount of water steam severe, increased salinity, water hammer occurs in the sound of the steam pipe, the steam connection flange outwardly dripping take place. 2, boiler full of water treatment rinse water table, determined to be minor or serious full of water full of water. Method: Close water table, the water pipe connected cock, then open drain cocks As can be seen from the decreased water level, indicating a slight full of water, the water supply is stopped, the drain valve open, put to the normal water level. Such as severe filled with water due to take emergency shutdown measures.
Most food processing facilities have industrial steam boilers or automatic coal hot water boiler manufacturers for generating steam or hot water for processing, cooking, or sanitation. Coal, fuel oil, and natural gas are the major fossil fuels used by food industry boilers.