20t h Energy saving industrial coal fired steam boiler
Cade Shopping Mall is located in central Shanghai Hongkou District, Shanghai Daily larger flow of people in the region. The introduction of Shanghai air pollutant emission standards, boiler flue gas emissions of nitrogen oxide emissions to less than 80 mg / m, Shopping Mall a coal-fired boilers have been used for many years, NOx emissions far super to this request, the urgent need to replace more environmentally friendly low nitrogen emission boilers. Other units through the use of fast Boiler introduction and understanding, determined and fast boiler to achieve cooperation, party fast to their specific needs to recommend one condensing gas hot water boiler of a 4.2MW for heating needs of the shopping center.
Horizontal industrial boiler for sale in India
ZG horizontal industrial boiler range which can be exported to India: horizontal fire tube boiler, horizontal water tube boiler, horizontal coal fired boiler, gas fired boiler, oil fired boiler, biomass fired boiler and so on. These product are featured with stability, quality, durability and reliability because our product are manufactured with top quality raw materials. The design, construction and superintendence of a wide variety of steam boilers, hot water boilers, and power plant boiler.
What are the methods to reduce pollution mill 1, check for leakage protection and maintenance of: 2 mm steam leakage will cause energy losses of more than 10 tons of coal each year do? When you do not use it, you can turn it off to save energy. For water, steam and compressed air leak survey and routine maintenance, cost very little. 2, the non-contact cooling water in repeated use: Since the non-contact cooling water temperature and the quality is very good, it can be reused for desizing, scouring, rinsing and other processes. Three best source of cooling water is regenerated: sintering machine, a pre-link and compressor systems. The plant water recovery system may be installed, pipes, valves, storage tanks, and control systems. 3, repeated use of steam condensate: Textile mills require large amounts of saturated water vapor in the dyeing process, wherein a portion of the condensate is converted to its high temperature and purity. Water can be pumped back to the boiler to form a new steam. For those who buy steam from suppliers, or boiler is located away from the dyeing process, the condensate can be used as water washing or desizing. 4, pre-treated wastewater reuse Procedure collected bleaching, mercerizing machine, the water can be reused in other programs, there is no direct discharge of wastewater. 5, hot wash water is recovered from the hot gas in the dyeing process, large amounts of hot water are used to wash. Heat the washing water can be collected by the system plate heat exchanger to preheat the water to be sent to the next washing. 6, pre-screened coal enterprises should introduce screening spiral coal boiler technology to selection of raw materials. It is possible to improve the media tell the good, the bad quality of proportion, to avoid loss of small volumes of coal and coal calorific value. 7, maintaining steam traps traps can help maintain effective delivery of the steam plant. The valve is removed from the steam pipe and prevent further condensation water, so as to avoid heat loss and reduce fuel consumption. 8, the piping, valves and heat insulated flange experience pipes, valves and flanges waste of resources, reducing efficiency. Steam delivery device insulated to prevent vapor loss is an inexpensive, energy-saving method of .9, the heat recovery from the boiler chimney at a temperature of 360 ℃ smoking, sometimes discharged directly into the atmosphere, there is no heat recovery. In fact, this heat can be used to preheat boiler water, steam or create a new steam system. 10, optimization of compressed air systems consume a large amount of compressed air in many parts of textile machines Mills. These instruments are prone to leakage, particularly in a threaded joint, rubber joints, valves, automatic regulator, the inflatable device and the old gasket. In addition, the use of compressed air pressure is usually based on the maximum pressure setting; reduce this pressure is feasible and would not have any negative impact manufacturing.
The heat loss of exhaust smoke is the largest of all kinds of heat loss in boiler. Generally, the heat loss of exhaust smoke is 6% of the heat fed into the furnace, and the heat loss of exhaust gas increases 0.5% when the temperature of exhaust gas increases by 12 ℃ and 15 ℃. So the exhaust temperature is one of the most important indicators of boiler operation. The following are several possible causes of increased flue gas temperature in the furnace: (1) slagging and ash accumulation on the heated surface. No matter it is the slag accumulation in the water-cooled wall of the furnace, or the ash deposition in the superheater, convection tube bundle, economizer and preheater, the thermal resistance of the flue gas measurement will increase, the cooling effect of the flue gas will become worse due to the deterioration of the heat transfer, and the exhaust temperature will rise. (2) excess air coefficient Big. Under normal conditions, the exhaust temperature increases with the increase of excess air coefficient at furnace outlet. After the increase of excess air coefficient, although the amount of smoke increased, the rate of smoke increased, and the convection heat increased, the increase of heat transfer was not as much as that of the increase of flue gas. It can be understood that after the increase of smoke speed, the flue gas leaves the heating surface without time to transfer heat to the working fluid. (3) the air leakage coefficient is too large. The flue gas leakage in the furnace and rear shaft of a negative pressure boiler is inevitable and the leakage coefficient allowed by a certain heating surface is specified. When the air leakage coefficient increases, the effect on the exhaust temperature is similar to that of the superheated air coefficient. And the air leaks away. The closer the furnace is, the greater the influence on the rise in exhaust temperature. (4) Water supply temperature. When the steam turbine load is too low or the high pressure heater is out of line, the feed water temperature of the boiler will be lowered. Generally speaking, if the fuel quantity is kept constant, the heat transfer temperature difference of the economizer decreases and the heat absorption of the economizer decreases when the feed water temperature is increased, which makes the exhaust temperature increase. (5) moisture in the fuel. The increase of moisture in the fuel increases the amount of smoke, thus increasing the exhaust temperature. (6) Boiler load. Although the boiler load increases proportionally, the amount of smoke, the amount of steam, the amount of water supplied, and the volume of air increase proportionally, however, the flue gas temperature at the furnace outlet increases proportionally. Increase, so that the exhaust temperature increased. After increasing the load, the outlet temperature of the furnace increases, the heat transfer temperature difference of the convection heating surface increases and the heat absorption increases. Therefore, the more the convection heating surface is, the less the influence of the boiler load on the exhaust gas temperature is. (7) fuel varieties. When the low calorific value gas is fired, the radiative heat transfer in the furnace decreases due to the decrease of furnace temperature, and the non-combustible components in low calorific value gas, mainly N _ 2, CO _ 2 and H _ 2O, increase the amount of flue gas, so the exhaust temperature increases. Although the excess air coefficient of furnace outlet is lower than that of coal burning, the ash content in the fuel oil is very low after the pulverized coal furnace is changed to burn oil, although the excess air coefficient at the furnace outlet is lower when burning oil. There is no larger ash particle in flue gas, and there is no cleaning effect of larger ash particle on the heating surface, and the convection heating surface is polluted more seriously. Therefore, combustion is not good, often smoke-emitting boiler smoke temperature rise. When there is a steel ball dust removal device at the tail, the exhaust temperature is slightly lower than that of burning coal because the tail is cleaner. (8) the operation mode of pulverizing system. For a closed pulverizing system with a silo, when the pulverizing system is in operation, as a part of the water in the fuel enters the furnace, the furnace temperature decreases and the flue gas increases, and the cold air leaking into the pulverizing system enters the furnace as a primary air during the operation of the pulverizing system. Reduction of air flow through air preheater To raise the exhaust temperature. On the contrary, when the pulverizing system is shut down, the exhaust temperature decreases.