oil fired hot water boiler with ce certificate
50, when arranged inside the boiler room to note a safety distance, the front end of the boiler ready spacing of not less than 2/3 of the length of the furnace, and not less than 2 m; vertical boiler can be shortened; bulk boiler is not less than 4 m and does not affect the blast furnace operation and maintenance. 2, the boiler side and rear channel spacing of not less than 0.8 m, and should meet the operational and maintenance (such as replacement tube bundle cleaning, stirring the fire, etc.) requirements. 3, the top horizontal boiler headroom not less than 2 m; vertical boiler top clearance height to facilitate the operation and maintenance; headroom boiler room the other channels, should not be less than 2 meters, when the passage of time and no need to operate its headroom height of 0.7 meters. 4, the boiler room is provided for two or more boilers, the boiler the distance between adjacent not less than 1 to 1.5 times the cylinder diameter of the boiler. 5, the boiler room is generally preferred fireman operation chamber provided, on the total rated greater than or equal evaporation 4t / h steam boiler (heating or fired hot water boiler with ce certificate is equal to or greater than 2.8MW) must be provided stoker operating room. Electric boiler tank may be provided in front of the boiler, and to ensure the art to fireman facing boiler water gauge, pressure gauge and other instruments during operation. 6, to the total rated evaporation 2t / h fuel gas boiler room to be provided or water spray foam fire extinguisher system, should outdoor outdoor fire hydrant, other fire-fighting equipment should also have the boiler room. 7, the fuel in the boiler room daily oil tank, the oil pump is generally not located in the boiler room, between daily oil tank, the oil pump between the application of the fire resistance of greater than 2.00h wall, the fire resistance of greater than 1.50h floor spaced from the other parts. Daily fuel tank between the boiler room and the door between the oil pump should be able to self-closing fire doors Class A, and let the oil block measures. Household upper tank return pipe to be provided, should be greater than the oil return pipe back to the oil pump. 8, an oil tank and all piping must have a reliable electrostatic grounding, the grounding resistance should not exceed 30 ohms. 9, gas boiler room boiler design should also comply with the relevant safety requirements of gas boiler room.
Furnace body Design of heating BoilerHeating boiler is a kind of heat energy equipment, which uses coal, fuel oil, gas, power and other fuels as heating source, heating water or other medium to a certain temperature through pump, valve and rely on radiator to heat the local environment to achieve the purpose of heating. The boiler structure is designed according to the normal pressure, the top of the boiler is equipped with a large air hole, the boiler works under the normal pressure, far from the explosion danger; The furnace body of the boiler is optimized by computer, the size of the boiler is optimized completely, the shape of the boiler is coordinated and beautiful. The vertical boiler of CLHS adopts the combustion mode of burners, and the fuel is burned under micro positive pressure in the furnace tank. The high temperature flue gas radiates heat transfer in the furnace tank, and then enters the pyrotechnic pipe convection. Heat exchange, and finally exhaust through the cigarette box. The smoke pipe is inserted with blocking plate, which slows the discharge rate of flue gas, strengthens the heat transfer, and ensures that the heat generated by fuel combustion heats the water of the furnace to the maximum extent, which greatly improves the thermal efficiency of the boiler. The CWNS horizontal boiler adopts the full wet back type three-way structure, the flue gas flow is long, the exhaust temperature is lowered, the full corrugated furnace tank is set up, the flame is strongly disturbed, and the heat transfer coefficient is greatly improved. It also effectively prevents the reduction of equipment life due to the hot expansion and cold shrinkage of metal. Large diameter smoke pipe and large hole bridge clearance, so that the boiler in the same time scale coating thin and easy to clean up.
Due to increase market demand for air conditioning, we increased the number of production lines, faced with the urgent need of a steam boiler problems. Emergence of fast boiler is time for us to solve this problem. From the start of contract manufacturing to transportation to our company for installation and operation, Fang fast only 35 days to solve our urgent needs. --customer feedback
Henan gas treatment condensing boiler operation in the secondary combustion Accident Henan condensing gas boiler, deposited in the rear of the boiler flue gas condensing Henan combustibles (soot, carbon black) re-ignition combustion phenomenon called secondary combustion, also known as Henan condensing gas boiler flue tail and then burned. It will backpass severe, air preheater, induced draft fan and other equipment economizer even destroyed. 1. Henan condensing gas boiler secondary combustion phenomenon (1) a sharp rise in exhaust gas temperature, chimney to take smoke, fire or even smoke. (2) changes drastically furnace pressure, positive pressure occurs. (3) severe flue enclosure dark red. (4) when there is an air preheater, a sharp rise in the temperature of the hot air, pressure instability. (5) blast doors sometimes the tail action. Cause 2.Henan condensing gas boiler secondary combustion (1) poor atomization burner, oil, gas and incomplete combustion into the rear of the boiler. (2) combustion improperly adjusted, with insufficient wind or with the wind unreasonable. (3) Henan condensing gas boiler startup, shutdown during low furnace temperature, the unburned fuel in the furnace. (4) When shutdown or boiler fire, air gun valve is not closed. (5) the combustion chamber negative pressure is too large, too late to make the gas burn it into the rear of the boiler. (6) Long-term non-stop cleaning backpass furnace, accumulating a certain amount of soot or carbon black. (7) through the air preheater flue or leakage. 3. The gas processing condensed Henan secondary combustion boiler (1) should immediately stop the gas, stop the wind, shutdown. (2) closing the flue, and a baffle duct around the door opening, is prohibited to start sending, induced draft fan. (3) immediately extinguishing device into steam, carbon dioxide or other fire extinguishing means, (4) Strengthening Henan condensing gas boiler feed water and turn on the water, open the valve or economizer recirculation tube to protect the economizer is not burning. (5) When the exhaust gas temperature close to the temperature of the injected steam, or less than 150 deg.] C over 1h and stable openable inspection hole inspection, after checking element determines an ignition source, before the fan starts ventilation and cooling. (6) when the temperature drops below the flue 50 ℃, check before entering the flue tail heating surface, and should completely remove the flue soot. If not burning, can be re-started ignition; if burning, should be replaced, repaired burning member.