china horizontal gas fired hot water boiler
Furnace pulverized coal fired boiler is smaller than you: Today saw a piece of content, said: with the same capacity, oil-fired boiler furnace is smaller than pulverized coal. why? The following reasons: the size of the furnace volume, in the boiler capacity is determined, depending on the size of the volume of heat load. Volumetric heat load size is mainly determined by the type of fuel. After the fuel into the furnace, it will take some time to burn. Typically all the required fuel burn before leaving the furnace, the pulverized coal burnout is obviously longer than oil, i.e. coal flame longer than oil. To ensure long-term safe operation of the boiler, not only to prevent the boiler slag, and flue gas at the furnace exit is low to make the temperature at the start of the deformation ratio of ash flue gas temperature 50 ~ 100 ℃, at the outlet of the furnace and to prevent subsequent convection slagging heating surface. In many coal ash content, coal-fired furnace to control the furnace exit gas temperature typically of 1050 ~ 1100 ℃. The fuel oil furnace because very little ash, furnace slag is not dangerous, do not consider the problem of slagging furnace slag discharge outlet pipe, so the furnace exit gas temperature can be higher. For the above two reasons, the volume of the thermal load is higher than Pulverized fuel boiler. Pulverized volumetric heat load is about 145 ~ 185kw / m3, and the volumetric fuel burner heat load of up to 255 ~ 350kw / m3, so the same volume of the furnace fuel burner furnace capacity is relatively small pulverized coal fired. Rinse water gauge oil-fired boiler
We produce steam boiler is a very important part of the device, this provides a quick way to our gas steam boiler, after use, we found an excellent energy-saving effect boilers, flue gas discharge temperature is lower than the previous boiler equipment many, in line with national environmental provisions of the boiler equipment. --customer feedback
Care coup gas boiler gas boiler as the name suggests refers to the fuel gas boiler, and it fired boiler, electric boiler compared to the more economical, so most people are choosing it as steam, heating, boiler equipment for bathing. Then its care coup, what does? 1, during operation of the gas boiler note the following points: (1) does not allow pressurized furnace burning or smoke, because stoker hole cover easy to burn. (2) on the bottom ground plane is not water, to prevent wet etching. 2, gas boiler run every 2-3 weeks, should be checked once. 3, gas boiler run every 3-6 months after the shutdown should conduct a comprehensive inspection. (1) and outside it to check if the pressure receiving portion of the weld, the steel sheet or absence of internal and external corrosion, should be repaired if found in serious defects, if not a serious defect also to be repaired when the next shutdown, if there suspicious, but does not affect safety during production, should make records for future reference. (2) can be checked and the water boiler primer coating to prevent corrosion. 4, gas boilers and boiler base paint at least once a year. 5, maintenance of gas boiler normally unused methods: dry and wet two kinds, one month shutdown, care should be taken dry method, wet shutdown can be less than one month regimen. About Care coup gas boiler small series first introduced here today, if you want to know more, please stay tuned to this site.
Piezoelectric often pay attention to what is currently required boiler maintenance, boiler advanced piezoelectric often need to be applied in industrial production and daily life of boiler equipment. However, the electric boiler pressure part of mechatronics equipment running high. If the user in a timely manner to carry out boiler maintenance, oil equipment will lead the line, aging equipment, pump wear. Therefore, in the operation of the boiler, the user should pay attention to equipment maintenance. First, note that prior to detecting piezoelectric constant boiler shutdown maintenance or service, the user equipment in accordance with normal operation to achieve slow cooling shutdown procedure, while the user should use the boiler water circulation and ventilation furnace, boiler and the furnace temperature was gradually decreased. Second, note that partition is provided during maintenance, the combustion chamber and flue piezoelectric often tested to be separated from the main boiler flue or other operation of the boiler with the flue connected. And flue tightly closed, after isolation and ventilation. Further, using a blind partitioning plate device should have sufficient strength, stiffness, to avoid high pressure medium at atmospheric pressure electric boiler drum, indicating the position of the partition, to avoid confusion. Third, note that the detection device before the container inspection atmospheric pressure vessel, the user must be turned off connecting line between the container and the gas apparatus, especially in the passage of inflammable poisonous media device. Container equipment during maintenance equipment not only need to close the valve, you must also use the device Blind plate closed to prevent valve leakage, the leakage of flammable or toxic gas into the container, resulting in a fire, explosion or poisoning.