2 ton industrial natural gas or heavy oil steam boiler
Features 10 1 atmospheric 2 ton industrial or heavy oil steam boilers, hot water boilers controller computer, all the functions are stored on a magic smart chip, a key to power boilers, automatic timing, temperature operation, the user can set the start , shutdown time, the setup is complete, no special duty to save time, and effort. 2, the burner configuration imported brands, high degree of automation, automatic purge controller according to the instruction, the electronic auto-ignition, spontaneous combustion, air oil (gas) automatic ratio adjustment, security and stability performance, good combustion. And there are flameout protection device, ensure safe operation. 3, the inner fire tube inserted spoiler retardant, smoke slow speed, to strengthen the heat exchanger, the temperature of the flue gas discharged from a low smoke chamber, reducing heat loss and save fuel. 4, large font display temperature, easy to grasp and boiler operating conditions of the system, the water temperature can be freely set from 10 ℃ to 90 ℃, automatic boiler or heating system to provide users with life, bath with hot water. 5, the control system in accordance with the temperature control of boiler water circulation pump start and stop, boiler water circulating pump starts when the water reaches an upper limit temperature, lower than the hot water circulation pump stops when the water temperature lower limit. 6, horizontal fuel gas hot water boiler three return all wet back structure, using a large furnace, rough smoke tube design, increased furnace radiation heat absorption, the effective energy saving. Using threaded pipe and waveform furnace, greatly enhanced heat transfer effect, greatly saving fuel consumption. 7, while the machine is equipped with thermal protection (ultrahigh temperature furnace, the burner is automatically stopped and an alarm buzzer, the second over protection (the boiler shell temperature exceeds 105 deg.] C, the secondary circuit is automatically cut off), the lack of anti-dry protection of water (when water is lower than the low water level of the furnace, the boiler is stopped and an alarm beep), a boiler leakage protection (the control system detects electrical leakage, short circuit, automatically cut off the power) .8, according to the boiler pressure design , no pressure in the boiler state, there is no safety hazard .9, using advanced multi-layer insulation centrifugal glass wool, steel for packaging famous white color, heat loss, anti-rust appearance .10, gas heating boiler is widely used in homes, villas , hospitals, schools, hotels, restaurants, fitness center, bath center and other enterprises.
Note Di 2 ton industrial or heavy oil steam boiler steam boiler operational considerations should use great caution when using, because the slightest error will bring harm, so the operation should be more cautious, for a description of the use of steam boilers, process clear operation should pay attention It matters. Biomass boiler is a kind of boiler to biomass energy as a boiler fuel called biomass boilers, steam boilers into biomass, biomass hot water boiler, biomass stove, biomass thermal oil heaters, vertical raw biomass boilers, biomass boilers and other horizontal. Steam boiler is an energy conversion device, the energy input to the boiler fuel chemical energy, electrical energy, thermal energy and other forms of high temperature flue gas, and after converting the boiler, the steam output having a certain outside thermal energy, high-temperature hot water or an organic carrier. According to many years of experience in the use of steam boilers, summarizes the operating steam boiler matters should be noted: First, before the boiler to be familiar with the use of manual, to protect the normal use of safety equipment and operating personnel fundamentally. Before starting, check the power supply voltage is operating properly and water, close the drain valve to open the water supply valve, the pump checks whether the jam, remove the blade cover, and the motor shaft to the flexible state to start the scroll machine. Check the boiler or the power off when changing accessories to avoid the risk caused by the charging operation. Secondly, the electronic control box, pumps, motors and other components should be avoided in order to prevent moisture absorption burning boiler should pay attention to maintaining clean, according to the relevant boiler water quality requirements, be sure to install a water softener use, because they do not use a water softener can cause boiler fouling, serious it can cause burst pipes, shortening the life of the boiler. Finally, if the above conditions are not covered by the warranty, if not used in accordance with the provisions of water treatment equipment, sewage note that when used. Emissions once a day, with pressure 0.1MPa-0.15MPa emissions to prevent clogging pipes, sewage pipes should be connected properly to prevent burns, the safety valve should be flexible maintenance plans, pull the lever at least once a month safety valve to check its take-off and elastic seat. Local Technical Supervision safety valve should be checked once a year.
Inner Mongolia Erdos special prosecutor with the Office of the State Administration of the market, the special work of investigation and remediation of pipe hidden within the scope of the power station boilers, special inspection and testing by personnel with the Ordos Municipal Quality Supervision Bureau, Inner Mongolia Academy of pot seized the relevant professional and technical personnel , fully operational.
According to "Boiler Safety Technology Supervision", "Boiler Inspection Rules," "Boiler periodic inspection rules" and other relevant standards, conduct a special inspection of the boiler design, manufacture, installation, use, management, and inspection and other aspects. Check not extended key subject of boiler tubes, means for producing a combination of elements not subject supervisor embodiment, boiler tubes mounted QA aspect, there are security risks flow meter housing and rescue drills and contingency plans.
For risks and problems found in the inspection, and the enterprises need before the prescribed date, timely rectification results submitted to the local special equipment safety supervision and management departments.
Gas-fired 2 ton industrial or heavy oil steam boiler abnormal situation, how should we deal with it? When we use gas steam boiler, failure or abnormal phenomena it is inevitable, but in order not to affect the normal use, in the event of a problem gas steam boiler to be timely processing solutions, then the face of all kinds of circumstances, we should how to handle it? Share some of the ways we deal with unusual circumstances. If only gas steam boiler circulating pump abnormalities, such as its current decreases, the pump outlet pressure back to zero, which indicates no oil pump is idle, it may be caused by oil vaporization. Yang identify the reasons therefore first vaporized measures; such as clogging of the filter circulating pump bypass opening evacuated immediately clean the filter; heat transfer fluid as a result of added aqueous or decomposed gases are not excluded in the system, should immediately open the vent an exhaust valve. Circulation pump pressure constant, the current increases and the flow drops, deterioration of the thermally conductive fluid, the viscosity increased, should be replaced or regenerated. New heat transfer fluid as a result of decomposition of aqueous or excluded gases in the system, should immediately open the vent valve of the exhaust gas. When the current is lower than normal circulation pump, the circulation pump efficiency is decreased, the flow rate decline may be heating pipes plug fouling, stainless steel chain should be cleaned. If the gas steam boiler before and after the filter increased in pressure, the pump inlet pressure drops, the filter may be stuck, the opening of the bypass, disassemble and clean the filter. In addition to its low furnace outlet temperature liquid phase heat carrier, mainly for lack of heat fouling problems, it is timely soot blowing. Gas steam boiler grate more common problem is stuck, there are reasons including breaking grate or the grate off loose pins; coal grate has stuck to metallic inclusions; arched grate; slag is sinking the tip of the grate stuck. In response to this phenomenon, the required reverse hand grate plate debris removal, replacement breaking grate after the start, then jammed as startup, stop the rotation of the reasons detailed inspection to resolve. But also to re-adjust the adjustment screw on both sides of the grate tension, if still does not work, we need to replace the sprocket.