condensing natural gas steam boiler in food industry
Overview of 3 ton Firetube Gas Fired Steam Boiler
3 ton Fire tube gas fired steam boiler as one of the implementation subitems awarded by the world bank GEF efficient environmental protection boiler project, which is developed by ZG Boiler for the technical cooperation with the German, has reached the advanced world level, and is in the leading level of domestic boiler industry.
3 otn Fired tube gas fired steam boiler for sale in ZG Boiler adopts the international popular three return structure with big volume design of combustion chamber, and it can make the burning more fully. The corrugated furnace structure not only increases the heat transfer area, but also satisfies the free expansion after the furnace is being heated. It has a wide fuels adaptability, not only gas, but also oil, light oil, heavy oil, city gas, biogas and so on all can be its fuels.
Factors industrial boiler energy-intensive factors which have high energy consumption of industrial boilers which 1, energy consumption is low management level industrial boiler is too large, there are currently a lot of long-term business. On the one hand understanding of the enterprise energy conservation boiler is still not sufficient, on the other hand the energy management level is still at a low level, and even some companies even the most basic measuring instruments are not equipped. In order to reduce operating costs, many companies have to buy the old boiler use, lack of components purchased fuel means of inspection. Even in the case of raw coal screening is not performed, it is directly put into production use, it is difficult to ensure full combustion of coal. Not only the thermal efficiency is low, but also resulted in a waste of fuel. 2, heat recovery is poor combustion is incomplete, the situation is the high rate of heat loss is extremely common in industrial boilers used in the process, saving the main parameters of the boiler will be exceeded. Economizer function is to heat energy recovered, but in actual use, heat recovery efficiency is very low. In this case, do not use a lot of boiler economizer direct altogether, inevitably produce exhaust gas temperature is too high. Meanwhile, return the device and steam condensate recovery, it has not been fully appreciated and better use, some are put to use in the boiler after installation, and did not take appropriate measures to deal with poor recycling effect. 3, lack of effective supervision of the level of energy service work, depends largely on the level of experience and technical personnel. But in practical terms, due to the lack of technical personnel, resulting in the energy service work at the level of the low. Various enterprises produced energy-saving products with high imitation, coupled with the lack of effective supervision of energy-saving measures, resulting in the entire market of energy-saving products more confusing. The effect of not only energy-saving effect is not ideal, and to transform the poor, the performance of energy-saving products remains to be greatly improved. Market confusion, vicious competition phenomenon has not been fundamentally curbed.
Directly under the Central Government Offices Administration (referred to as the straight Authority) is the CPC Central Committee and subordinate units, are responsible for the CPC Central Committee and services for the organs and services, an important function of serving the people. Central Government institutions funds, finance, public service vehicles, the state-owned assets and real estate management, service management is responsible for the specified life of the party and state leaders as well as services related objects.
Combustion characteristics and operation of condensing steam boiler in food industry steam for steam boilers everyone know how much will the following to let everyone have a preliminary understanding of the steam boiler by two aspects, but also hope to give a friend wanted to buy a steam boiler of some help. Chain-type layer is generally fixed combustible fuel steam boiler chain grate or a grate (the traveling), it is fixed only for small coal-fired boilers. The most commonly used medium-sized coal-fired boilers or for chain grate, as the chain travels will gradually sent to the tail of the coal grate in the process of moving complete fuel combustion tube from the inlet to the lower part of the grate grate internal supplemental air required for combustion, ignition top-down, no ventilation grate uneven seam and around the relative movement, through non-flammable. After heating area of the heating flue gas temperature of the working fluid designed to flow through the same furnace hot flue gas and heating surface arranged in the other exhaust flue boiler. Incidental chain grate type, scale type, beams, and other means, the current domestic applications mainly for small and medium-sized joint type and scale type chain grate, generally large chain grate beam type. Former steam boiler steam boiler system to start all waterproof steam cylinder valve open, let go condensate. The inlet steam valve slightly open, to warm up the cylinder, drain cocks to be out after closing the steam, drain cocks. The steam valve was then opened progressively larger until drainage tank vent cock and water out there, and closed vent cock drain cocks. Turn on the water supply valve to the boiler feed water. Steam boiler in operation if there is gas in timely attention tank, water tank periodically open the air discharge valve, in order to avoid air resistance tank, the influent. Pump flow regulator bypass should be adjusted to achieve the degree of opening of the valve, and not with a method of adjusting the outlet valve is adjusted. At the rated discharge pressure of the pump, which inlet pressure should not exceed a predetermined value. Inlet and exhaust pressure difference should be maintained within a predetermined range. Steam boiler steam valve should be shut down first, then turn off the water valve and turn on the water valve is open, then turn on the water faucet open the lower part of the tank and cylinder, the cylinder water drain. Of steam cylinder reciprocating pump, which cylinder two stroke difference should not exceed 5% of rated travel.