2000 kg oil fire steam boiler price
Steam boiler pressure gauge should pay attention to matters 1, rated steam pressure less than 2.45MPa 2000 kg fire steam boiler price and pressure gauge accuracy not only in 2.5; rated pressure steam boiler child or equal to 2.45MPa, the pressure is too spread made not less than 1.5 level. Dial gauge diameter of not less than 100mm, in order to ensure the operation of the operator to see the surface of the pressure value shown. 2, should draw the red line on the dial gauge steam boiler, he pointed out that the maximum allowable working pressure. 3, the steam boiler pressure gauge should be provided at a convenient place to observe and purging, and to prevent the high temperature affected, freezing and vibration. 4, steam boiler pressure gauge should check at least every six months once the check should seal. 5, the pressure gauge connection tube steam boiler should leaks steam leakage phenomenon, otherwise it will reduce the pressure instruction value. 6, a steam boiler gauge scale element should be compatible with the measured working pressure, working pressure, typically 1.5; 3 times, preferably 2 times. When no steam boiler gauges, pressure gauges or pressure damage did not meet the requirements of the apparatus, boiler steam pressure gauges of the following circumstances, should stop using: 1, the surface glass breaking or blurred dial scale; 2, no seals , damage or seal verification period exceeded; 3, no pressure gauge pointer finite bit staple staple can not be restored to the limit at infinite set of bits from zero gauge pressure exceeds the pressure data bits garment allowable difference?; 4, the jump table or a pointer leak; 5, other effects gauge accurate defect. The use of the accumulator: the accumulator for a hydraulic accumulator system intermittent mechanical, hydraulic fluid may be stored in the actuator output when a batch or a low speed, and the actuator requires a large flow of fast-moving, as an auxiliary energy providing oil to the system together with the hydraulic pump, oil pump and thereby achieve miniaturization of the entire hydraulic system, to achieve the object of absorbing the impact energy sudden change fast opening and closing valve and the hydraulic load, the system generates a pressure shock, pet cause vibrations and noise, and even damage the machine. The accumulator can be alleviated, which absorb fluid shock absorber pressure pulsation absorbing accumulator, and reducing the pressure pulsation and flow pulsations of various pump, thereby reducing system noise and vibration. Having a damping effect of the gas spring accumulator, it can be used to absorb the mechanical vibrations between the body and the traveling wheel of the vehicle and the like. The accumulator can be balanced upright actuator (hydraulic cylinder) and gravity load decreases when the potential absorption into hydraulic energy store, while generating the rate-limiting resistance; upright when the actuator rises, releasing the original absorbing energy accumulator , together with the pump oil to the hydraulic cylinder, in order to achieve balance and energy.
wns series oil gas 2000 kg fire steam boiler price for pharmaceutical factory benefits
The boiler is equipped with movable front and rear smoke box covers to make the boiler easy to repair.
Our emphasis on increasing green, local governments also boiler operation produces nitrogen oxides and smoke emission requirements become more stringent. Fast boiler followed by the national trend of development, deepening of cleaning boiler product design and development. Lulu as a representative of business development of the national beverage, and hope to find a set of boiler energy conservation and clean in one, for drink production process of fermentation, sterilization, drying, curing and other processes. After many visits and market research, in October 2017 and entered into boiler fast boiler purchase contracts, purchase two 10 tons of steam and a whole 20 tons of steam condensing 2000 kg fire steam boiler price. The two sides this cooperation is the other quality fast condensing gas boiler highly recognized, has proved a powerful strength fast boiler in the boiler production and service of gas condensate from the side.
Gas boiler Burner Failures and gas boiler burners Failures and - best ￼ a gas boiler, gas boiler burner ignition misfire rod reasons: 1, the ignition bar gap interposed carbon residue with oil. 2, ignition rods fragmentation. moist. Leakage. 3, the distance between the ignition does not stick, too long or short. 4, ignition rods Insulation damage, short to ground. 5, ignition cable and transformer failure: cable, connector damage caused by a short circuit during ignition; transformer break or other fault occurs. Measures following five: Clear, renewal, adjust the distance, change and switching transformer. Second, gas boiler, but spark ignition rods misfire reasons: 1, the cyclone disc space ventilation is blocked carbon, poor ventilation. 2, dirty oil nozzle clogging or wear. 3, the throttle angle is set too small. 4, the firing bar from the leading edge from the oil nozzle tip inappropriate (too protruding or retracted) 5, the first solenoid valve is an oil debris blocking gun (gun small kerosene). 6, oily or too viscous to flow easily clogged or the oil filtration system the valve is not opened, so that insufficient suction pump, oil pressure. 7, the filter pump itself blocked. 8, the oil more water (boiling abnormal noise within the heater). Measures are: Clear; first wash, such as not renewed; turndown test; adjusting the distance (in 3 ~ 4mm as well); Remove cleaning (cleaning the parts diesel); Check tubing and oil filters, insulation equipment ; remove peripheral screw pump, carefully remove the cover inside out oil network, with immersion oil; renewal of the test oil. Third, when the gas boiler and turn the fire a small fire normal, off, or flashing instability reasons: 1, the air volume damper setting fire too. 2, oil fires micro switch valve (damper outermost that group) inappropriate setting (set throttle air flow rate is greater than the fire). 3, oleaginous easy to spray viscosity is too high (heavy). 4, and the nozzle plate spacing cyclone inappropriate. 5, fire nozzle worn or dirty. 6, the preliminary fuel tank temperature is too high, so that the steam not smooth oil pump oil feed. 7, fuel oil boiler water. Action: Test gradually reduced; heating temperature; adjusting the distance (between 0 ~ 10mm); clean or replace; approximately set to about 50 deg.] C; or drain oil change. Fourth, the noise increases gas boiler burner reasons: 1, cut-off valve is closed or the passage into the fuel shortage, an oil filter blockage. 2, the oil inlet temperature is low, the oil viscosity is too high or the temperature is too high the pump inlet. 3, oil pump failure. 4, fan motor bearing damage. 5, dirty fan impeller. Processing methods: ① the oil line check valve is open, if the oil filter is working properly, the filter cleaning pump itself. ② heating oil or reduce the oil temperature. ③ Replace the oil pump. ④ replace motor or bearings. ⑤ cleaning fan wheel.