1 ton lng steam generator steam boiler
Hot water boiler vaporization problem the whole solution 1, hot water boiler 1 ton lng steam generator steam boiler of the phenomenon (1) boiler and pressure suddenly increased safety valve starts to emerge from the water and steam in the expansion tank. (2) the impact of sound water boiler, pipes to vibrate. Impact or the like occurs in the water (3) circulatory system piping. (4) a sharp rise in the temperature of boiler water, over-temperature signal overtemperature alarm occurs. 2, because (1) hot water boiler pot all the water vaporization operator negligence or misuse. Such as forced circulation hot water systems, at startup, the first boiler ignition, after the circulation pump. When shutdown, stop circulation pump, after stopping the boiler operation; or storage of fuel and heat in the boiler does not distribute all do, eager to stop the circulation pump is running and so grossly erroneous operation. (2) the occurrence of circulating hot water boiler outage, improper handling. (3) hot water boiler circulation system or severe leakage, device malfunction or constant pressure, causing a sudden drop in pressure in the boiler. This situation occurs mainly in the high-temperature hot water boilers. (4) cyclic interrupt occurs, although the boiler immediately stop running, but the remaining fuel in the combustion chamber and heat storage water vapor of the pan. This usually heat storage capacity in the furnace, the occurrence of a small pot of water volume of hot water boiler. (5) stop the pump sudden power failure or failure of the circulation pump. (6) the temperature of the hot water boiler, the pressure indicating instrument malfunction, resulting in erroneous judgment. 3, the reason the hot water boiler local vaporized boiler water (1) within the reservoir portion of the tube boiler scale or debris, the local destruction of the boiler water cycle. (2) a boiler structure unreasonable or undesirable combustion conditions, resulting in the line between the parallel deviation is too large heat boiler or boiler water uneven flow distribution, resulting in local overheating vaporized. Local and overall circulation circuit (3) can not form a natural circulation boiler, causing local overheating of vaporized water circulation circuit occurs once the pump stops and the like. 4, treatment of hot water boiler steam boiler (1) stops running hot water boiler. (2) Check the hot water boiler and heating cycle causes vaporization system, and processed. (3) hot water boiler and hot water heating system natural circulation loop, loop back to the natural valve open road. (4) When a sudden power failure, the pump stops running, stopping in the boiler water cycle (forced circulation boiler), the temperature of the boiler water continues to rise due to heat accumulation surface of the combustion chamber of the boiler water to steam, because of a large water capacity If handled properly, usually does not cause accidents pot of water vapor. For hot water boiler tube DC (most of this is domestically produced boilers), because of its small water capacity, when a sudden power failure stop the pump, resulting in more accidents pot of water vapor. Hot water boiler should have suddenly prevent or mitigate the pot of water vapor measures to stop the pump during a power outage. China is now using more is to add water to the boiler and the boiler outlet slow release of steam, the pot of water on the one hand to maintain liquidity, on the other hand reduce the water temperature, up until the elimination of the combustion chamber of the regenerator. Some install the spare circulation pump driven by the internal combustion engine, when a sudden power failure, start the engine, but poor when asked to take into account, because the engine is not instantaneous will be able to start. There is provided a self-standby power supply or generator.
Relationship between generator capacity and boiler capacity
From the energy point of view, the power generation process of the power plant is essentially a process of energy conversion (chemical energy → thermal energy → kinetic energy → electrical energy).
Fangkuai Group adopts the concept of “moulding character and creating high-quality products”, and continues to research and continuously improve the technological content of products to get closer to users. With the mission of “creating convenient and fast boiler high-quality products for users”, it uses remote monitoring, APP, and active return visits. And other channels to provide users with convenient and efficient services; with the core values of "professionalism, lean work" as the core value, established an effective enterprise management system, adopted ISO9001 quality management system, OHSA18001 occupational health and safety management system and ISO14001 environmental management System certification; and cultivated a large number of high-quality employees with norms of behavior, professionalism, and continuous commitment to provide customers with more convenient and efficient services.
Secondly, if your boiler is electric 1 ton lng steam generator steam boilers, the installation should pay attention to the ground as it relates to the use of safety later. In order to secure the ground wire installation, a ground line nearby and piling a depth greater than or equal to 1 m 5, the cable connector ground should be sintered at a ground pile head. Moisture to prevent rust should be higher than the ground connecting linker 100mm is appropriate. Boiler exhaust chimney to be discharged toward the outside should be, and should be higher than at the outlet of the boiler Di from 1.5 to 2 m. Ask your local branch overhaul of special equipment installed after the declaration. Acceptance by the relevant part of the consent to the use, and receive a use permit before using the boiler. 30L or less than the vapor pressure of the steam generator volume is less than 0.1MPa fall within the scope of the national exemption, ie no need for boiler use permits can be used.