Capacity of 1200000 KCal Gas Fired Boiler
If natural gas as capacity of 1200000 kcal fired boiler fuel choice, because the convenience of clean natural gas and fuel used in the boiler service life will be over 10 years; but if it is a boiler coal or other fuels, it will shorten the life of some. Further, the life of the boiler with the use of the frequency, the higher the frequency the shorter the life of the boiler, the greater the contrary. Late boiler maintenance is also very important for the life of the boiler, good maintenance will extend the life of the boiler.
After the capacity of 1200000 kcal fired boiler put into use, such as the hotel responsible person to give us feedback: fast boiler advanced product design, simple and intuitive operation, the most critical is energy saving, low NOx emissions, can be used in the Beijing area. Compared with other boiler brands, fast Boiler made us worry. --customer feedback
Gas capacity of 1200000 kcal fired boiler safe handling as the country increasingly stringent emission standards for air pollution, the country has already started work boilers from coal to gas, out of heavily polluting coal-fired boilers, gas boilers using clean fuels. In this regard, Kono Tips boiler, gas boiler process, the need to pay attention to some safety issues: 1. burner to keep the working environment clean and dry, burner cleaning and maintenance once per shift to the control circuit must not get wet, affected by high temperature. 2. Check the electrical installations, mainly: whether the damaged wire, jacket damage, without loosening the screws, the contact is good, the motor is running any abnormal sound. 3. During normal operation, the burner portion close to thermodynamic device (such as a flange connection part) will be very hot, to avoid burns. Do not place near flammable materials, so as not to cause a fire. 4. combustor during startup, if the burner is locked repeated alarm reasons should be identified, and then identify failures and excluded press the reset button (pressing the reset button must not exceed 10 seconds), continue to start. 5. After the total gas pipeline experienced a temporary power failure solenoid valve (steel tile shed) to stop gas supply will automatically shut down until the first call burner electric alarm device to send, then a small hammer solenoid valve with total on hand to pull, you must first send electricity to manually open solenoid valve, solenoid valve will be closed and vice versa total. 6. fireman not mess-tune the burner, abnormal promptly notify management personnel, approved by management and then make adjustments. 7. In the long-term shutdown state, to do maintenance work on the boiler equipment, for each transmission parts to clean, lubricate.
Gas-fired steam capacity of 1200000 kcal fired boiler abnormal situation, how should we deal with it? When we use gas steam boiler, failure or abnormal phenomena it is inevitable, but in order not to affect the normal use, in the event of a problem gas steam boiler to be timely processing solutions, then the face of all kinds of circumstances, we should how to handle it? Share some of the ways we deal with unusual circumstances. If only gas steam boiler circulating pump abnormalities, such as its current decreases, the pump outlet pressure back to zero, which indicates no oil pump is idle, it may be caused by oil vaporization. Yang identify the reasons therefore first vaporized measures; such as clogging of the filter circulating pump bypass opening evacuated immediately clean the filter; heat transfer fluid as a result of added aqueous or decomposed gases are not excluded in the system, should immediately open the vent an exhaust valve. Circulation pump pressure constant, the current increases and the flow drops, deterioration of the thermally conductive fluid, the viscosity increased, should be replaced or regenerated. New heat transfer fluid as a result of decomposition of aqueous or excluded gases in the system, should immediately open the vent valve of the exhaust gas. When the current is lower than normal circulation pump, the circulation pump efficiency is decreased, the flow rate decline may be heating pipes plug fouling, stainless steel chain should be cleaned. If the gas steam boiler before and after the filter increased in pressure, the pump inlet pressure drops, the filter may be stuck, the opening of the bypass, disassemble and clean the filter. In addition to its low furnace outlet temperature liquid phase heat carrier, mainly for lack of heat fouling problems, it is timely soot blowing. Gas steam boiler grate more common problem is stuck, there are reasons including breaking grate or the grate off loose pins; coal grate has stuck to metallic inclusions; arched grate; slag is sinking the tip of the grate stuck. In response to this phenomenon, the required reverse hand grate plate debris removal, replacement breaking grate after the start, then jammed as startup, stop the rotation of the reasons detailed inspection to resolve. But also to re-adjust the adjustment screw on both sides of the grate tension, if still does not work, we need to replace the sprocket.