1 ton mobile gas steam boilers prices
Gas 1 ton mobile steam boilers prices loading, installation considerations gas steam boiler is a very wide range of special equipment, usually built in the boiler room. However, its load, the installation process, some issues must be taken, otherwise it may cause a certain degree of economic losses. 1, the process of handling and transporting gas in a steam boiler to be noted the following: the lifting capacity of the lifting device should be matched to the weight of the boiler Lifting. Can not be used for lifting has a length marked with a lifting lug can not be used should be chosen on the boiler rope, rope length to avoid inappropriate, leading to scratching furnace. In the loading, unloading and handling process must ensure that the boiler without any damage. 2, installation of boiler maintenance reserve space, make sure there is enough space for maintenance around the boiler. 3, the base gas steam boiler, the base of the boiler and precautions to be installed on the basis of 100-150mm above the floor of the boiler on the premises, subject to prior confirmation boiler manufacturing company with technical personnel, in accordance with the basis for construction drawings. Must stay out of anchor bolts embedded hole basis. Foundation must be able to withstand the weight of the boiler and the largest holding water amount. When the mounting base, must first be positioned. After the alignment adjustment in the end the length of two diagonal lines of the same base, then the entire tightening the fixing bolt. Base mounting reference line marked for reference. 4. General Precautions Be careful not to tilt too boilers and accessories and be impact. Can not be placed outside the boiler fuel. Do not dirty oil and water boilers should generally be installed in a separate boiler room, the new gas steam boiler room should not be connected to the house. A boiler can not be connected, (B) and (C) use of flammable liquid fire risk room. If the production plant is connected to the other, separated by a firewall application. 5, fire resistance rating of the boiler room of the building and fire safety requirements should be consistent with "architectural design code for fire protection" and "design of tall buildings for fire protection" requirements. Gas-fired steam boiler room on the ground should be smooth, non-flammable, no water, load-bearing foundation should meet the requirements. Gas-fired steam boiler supply voltage should be stable, to avoid burn electrical components. The voltage instability, is recommended to install regulators. To set the boiler room ventilation equipment, to maintain the boiler temperature at 50 ° or less.
For more than two decades, it has been the focus on clean boilers, the insistence on precision and wisdom, and the pursuit of exquisite craftsmanship that have made today's Fangkuai boilers. Fangkui Boiler will always be based on the boiler industry, and will return customer support and trust with brilliant results and sophisticated technology.
ZG also manufactures high efficiency, multi fuel Industrial water tube Boilers & Steam Boiler based on technology acquired, with whom we had over 60 Years of technical collaboration. It can supply boilers upto 270 TPH capacity, steam at pressure upto 5.28Mpa. and temperatures up to 330. ZG has a large proven reference list of more than 1000 installations completed worldwide in last 6 decades. Water tube boiler fuel can be solid fuel, gas and oil fuel.The water-tube boilers described above are usually of a large capacity.
Performance horizontal oil-fired boiler is now full of water and the handling of horizontal 1 ton mobile steam boilers prices steam boiler accident refers to a horizontal design, in accordance with the fuel divided into horizontal electric steam boilers, horizontal steam boiler fuel, gas steam boiler and lying horizontal coal-fired steam boilers. Horizontal steam boiler flue gas flow due to the long, slow smoke, high thermal efficiency, it is very energy efficient. Horizontal steam boiler filled with water treatment and now the performance of an accident, the phenomenon of (1) the water level is higher than the maximum permitted cable, or can not see the water level, water table within a glass tube (board) Color dark boiler full of water. (2) all of the water phase as a color level gauge indication color. High-water alarm signal (3) water level alarm occurs. (4) decreased superheated steam temperature. (5) water flow is not normally greater than the steam flow. (6) water in a large number of sub-cylinder, severe trap operation. (7) with a large amount of water steam severe, increased salinity, water hammer occurs in the sound of the steam pipe, the steam connection flange outwardly dripping take place. 2, boiler full of water treatment rinse water table, determined to be minor or serious full of water full of water. Method: Close water table, the water pipe connected cock, then open drain cocks As can be seen from the decreased water level, indicating a slight full of water, the water supply is stopped, the drain valve open, put to the normal water level. Such as severe filled with water due to take emergency shutdown measures.