3 set hot water boiler in pharmaceutical factory
Gas 3 set hot water boiler in pharmaceutical factory pump installation step 1, while checking the four sides of the center point of the base of the pump shown and vertical and horizontal lines on the basis of the pump installation. 2, the hoisting ropes when lifting bail based on the pump and motor to adjust the position of the base, so that the center point coincides with the center line on the base on the base. 3, the horizontal adjustment, the horizontal foot on the working surface of the pump chassis, adjust the level of the pump, the level of which shall not exceed 0.1mm / m. 4, a three-valve pump, i.e. the pump inlet valve and a check valve should be fitted, with an outlet valve. 5, gas hot water boiler pump inlet and outlet pipe connections are mostly flexible, inlet and outlet installation of soft joints. 6, water pump export pipeline smaller than 1, provided with adjustable shorting should export. 7, the horizontal section of the suction pipe connected to the pump, there should be 0.01-0.02 slope, and in the highest parts of the boiler pump suction pipe.
AMD Power were to buy 10 tons of steam and one 4 tons of steam condensing steam boiler fuel gas from the company for cell processing company production and construction. From the analysis of the demand to the boiler factory, by the company solely responsible for AMD Power fully demonstrated the company's confidence in me, the smooth progress of bilateral cooperation.
3 ton gas fired steam boiler can supply steam during the process of biscuits production. WNS 3 ton gas fired steam boiler is a typical three-pass, wet-back horizontal firetube boiler. The first pass in this gas fired steam boiler flows through the furnace from front to back. The furnace of this steam boiler is corrugated to maximize efficiency while also minimizing thermal stress. Flue in the gas fired steam boiler gasses then travel from the combustion furnace to the front chamber forming the second pass. For the third pass in this 3 ton gas fired steam boiler gases flow through tubes to the back of the boiler stack and out the exhaust vent, located conveniently in the back of the boiler. The second and third passes travel through heavy-duty seamless tubes in this 3 ton gas fired steam boilers for biscuit company.
Condensing boiler forced-premix burners, the combustion head surface metal fiber braid is formed only one layer of light blue flame burner head in the cylinder wall, and since the high temperature of the barrel wall, will form a high temperature radiation, compared with atmospheric burners stainless steel, metal fiber burner both radiation heat transfer, but also convection heat transfer, better heat transfer.