10 bar gas steam boiler
Hot water boiler heating industry is our essential equipment, gas hot water boiler water provided by the party fast flotilla, high thermal efficiency direct savings on fuel costs of inputs for our company, the intelligence facilities let the boiler run more convenient and effective to reduce the labor intensity of fireman people. --customer feedback
Why hot water boiler heating more energy efficient, more environmentally friendly: generally used for heating hot water boilers, but the need to use less steam production process. Biomass boiler categories: biomass boilers Horizontal, vertical biomass boilers. Biomass gas thermal oil heaters, biomass 10 bar steam boiler, biomass hot water boiler, biomass oil furnace. Steam boiler is an energy conversion device, the energy input to the boiler fuel chemical energy, electrical energy, thermal energy and other forms of high temperature flue gas, and after converting the boiler, the steam output having a certain outside thermal energy, high-temperature hot water or an organic carrier. Because it is more energy efficient than steam boiler, more environmentally friendly. First of all, in terms of fuel consumption, hot water heating than the steam boiler heating savings of 20% to 40% of fuel, this amount is very impressive. Summed up for two reasons: First, it does not condensate and heat loss due to evaporation of the secondary, two hot water heating pipe is heated by the use of special materials, as thin as possible to meet pipeline needs, heat loss is small. Heat loss due to the steam heating pipe caused by steam leakage large.
Boiler multiple protection: (1) the integration of boiler water level to protect water level and boiler design, the appearance of more compact appearance, accurately show the actual water level in the boiler body function. Coupled with dual independent electronic water level control system to achieve ultra-low water level in the boiler, low water level automatic adjustment function, the normal water level, high water level, ensure that the boiler in a variety of unforeseen circumstances foolproof, secure home. (2) steam pressure protection ☆ pressure controller: selection of high sensitivity of the pressure controller, the pressure is high, or low levels of signal to the electrical switch, other control lines or automatic control chain protection. Common pressure controller and pressure gauge, vapor pressure overpressure alarm can cut off the burner limit is reached; the pressure controller may be single or double fire burning fire the actual operating pressure regulator. ☆ safety valve: safety valve is the last line of defense to protect the boiler, the boiler pressure exceeds the limit, according to the set pressure relief valve design with the school, the exhaust steam pressure relief, to ensure the normal operation of the boiler. (3) having a burner flame protection flame protection inlet means, combustion function is to detect, when the ignition failure or extinguish combustion middle, immediately off the burner into the oil (gas) solenoid valve, the blower continues to operate at this time, the furnace was purged combustible residual gas, after 20 to 30 seconds purge, and various auxiliary blowers automatically cut off power, the boiler operation stops. (4) self-locking power failure protection case, the boiler shutdown immediately burst self-locking power interruption, if the current power is restored, the boiler will not start at any time, you must reset release self-locking, to re-start the ignition.
After the gas hot water boiler hot water boiler vaporization emergency 1. Vaporization handler circulating pump stops abnormally pump failure caused by: ① blower stops running immediately. ② immediately open the door, take measures to pressure the fire, lift the chute gate, cutting off the supply of coal grate. ③ In the case of boiler pressure not greater than 0.6MPa (600KPa), the exhaust valve to follow, only a sharp rise in pressure in the boiler deflated, used only relief exceeds 0.9MPa, and the exhaust process to be carried out slowly, prevention boiler due to loss of pressure and more violently again vaporized. ④ close the boiler water, water main gas valve. ⑤ open stop valve recirculation line, to ensure that the water supply pipe velocity convection heating surface (economizer) to prevent re-vaporization of the economizer. ⑥ The operation of the above operation, at the same time to pay the boiler to reduce the boiler water temperature and the furnace pressure. ⑦ After the boiler pressure is normal, i.e., opening the standby circulating pump, into the normal combustion. 2. Treatment failure or sudden loss of power boiler vaporization of power: ① immediately open the door, lift the coal chute slide gate to take pressure fire measures to reduce the oven temperature. ② Grate with the fastest speed in order in the shortest time to fire onto the slag tap. ③ the degree of treatment in the first case. Once a short time can not supply heating network system, antifreeze should take emergency measures. 3. Due to excessive heat boiler boiler vaporization process: ① the immediate closure of the drum, induced draft fan. ② immediately open the door, take measures to pressure the fire, lift the supply of coal chute slide gate, off of coal, while the grate into fast gear. ③ In the case confirmed the presence of water, the boiler can supply water to the boiler body, boiler out of the water while closing the main valve. ④ Open line stop valve recirculation pump to ensure water velocity convection heating surface of the pipe, to prevent the economizer again vaporized. ⑤ Open circulating pump with jog mode, jog each time less than 30 seconds, again less than one minute jog interval. Jog purpose is to reduce the boiler water temperature, while preventing a large amount of steam into the pipeline system. ⑥ back into place after the safety valve, circulating pump running, and then the normal burning stove. 4. Water boiler system run vaporization process due to water loss, loss of pressure caused by: ① immediately closed drum, induced draft fan. ② out of the water while closing the main valve and the boiler circulating pump. ③ take the same measures to cool the furnace tube described above. ④ Open stop valve recirculation line. ⑤ rely exhaust valve until the safety valve back into place. ⑥ until the boiler water temperature drops below 50 ℃, when the temperature of the furnace temperature less number 200 ℃, again within the boiler feed water, water course to be carried out slowly, to prevent harm to the boiler when the temperature is too large. ⑦ After processing leakage fault, the system time to the replenishment, and out of the water boiler always open the valve, and the circulating pump, and then normal combustion.