6 ton natural gas steam boiler
"Fangkuai" boiler relies on its own products and technical advantages in industrial boilers and automatic control, and uses advanced Internet of Things technology, mobile internet technology, cloud computing technology, big data technology and intelligent control technology with heat sources, heat networks, and thermal users. It is highly centralized to form an intelligent cloud management and control center, which truly realizes the intelligentization of industrial boilers. "Fangkuai" remote monitoring system for boilers has improved boiler operation efficiency; "Fangkuai" boiler cloud service platform allows boilers to learn to think; "Fangkuai" boiler big data allows boiler cloud service platform to have "super brain"; " The real-time monitoring of the “Fangkuai” boiler makes the boiler problem nowhere to hide; the “Fangkuai” boiler 400 service system makes the service more convenient and faster.
Such as the use of coal fired boilers, coal heating value 5500Kcal / Kg (in terms of standard coal) around, (coal prices have continued their upward trend in the market price of 460 yuan per ton, and the purchase and sale channel is not smooth, to control the current energy under rotten mining waste and serious situation, the price of coal have continued upward momentum). 10t 6 ton steam boiler steam coal consumption per ton of 0.2 ton, the price of 92 yuan. The hot gas is 8000kcal / Nm3, the price of natural gas per cubic 2.0 million, according to gas consumption per ton of steam gas consumption 80Nm3, the price of 160 dollars.
Matters needing attention in loading and installation of Gas-fired Steam Boiler
Gas-fired steam boilers are a very wide range of special equipment, usually built in boiler rooms. However, in the process of loading and installation, some problems must be paid attention to, otherwise it may cause a certain degree of economic loss.
1. Pay attention to the following matters during the loading and unloading and handling of gas-fired boilers: the lifting capacity of the lifting equipment should match the weight of the lifting boiler. The lifting lug on the boiler with the lifting lugs that cannot be used for lifting can not be used for lifting. The length of the steel cord should be reasonably selected to avoid the scratching of the furnace due to the improper length of the steel cord. The boiler must be protected from any damage during handling and handling.
2. Reserves for maintenance space When installing boilers, ensure that there is sufficient maintenance space around the boiler.
3. Setting and precautions for the base and base of the gas steam boiler The boiler body must be installed on the basis of 100-150mm above the floor of the boiler room. It must be confirmed with the technical personnel of the boiler manufacturing company in advance and constructed according to the basic drawings. The anchor bolts must be reserved on the foundation. The foundation shall be capable of withstanding the maximum weight of the boiler and the amount of water it holds. When installing the base, you must first position it. After positioning, adjust to the same length of the two diagonals of the base, and then tighten all the fixing bolts. The installation of the base is carried out with reference to the reference line.
4, general precautions Be careful not to tilt and impact the boiler and accessories too much. No combustibles can be placed around the boiler. Do not use oil and water to smother the boiler. The boiler should normally be installed in a separate boiler room. The new gas-fired boiler room should not be connected to the house. The boiler room shall not be connected to Class A, Class B and Category C fire hazard rooms using flammable liquids. If connected to other production plants, the application firewall is separated.
The reason the gas boiler burner increased noise analysis when making use of the gas boiler and found this small fire normal, but this time turn the fire, extinguished or flashing instability. First speaking, that is because of this fire damper of the air volume setting is too large; i.e. after an oil fire because the micro-switch valve (damper outermost that group) inappropriate setting (set lower than the fire damper of the air flow larger) burner gas noise increases, mostly because the oil shut-off valve which is closed or lack of oil into the oil filter clogging; or, this is because of low temperature into the oil, the viscosity is too high or the pump into the oil temperature is too high; oil pump failure; fan motor bearing damage; there is because the fan impeller dirty equipment resulting in large noise. The above-described failure when using gas boiler, but also because the viscosity is too high oleaginous easy to be atomized (heavy oil); cyclones and because improper disc and the nozzle pitch; Note that because the fire is worn or dirty nipple; also because this preparatory tank the heating temperature is too high, causing the oil pump oil feed steam does not conform; or because the fuel inside the boiler resulting aqueous oil. When the above-described fault gas boiler used to perform this process, the test should be done gradually decreases; after heating temperature should be; adjusting the distance (between 0 ~ 10mm); clean or replace; is set to about 50 deg.] C to about; or drain oil change.