China Manufacturer 1-20 ton Per Hour Industrial Gas Fired Steam Boiler Supplier
（9）Combustion Adjustment method of Oil-fired Gas-fired Boiler
The combustion adjustment of oil-fired gas-fired boiler is successful and the load adjustment can be carried out after turning into normal operation. At this time, the combustion situation in the furnace should be observed frequently. If the atomization of oil and gas is not good, the flame jumps, the flame hits the furnace tank, and the exhaust temperature is too high or too low, the oil pressure, oil temperature, steam volume, air pressure and steam pressure should be adjusted in time to ensure the safe and economical operation of the boiler. The oil pressure and the pressure are related to the boiler load. The adjustment of the oil pressure is realized by adjusting the pressure of the burner or the amount of oil returned. The adjustment of air pressure is achieved through the opening of the valve. When adjusting a load, enter At the same time, the air volume adjustment must be carried out synchronously to ensure the reasonable match between the oil quantity and the air volume, so as to achieve the purpose of economical operation of the boiler.
Diqing in Yunnan Nonferrous Metals Co., Ltd. mainly engaged in Pulang copper mining, site selection, sales and other items. As we all know, in the copper smelting process, it consumes a lot of electricity and thermal power resources, which account for most of the hot water consumption. Combined with the actual demand Diqing company, to provide fast Boiler 1 stage electric heating hot water boiler of 2.1MW.
Steam boilers and thermal oil heaters which is better? Which is more energy-efficient? Steam boilers and thermal oil heaters, which is more fuel cost savings? At the same power (represented with evaporation) for comparing the boiler, HTF medium because of the high temperature, so that the temperature of the steam exhaust gas temperature than the exhaust gas with a higher heating power of the boiler, the exhaust gas temperature directly affects Thermal efficiency. That same power (represented with evaporation) conditions, the efficiency is not high efficiency oil boiler china manufacturer 1-20 ton per hour industrial fired steam boiler supplier. In fact, now you finally choose what kind of boiler is required to rely on the temperature of your decision. If you ask a medium temperature to 300 degrees, you can only choose oil furnace; if you think there is a live medium temperature of 180 degrees is enough to use, it is recommended that you choose a steam boiler, because it is more energy-efficient with conditions). These are the kind of steam boilers and thermal oil heaters and today we analyze all the information of more energy-efficient, and the above information indicates that the steam boiler more energy saving, more fuel-efficient.
The reason the gas boiler burner noise analysis increases in the use of gas-fired boiler, found a small fire is normal, but when it becomes a fire goes out or flashing instability. First, because of excessive wind fire damper is provided; secondly, because of the fire valve microswitch (outermost damper group) is set incorrectly (fire damper is set larger than the amount of wind). Fuel circuit closing valve or port into the oil shortage, an oil filter plugging, increased gas burner boiler noise; Alternatively, since the oil inlet temperature is low, the viscosity is too high, the oil feed pump temperature, pump failure, fan motor bearing damage, and because the fan impeller dirty equipment, resulting in noisy equipment. Gas boiler in the course of the above failures, the viscosity is too high to spray the oil (heavy oil), and improper nozzle plate from the cyclone, and the like due to worn or dirty nozzles plus reasons. May be due to too high a heating temperature of the tank, leading to the steam delivery oil pump is not smooth; or because the fuel oil boiler caused by the water content. In use the gas boiler, the above failures should be gradually reduced, the heating temperature, to adjust the distance (0 ~ 10mm), cleaning or replacement should be about 50 ℃, the heating temperature should be raised. Oil change or drainage.