5tons coal fired chain grate steam boiler n chemical engineering
Steam boiler wear and electric test pump DSY Henan fast boiler's 5tons coal fired chain grate steam boiler n chemical engineering small series with you about wear and DSY electric test pump wear is one common steam boiler heating surface defects, boiler heating surface is arranged in the boiler the furnace and the flue, in particular a heating surface in the steam boiler flue vertical tail, by the long brush smoke, soot in the flue gas so that the wall heating surface wear thinned, so that heat from the flue gas scouring wall ironed a phenomenon known as wear and tear. Flow rate, the concentration of soot in the flue gas and the hardness of the tube bundle arrangement such factors as the wear rate of the heating surface of the steam boiler and the flue gas is related to the flow rate of flue gas wherein the greatest impact on the wear of the heating surface. Experimentally measured, proportional to the cube of the wear rate of the heating surface tubes and the flue gas velocity, it is necessary to effectively control the flow rate of flue gas. Leakage of the furnace wall, a partial wall flue ash, convection heating surface partially severe slagging will cause a partial flue gas velocity is too large, so that the heating surface tubes local wear increased, further, when the soot blowers work failure, high pressure steam steam heating surface tube will blow erosion, so that the wall thinning. Heating surface tubes often wear area is: cool ash, burner, bullnose, and close to Manhole sootblowing waterwall tube aperture; a lower portion of the flue gas before the steering tube heating surface vertical chamber; vertical tail horizontal heating surface portion of the second row of three tubes of the flue, the lower portion of the second three tubes, tube support edge portion of the clip, close to the furnace wall side of the rows of tubes and the individual tubes and the like projecting tube rows. Heating surface wear reduction methods are: to reduce boiler load, reducing flue gas velocity; burning coal quality, reducing the content of fly ash in the boiler flue gas steam; change bundle arrangement, a staggered arrangement to the line arrangement; Clear slagging and blocking flue ash, flue gas flow area increases; leakage reduction furnace wall; the installation of a shoe or the spoiler like. Abrasion test on the electric pump plunger hole set DSY electric test checking pump plunger sleeve (1) Check the DSY type. If the pump DSY electric test has passed the test on sealing ST-990 or the tester 3,375,375, the plunger sleeve is available. If the leakage is large, it is necessary to replace the plunger and plunger sleeve. (2) using the burr, coke, and high-expansion magnifying glass to check the amount of deformation of the bore. When the metering orifice is damaged, DSY i.e. electric test pump is not working properly. Do not attempt to clean with a wire, plug, etc., should be cleaned with a solvent. (3) Check the fuel oil channel as well as choking loose plunger sleeve for cracks. (4) Check DSY electric test pump plunger sleeve surface endless belt black area and Degree how damage flatness. Some electric test pump head end of the barrel nozzle sump has been canceled. Henan is committed to fast boiler steam boiler manufacturing, product quality, reasonable prices and widespread industry praise, if you have any needs, please contact us!
Fuel type: natural gas, biogas, lpg, oil, city coal gas, light oil, heavy oil, disel oil
Rubber can be seen everywhere in life. There are more and more rubber products in the industrial sector. There are many varieties and wide applications. The main products are tapes, hoses, gaskets, rubber rollers, rubber sheets and rubber linings. Labor protection products. For rubber plants, boilers are a very important configuration. Rubber companies use steam generated by steam boilers. The rubber article can be vulcanized by a vulcanization apparatus to change the rubber article into an elastomer. Customers should choose the right boiler according to their own needs.
Hot water boiler in the school dormitory and classroom building are generally used for central heating, drinking water and bathing water aspects of teachers and students and so on. Shanxi Linxian County high school is an important educational school personnel training for the community. 2017, the school responded positively to national coal to gas and other environmental policies, but also to provide students with a more favorable living and learning environment, the school decided to phase out conventional coal-fired boilers, clean and environmentally friendly replacement for the gas boiler. After getting to know and choose the boiler industry, major companies, determined cooperation with professional production of clean fuel boiler fast boiler-by-side to provide a fast 4.2MW integrated condensing gas hot water boiler (WNS4.2-1.0 / 115 / 70-YQ).
6 tons gas 5tons coal fired chain grate steam boiler n chemical engineering steam pressure adjusting a boiler operation, must frequently monitor the pressure gauge indicated. To maintain stable steam pressure, boiler pressure must not exceed the design pressure. Second, increasing boiler load: Steam pressure decreased boiler load is increased, if the level is high at this time, the amount of water should be reduced to a water supply or suspend, the amount of coal and increase the air volume. Gradually increase the amount of water at the same time to strengthen the burning, keep the steam pressure and the water level is normal. Third, the boiler load reduction: the vapor pressure rises to reduce boiler load, if the level is high at this time, the amount of coal should be reduced and the air volume, reduced combustion. Then the appropriate water reduction or suspension of water supply to the water vapor pressure and stability in the nominal range. Then press the normal combustion and the amount of feed water 8 to adjust. If the actual water level within the boiler is low, to increase the amount of water should, until the water level returns to normal after the combustion and needs to be adjusted according to the water vapor pressure and load changes.