Energy Saving Quick Assembly Rice Husk fired Steam Boiler
Pay attention to gas energy saving quick assembly rice husk fired steam boiler which runs: customer after purchasing gas steam boiler, not sit back and relax, but also need to seriously understand the operation of the boiler starts, the attention to what matters, so you can be more effective in ensuring the long life of the boiler. 1, the cold gas steam boiler working pressure from the ignition rises, boost heating time is about 3 to 4 hours. When the boiler pressure rose to 0.05 ~ 0.1MPa, should wash boiler pressure gauge and water level gauge; when the boiler pressure rose to 0.15 ~ 0.2MPa, the boiler should be shut down air valve and check valve for leaks, measures should be taken if a leak be eliminated; when the boiler pressure rose to 0.2 ~ 0.25MPa, boiler blowdown to conduct a test, when sewage boiler water level should be above the normal water level, and check the drain valve leaks, if the leak should take measures to eliminate; when the boiler when the pressure is raised 0.3MPa, a full review of the fastening member boiler pressure element, such as manholes, hand bolt holes, and check holes of each flange connection is loose, and a tighten heat. 2, the pump checks whether the automatic operation to maintain the normal water level, water level in the "line from the pump" the normal start, the water level in the "stop pump line" pump can be stopped; 3, control pressure is normal, when the steam pressure reaches when the set value, the combustion is stopped, lights overpressure, the pressure is reduced to the set value, the boiler can start automatically; 4, when the load pressure reaches the set value, the fire load due to a small fire, when the pressure drops to set when the predetermined value, the transfer of small fires burning fire; 5, when the pressure can not be set at normal pressure shutdown, the shutdown will alarm the second overpressure shall be restarted; 6, the exhaust gas temperature should not exceed 300 ℃, otherwise, the shutdown should check; 7, when gas steam boiler into normal operation phase, boiler fireman personnel to strengthen the boiler, instrumentation and safety accessories and auxiliary equipment is a monitor, a good job is a boiler and auxiliary equipment inspection tour and in a timely manner fill run record.
Diameter (1) of the dip pipe and pressure should be based on the rated capacity of the boiler is determined, and an inner diameter not less than 25 mm;
In July 2013, a Purchase Department Manager from Philippines visited our factory in China. He wanted to know more about our biomass fired energy saving quick assembly rice husk fired steam boiler manufacturing sites. Accompanied with our advanced engineers, they visited our boiler manufacturing sites. Our engineers introduced the features and high technology of this Bagasse Biomass Fired Steam Boiler whose designs also won national patents in China. Our consumer from Philippines were really satisfied and finally we two parts signed a sales contract about purchasing a set of 4 ton/h Bagassse Biomass Fired Steam Boiler For Sugar Factory.
The recent good news story: Union Square soon Group was named the provincial Federation of factory affairs leading group as "micro-small and medium private enterprises in Henan workers' congress building demonstration units" honorary title. Win the title, is inseparable from the efforts of all labor union workers, they work with their own solid foundation, effective operational mechanism and splendid achievements successfully nominated and award winning. Over the years, the Labor Union under the correct guidance of urban levels of trade unions, under the correct leadership of the Party, Comrade rely on the staff, smooth internal management channels, good to play the democratic management of conflicts "relief valve" business "stabilizer" and developing the "catalyst".